Discharging a Capacitor
Charging a Capacitor
Parity GeneratorClosely Related Articles
Trip Circuit Supervision
Differential Protection of Alternator
Rotor Earth Fault Protection of Alternator
Loss of Field or Excitation Protection of Alternator or Generator
Motor Protection Circuit Breaker
Stator Earth Fault Protection of Alternator
Inter Turn Fault Protection of Stator Winding of Generator
Motor Protection Scheme
Motor Thermal Overload Protection
Electrical Fault Calculation | Positive Negative Zero Sequence Impedance
External and Internal Faults in Transformer
Backup Protection of Transformer | Over Current and Earth Fault
Transformer Protection and Transformer Fault
Protection of Lines or Feeder
Busbar Protection | Busbar Differential Protection Scheme
Protection of Capacitor Bank
Types of Electrical Protection Relays or Protective Relays
Motor Protection Relay for High Voltage Induction Motor
Feeder Protection Relays
Pick Up Current | Current Setting | Plug Setting Multiplier and Time Setting Multiplier of Relay
Electromagnetic Relay Working | Types of Electromagnetic Relays
Induction Cup Relay Working Principle Construction and Types
Over Current Relay Working Principle Types
Thermal Relay Working Principle Construction of Thermal Overload Relay
Distance Relay or Impedance Relay Working Principle Types
Inverse Time Relay | Definite Time Lag Relay
Protection System in Power System
The close and trip, indication and alarm circuits different of circuit breakers are also included and explain.
Objective of Power System ProtectionThe objective of power system protection is to isolate a faulty section of electrical power system from rest of the live system so that the rest portion can function satisfactorily without any severer damage due to fault current.
Actually circuit breaker isolates the faulty system from rest of the healthy system and this circuit breakers automatically open during fault condition due to its trip signal comes from protection relay. The main philosophy about protection is that no protection of power system can prevent the flow of fault current through the system, it only can prevent the continuation of flowing of fault current by quickly disconnect the short circuit path from the system. For satisfying this quick disconnection the protection relays should have following functional requirements.
Protection System in Power SystemLet’s have a discussion on basic concept of protection system in power system and coordination of protection relays. In the picture the basic connection of protection relay has been shown. It is quite simple. The secondary of current transformer is connected to the current coil of relay. And secondary of voltage transformer is connected to the voltage coil of the relay. Whenever any fault occurs in the feeder circuit, proportionate secondary current of the CT will flow through the current coil of the relay due to which mmf of that coil is increased. This increased mmf is sufficient to mechanically close the normally open contact of the relay. This relay contact actually closes and completes the DC trip coil circuit and hence the trip coil is energized. The mmf of the trip coil initiates the mechanical movement of the tripping mechanism of the circuit breaker and ultimately the circuit breaker is tripped to isolate the fault.
Functional Requirements of Protection Relay
ReliabilityThe most important requisite of protective relay is reliability. They remain inoperative for a long time before a fault occurs; but if a fault occurs, the relays must respond instantly and correctly.
SelectivityThe relay must be operated in only those conditions for which relays are commissioned in the electrical power system. There may be some typical condition during fault for which some relays should not be operated or operated after some definite time delay hence protection relay must be sufficiently capable to select appropriate condition for which it would be operated.
SensitivityThe relaying equipment must be sufficiently sensitive so that it can be operated reliably when level of fault condition just crosses the predefined limit.
SpeedThe protective relays must operate at the required speed. There must be a correct coordination provided in various power system protection relays in such a way that for fault at one portion of the system should not disturb other healthy portion. Fault current may flow through a part of healthy portion since they are electrically connected but relays associated with that healthy portion should not be operated faster than the relays of faulty portion otherwise undesired interruption of healthy system may occur. Again if relay associated with faulty portion is not operated in proper time due to any defect in it or other reason, then only the next relay associated with the healthy portion of the system must be operated to isolate the fault. Hence it should neither be too slow which may result in damage to the equipment nor should it be too fast which may result in undesired operation.
Important Elements for Power System Protection
SwitchgearConsists of mainly bulk oil circuit breaker, minimum oil circuit breaker, SF6 circuit breaker, air blast circuit breaker and vacuum circuit breaker etc. Different operating mechanisms such as solenoid, spring, pneumatic, hydraulic etc. are employed in the circuit breaker. Circuit breaker is the main part of protection system in power system and it automatically isolate the faulty portion of the system by opening its contacts.
Protective GearConsists of mainly power system protection relays like current relays, voltage relays, impedance relays, power relays, frequency relays, etc. based on operating parameter, definite time relays, inverse time relays, stepped relays etc. as per operating characteristic, logic wise such as differential relays, over fluxing relays etc. During fault the protection relay gives trip signal to the associated circuit breaker for opening its contacts.
Station BatteryAll the circuit breakers of electrical power system are DC (Direct Current) operated. Because DC power can be stored in battery and if situation comes when total failure of incoming power occurs, still the circuit breakers can be operated for restoring the situation by the power of storage station battery. Hence, the battery is another essential item of the power system. Some time it is referred as the heart of the electrical substation. An electrical substation battery or simply a station battery containing a number of cells accumulate energy during the period of availability of AC supply and discharge at the time when relays operate so that relevant circuit breaker is tripped at the time failure of incoming AC power.
Closely Related Articles Trip Circuit SupervisionDifferential Protection of Generator or AlternatorAnnunciation System Alarm AnnunciatorRotor Earth Fault Protection of Alternator or GeneratorLoss of Field or Excitation Protection of Alternator or GeneratorOvervoltage ProtectionMotor Protection Circuit Breaker or MPCBStator Earth Fault Protection of AlternatorInter Turn Fault Protection of Stator Winding of GeneratorSmall and Large Motor Protection Scheme Motor Thermal Overload ProtectionElectrical Fault Calculation | Positive Negative Zero Sequence ImpedanceExternal and Internal Faults in TransformerBackup Protection of Transformer | Over Current and Earth FaultTransformer Protection and Transformer FaultGenerator ProtectionProtection of Lines or Feeder Busbar Protection | Busbar Differential Protection SchemeProtection of Capacitor BankMore Related Articles Types of Electrical Protection Relays or Protective RelaysMotor Protection Relay for High Voltage Induction MotorFeeder Protection RelaysPick Up Current | Current Setting | Plug Setting Multiplier and Time Setting Multiplier of RelayElectromagnetic Relay Working | Types of Electromagnetic RelaysInduction Cup Relay Working Principle Construction and Types Over Current Relay Working Principle TypesDifferential RelayThermal Relay Working Principle Construction of Thermal Overload RelayDistance Relay or Impedance Relay Working Principle TypesInstantaneous RelayInverse Time Relay | Definite Time Lag RelayBackup RelayNew Articles Ring CounterDischarging a CapacitorCharging a CapacitorElectric PotentialParity Generator