Trees and Cotrees
PSD or CSD
Digital to Analog Converter
Difference AmplifierClosely Related Articles
Types of Winding
Construction of Alternator
Armature Reaction in Alternator
Rating of Alternator
Power Conditions in Alternators
Parallel Operation of Alternator
Motor Generator Set | M G Set
Principle of DC Generator
Construction of DC Generator
Characteristics of Series Wound DC Generator
Characteristic of Separately Excited DC Generator
EMF Equation of DC Generator
Parallel Operation of DC Generators
Self Excited DC Generators
Phasor Diagram for Synchronous Generator
DC Generators characteristics
Types of DC Generators
Characteristic of Shunt Wound DC Generator
Magnetization Curve of DC Generator
Applications of DC Generators
Armature Winding of Alternator
- First and most important property of an armature winding is, two sides of any coil should be under two adjacent poles. That means, coil span = pole pitch.
- The winding can either be single layer or double layer.
- Winding is so arranged in different armature slots, that it must produce sinusoidal emf.
Types of Armature Winding of AlternatorThere are different types of armature winding used in alternator. The windings can be classified as
- Single phase and poly phase armature winding.
- Concentrated winding and distributed winding.
- Half coiled and whole coiled winding.
- Single layer and double layer winding.
- Lap, wave and concentric or spiral winding and
- Full pitched coil winding and fractional pitched coil winding.
Single Phase Armature WindingSingle phase armature winding can be either concentrated or distributed type.
Concentrated Armature WindingConcentrated winding is employed where number of slots on the armature is equal to number of poles in the machine. This armature winding of alternator gives maximum output voltage but not exactly sinusoidal. The most simple single phase winding, is shown below in the figure-1. Here, number poles = number of slots = number of coil sides. Here, one coil side is inside one slot under one pole and other coil side inside other slot under next pole. Clearly the emf induced in one coil side is added to that of adjacent coil side. This arrangement of armature winding of alternator, is known as skelton wave winding. As per the fig-1, coil side-1 under N-pole is connected to coil side-2 under S-pole at the back and coil side-3 at the front and so on. The direction of induced emf of coil side-1 is upward and emf induced in coil side-2 is downward. Again as coil side-3 is under N-pole, it will have emf in upward direction and so on. Hence total emf is summation of emf of all coil sides. This form of armature winding is quite simple but rarely used as this requires considerable space for end connection of every coil side or conductor. This problem can be overcome, sum extent by using multi turns coil. In order to get higher emf, the multi turn half coiled winding is used. Since the coils cover only one half of the armature periphery thus, this winding is referred as half coiled or hemi - tropic winding. This is shown in fig-2. If the coils are distribute over the whole armature periphery, then the armature winding of alternator is referred as whole coiled winding. As shown in the fig-3 it is double layer winding, where one side of each coil placed on the top of armature slot where other side is placed in the bottom of the slot. (Represented by dotted lines). Hence it is essentially a double layer winding.
Distributed Armature Winding of AlternatorFor obtaining smooth sinusoidal emf wave from, conductors are placed is several slots under single pole. This armature winding is known as distribute winding. Although distributed armature winding of alternator, reduces emf but still it very much usable due to following reason.
- It also reduces harmonic emf and so wave form is improved.
- It also diminishes armature reaction.
- Even distribution of conductors, helps for better cooling.
- The core is fully utilized as the conductors are distributed over the slots on the armature periphery.
Lap Winding of AlternatorFull pitched lap winding of 4 poles, 12 slots, 12 conductors (one conductor per slot) alternator is shown below. The back pitch of the winding is equal to the number of conductors per pole i.e. = 3 and front pitch is equal to back pitch minus one. The winding is completed per pair of pole and then connected in series as shown in figure - 4 below.
Wave Winding of AlternatorWave winding of same machine i.e. 4 pole, 12 slots, 12 conductors is shown in the figure-e below. Here, back pitch and front pitch both equal to number of conductor per pole.
Concentric or Spiral WindingThis winding for same machine, i.e. 4 poles 12 slot 12 conductors alternator is shown in the figure-f below. In this winding the coils are of different pitches. The outer coil pitch is 5, the middle coil pitch is 3 and inner coil pitch is one.
Poly Phase Armature Winding of AlternatorBefore discussing poly phase armature winding of alternator, we should go through some of related terms for better understanding.
Coil GroupIt is product of number of phases and number of poles in a rotating machine. Coil group = number of poles Number of phases.
Balanced WindingIf under each pole face, there are equal number of coils of different phases, then the winding is said to be balanced winding. In balanced winding, coil group should be an even number.
Unbalanced WindingIf the number of coils per coil group is not a whole number, the winding is known as unbalanced winding. In such case each pole face contains unequal of coils of different phase. In two phase alternator, two single phase windings are placed on the armature by 90 electrical degree apart from each other. Incase of three phase alternator, three single-phase windings are placed on the armature, by 60 degree (electrical) apart from each other. The figure below represents, a Skelton 2 phase 4 pole winding two slots per pole. The electrical phase difference between adjacent slots = 180/2 = 90 degree electrical). Point a and b are starting point of first and second phase winding of two, phase alternator. a’ and b’ are finishing point of first and second phase wining of two phase alternator, respectively. Figure below represents a Skelton 3 phase 4 pole winding, 3 slots per pole. The electrical phase difference between, adjacent slots is 180/ 3 = 60 degree (electrical) a, b and c are starting point of Red, Yellow, and blue phases and a’, b’, and c’ are the finishing points of same Red, Yellow and Blue phases of the three phase winding. Say red phase winding starts at slot no 1 and ends over slot no 10. Then yellow winding or second winding starts at slot no 2 and ends over slot no 11. Third or blue phase winding starts at slot no 3 and ends at slot no 12. The phase difference of induced emfs, in red phase and yellow, yellow phase and blue phase and blue phase and red phase winding respective by 60 degree, 60 degree and 240 degree (electrical respectively). Since in three phase system, the phase difference between red, yellow and blue phase is 120 degree (electrical). This can be achieved by revering yellow phase (second winding) winding as shown in figure above.
Figure- below represents 4 pole, 24 slot, single layer, full pitched 3 phases distributed winding. No of slot per pole per phase _______________________ The phase difference between emfs induced in the conductors, of two adjacent slots is _________ Hence,
|Slots No: 1, 2, 7, 8, 13, 14, 19, and 20 for R phase|
|Slots No: 5, 6, 11, 12, 17, 18, 23 and 24 for Y phase|
|Slots No: 3, 4, 9, 10, 15, 16, 21 and 22 for B phase|
Integral Slot and Fractional Slot WindingWhen the number of slots per pole per phase is an integer, the winding is the integer slot winding but when the number slots per pole per phase is fractional number the winding is referred as fractional slot winding. Fractional slot winding is practicable only with double layered winding. It limits the number of parallel circuit available, because phase group under several poles must be connected in series before a unit is formed and the widening respects the pattern to give second unit that can be put in parallel with the first.
Closely Related Articles Armature Winding | Pole Pitch Coil Span Commutator PitchWave WindingWinding Factor | Pitch Factor | Distribution FactorLap Winding Simplex and Duplex Lap WindingFrog Leg Winding | Drum Winding | Gramme Ring WindingMore Related Articles Alternator Synchronous Generator | Definition and Types of AlternatorWorking Principle of AlternatorConstruction of AlternatorArmature Reaction in Alternator or Synchronous Generator Rating of AlternatorDerivation of Various Power Conditions in Alternators and Synchronous MotorsInduction Generator | Application of Induction GeneratorParallel Operation of AlternatorMotor Generator Set | M G SetPrinciple of DC GeneratorConstruction of DC Generator | Yoke Pole Armature Brushes of DC GeneratorCharacteristics of Series Wound DC GeneratorCharacteristic of Separately Excited DC GeneratorEMF Equation of DC GeneratorParallel Operation of DC GeneratorsSelf Excited DC GeneratorsHopkinson TestPhasor Diagram for Synchronous GeneratorDC Generators Performance CurvesTypes of DC GeneratorsCharacteristic of Shunt Wound DC GeneratorMagnetization Curve of DC GeneratorApplications of DC GeneratorsNew Articles Trees and Cotrees of Electric NetworkDifferentiatorIntegratorPhase Synchronizing Device or Controlled Switching DeviceDigital to Analog Converter or DACDifference Amplifier