Air Circuit Breaker Air Blast Circuit BreakerPublished on 24/2/2012 and last updated on 13/8/2018
This type of circuit breakers, is those kind of circuit breaker which operates in air at atmospheric pressure. After development of oil circuit breaker, the medium voltage air circuit breaker (ACB) is replaced completely by oil circuit breaker in different countries. But in countries like France and Italy, ACBs are still preferable choice up to voltage 15 KV. It is also good choice to avoid the risk of oil fire, in case of oil circuit breaker. In America ACBs were exclusively used for the system up to 15 KV until the development of new vacuum and SF6 circuit breakers.Please Rate this Article
Working Principle of Air Circuit BreakerThe working principle of this breaker is rather different from those in any other types of circuit breakers. The main aim of all kind of circuit breaker is to prevent the reestablishment of arcing after current zero by creating a situation where in the contact gap will withstand the system recovery voltage. The air circuit breaker does the same but in different manner. For interrupting arc it creates an arc voltage in excess of the supply voltage. Arc voltage is defined as the minimum voltage required maintaining the arc. This circuit breaker increases the arc voltage by mainly three different ways,
- It may increase the arc voltage by cooling the arc plasma. As the temperature of arc plasma is decreased, the mobility of the particle in arc plasma is reduced; hence more voltage gradient is required to maintain the arc.
- It may increase the arc voltage by lengthening the arc path. As the length of arc path is increased, the resistance of the path is increased, and hence to maintain the same arc current more voltage is required to be applied across the arc path. That means arc voltage is increased.
- Splitting up the arc into a number of series arcs also increases the arc voltage.
Types of ACBThere are mainly two types of ACB are available.
- Plain air circuit breaker.
- Air blast Circuit Breaker.
Operation of ACB
- The first objective is usually achieved by forcing the arc into contact with as large an area as possible of insulating material. Every air circuit breaker is fitted with a chamber surrounding the contact. This chamber is called 'arc chute'. The arc is driven into it. If inside of the arc chute is suitably shaped, and if the arc can be made conform to the shape, the arc chute wall will help to achieve cooling. This type of arc chute should be made from some kind of refractory material. High temperature plastics reinforced with glass fiber and ceramics are preferable materials for making arc chute.
- The second objective that is lengthening the arc path, is achieved concurrently with fist objective. If the inner walls of the arc chute is shaped in such a way that the arc is not only forced into close proximity with it but also driven into a serpentine channel projected on the arc chute wall. The lengthening of the arc path increases the arc resistance.
- The third technique is achieved by using metal arc slitter inside the arc chute. The main arc chute is divided into numbers of small compartments by using metallic separation plates. These metallic separation plates are actually the arc splitters and each of the small compartments behaves as individual mini arc chute. In this system the initial arc is split into a number of series arcs, each of which will have its own mini arc chute. So each of the split arcs has its own cooling and lengthening effect due to its own mini arc chute and hence individual split arc voltage becomes high. These collectively, make the overall arc voltage, much higher than the system voltage.
Air Blast Circuit BreakerThese types of air circuit breaker were used for the system voltage of 245 KV, 420 KV and even more, especially where faster breaker operation was required. Air blast circuit breaker has some specific advantages over oil circuit breaker which are listed as follows,
- There is no chance of fire hazard caused by oil.
- The breaking speed of circuit breaker is much higher during operation of air blast circuit breaker.
- Arc quenching is much faster during operation of air blast circuit breaker.
- The duration of arc is same for all values of small as well as high currents interruptions.
- As the duration of arc is smaller, so lesser amount of heat realized from arc to current carrying contacts hence the service life of the contacts becomes longer.
- The stability of the system can be well maintained as it depends on the speed of operation of circuit breaker.
- Requires much less maintenance compared to oil circuit breaker.
There are also some disadvantages of air blast circuit breakers-
- In order to have frequent operations, it is necessary to have sufficiently high capacity air compressor.
- Frequent maintenance of compressor, associated air pipes and automatic control equipments is also required.
- Due to high speed current interruption there is always a chance of high rate of rise of re-striking voltage and current chopping.
- There also a chance of air pressure leakage from air pipes junctions.
- Axial Blast ACB.
- Axial Blast ACB with side moving contact.
- Cross Blast ACB.