# Winding Factor | Pitch Factor | Distribution Factor

**, we should know about**

*winding factor***pitch factor**and

**distribution factor**, as winding factor is the product of pitch factor and distribution factor.

If winding factor is denoted by K

_{w}, pitch factor and distribution factor are denoted by K

_{p}and K

_{d}respectively, then, k

_{w}= k

_{p}k

_{d}.

The pitch factor and distribution factor are explained below one by one.

## Pitch Factor

In short pitched coil, the induced emf of two coil sides is vectorically added to get, resultant emf of the coil. In short pitched coil, the phase angle between the emfs induced in two opposite coil sides is less than 180^{o}(electrical). But we known that, in full pitched coil, the phase angle between the emfs induced in two coil sides is exactly 180

^{o}(electrical).

Hence, the resultant emf of a full pitched coil is just arithmetic sum of the emfs induced in both sides of the coil. We well know that, vector sum or phasor sum of two quantities, is always less than their arithmetic sum. Pitch factor is the measure of resultant emf of short pitched coil in comparison with resultant emf of full pitched coil.

Hence, it must be the ratio of phasor sum of induced emfs per coil to the arithmetic sum of induced emfs per coil. Hence, it must be less than unity.

Let’s a coil is short pitched by an angle α (electrical degree). Emf induced per coil side is E. The arithmetic sum of induced emfs is 2E. That means, 2E, is the induced voltage across the coil terminals, if the coil would have been full pitched.

Now, come to the short pitched coil. From the figure below it is clear that, resultant emf of the short pitched coil
Now, as per definition of pitched factor,
This pitch factor is for the fundamental component of emf. The flux wave may consists of space field harmonics also, which give rise to the corresponding time harmonics in the generated voltage wave form. A 3^{rd} harmonic component of the flux wave, may be imagined as produced by 3 poles as compared to one pole for the fundamental component.

In the view of this, the chording angle for the r^{th} harmonic becomes r times the chording angle for the fundamental component and pitch factor for the r^{th} harmonic is given as,
The r^{th} harmonic becomes zero, if,
In 3 phase alternator, the 3^{rd} harmonic is suppressed by star or delta connection as in the case of 3 phase transformer. Total attention is given for designing a 3 phase alternator winding design, for 5^{th} and 7^{th} harmonics.

For 5^{th} harmonic
For 7^{th} harmonic
Hence by adopting a suitable chording angle of α = 30^{o}, we make most optimized design armature winding of alternator.

## Distribution Factor

If all the coil side of any one phase under one pole are bunched in one slot, the winding obtained is known as concentrated winding and the total emf induced is equal to arithmetic sum of the emfs induced in all the coils of one phase under one pole.But in practical cases, for obtaining smooth sinusoidal voltage wave form, armature winding of alternator is not concentrated but distributed among the different slots to form polar groups under each pole. In distributed winding, coil sides per phase are displaced from each other by an angle equal to the angular displacement of the adjacent slots. Hence, the induced emf per coil side are not an angle equal to the angular displacement of the slots. So, the resultant emf of the winding is the phasor sum of the induced emf per coil side. As it is phasor sum, must be less than arithmetic sum of these induced emfs.

Resultant emf would be arithmetic sum, if the winding would have been a concentrated one.

As per definition, distribution factor, is measure of resultant emf of a distributed winding in compared to a concentrated winding.

It is expressed as ratio of the phasor sum of the emfs induced in all the coils distributed in a number of slots under one pole to the arithmetic sum of the emfs induced. Distribution factor is, As pitch factor, distribution factor is also always less than unity.

Let number of slots per pole is n.

Number of slots per pole per phase is m.

Induced emf per coil side is E

_{c}.

Angular displacement between the slots, The emfs induced in different coils of one phase under one pole are represented by AC, DC, DE, EF and so on. They are equal in magnitude but differ from each other by an angle β.

If bisectors are drawn on AC, CD, DE, EF--------. They would meet at common point O.

Emf induced in each coil side, As the slot per pole per phase is m, the total arithmetic sum of all induced emfs per coil sides per pole per phase, The resultant emf would be AB, as represented by the figure,

Hence, the resultant emf mβ is also known as the phase spread in electrical degree.

The distribution factor K

_{d}given by equation is for the fundamental component of emf.

If the flux distribution contains space harmonics the slot angular pitch β on the fundamental scale, would become rβ for the r

^{th}harmonic component and thus the distribution factor for the r

^{th}harmonic would be.

Therefore,

**winding factor**

**Comments/Feedbacks**

Closely Related Articles Armature Winding | Pole Pitch Coil Span Commutator PitchWave WindingLap Winding Simplex and Duplex Lap WindingFrog Leg Winding | Drum Winding | Gramme Ring WindingArmature Winding of AlternatorMore Related Articles Alternator Synchronous Generator | Definition and Types of AlternatorWorking Principle of AlternatorConstruction of AlternatorArmature Reaction in Alternator or Synchronous Generator Rating of AlternatorDerivation of Various Power Conditions in Alternators and Synchronous MotorsInduction Generator | Application of Induction GeneratorParallel Operation of AlternatorMotor Generator Set | M G SetPrinciple of DC GeneratorConstruction of DC Generator | Yoke Pole Armature Brushes of DC GeneratorCharacteristics of Series Wound DC GeneratorCharacteristic of Separately Excited DC GeneratorEMF Equation of DC GeneratorParallel Operation of DC GeneratorsSelf Excited DC GeneratorsHopkinson TestPhasor Diagram for Synchronous GeneratorDC Generators Performance CurvesTypes of DC GeneratorsCharacteristic of Shunt Wound DC GeneratorMagnetization Curve of DC GeneratorApplications of DC GeneratorsNew Articles Trees and Cotrees of Electric NetworkDifferentiatorIntegratorPhase Synchronizing Device or Controlled Switching DeviceDigital to Analog Converter or DACDifference Amplifier