# Short Transmission Line

The transmission lines which have length less than 50 km are generally referred as ** short transmission lines**.

For short length, the shunt capacitance of this type of line is neglected and other parameters like electrical resistance and inductor of these short lines are lumped, hence the equivalent circuit is represented as given below, Let’s draw the vector diagram for this equivalent circuit, taking receiving end current I

_{r}as reference. The sending end and receiving end voltages make angle with that reference receiving end current, of φ

_{s}and φ

_{r}, respectively.

As the shunt capacitance of the line is neglected, hence sending end current and receiving end current is same, i.e. .

__You may also be interested on__

Now if we observe the vector diagram carefully, we will get,
V_{s} is approximately equal to
That means,
as the it is assumed that
As there is no capacitance, during no load condition the current through the line is considered as zero, hence at no load condition, receiving end voltage is the same as sending end voltage.
As per dentition of voltage regulation of power transmission line,

Here, v_{r} and v_{x} are the per unit resistance and reactance of the **short transmission line** respectively.
Any electrical network generally has two input terminals and two output terminals. If we consider any complex electrical network in a black box, it will have two input terminals and output terminals. This network is called two - port network. Two port model of a network simplifies the network solving technique. Mathematically a two port network can be solved by 2 by 2 matrix.

A transmission as it is also an electrical network; line can be represented as two port network. Hence two port network of transmission line can be represented as 2 by 2 matrixes. Here the concept of ABCD parameters comes. Voltage and currents of the network can represented as ,

Where, A, B, C and D are different constant of the network.
If we put I_{r} = 0 at equation (1), we get,

_{r}= 0 at equation (1), we get That indicates it is impedance of the transmission line when the receiving terminals are short circuited. This parameter is referred as transfer impedance. C is the current in amperes into the sending end per volt on open circuited receiving end. It has the dimension of admittance. D is the current in amperes into the sending end per amp on short circuited receiving end. It is dimensionless. Now from equivalent circuit, it is found that, Comparing these equations with equation 1 and 2 we get, A = 1, B = Z, C = 0 and D = 1. As we know that the constant A, B, C and D are related for passive network as,

**short transmission line**. From above equation (1), When I

_{r}= 0 that means receiving end terminals is open circuited and then from the equation 1, we get receiving end voltage at no load. and as per definition of voltage regulation of power transmission line,