Insulation Resistance Measurement
Ampere's Circuital Law
Mechanical Equivalent of Heat
Trees and Cotrees
IntegratorClosely Related Articles
Circuit Breaker Maintenance
Routine Tests of CB
Remote Controlling of Circuit Breaker
Circuit Breaker Operation
Ratings of CB
Short Circuit Current of Circuit Breaker
Air Circuit Breaker
Oil Circuit Breaker
Vacuum Circuit Breaker
Residual Current Circuit Breaker
Arc in CB
Arc Interruption Theory
Arc in Vacuum
Miniature Circuit Breaker
ELCB and RCCB
Electrical Power Distribution
Gas Insulated Switchgear
Metal Enclosed Switchgear
Basic Insulation Level
Electrical Circuit Breaker | Operation and Types of Circuit Breaker
What is Circuit Breaker?Electrical circuit breaker is a switching device which can be operated manually and automatically for controlling and protection of electrical power system respectively. As the modern power system deals with huge currents, the special attention should be given during designing of circuit breaker for safe interruption of arc produced during the operation of circuit breaker. This was the basic definition of circuit breaker.
Introduction to Circuit BreakerThe modern power system deals with huge power network and huge numbers of associated electrical equipments. During short circuit fault or any other types of electrical fault these equipment as well as the power network suffer a high stress of fault current in them which may damage the equipment and networks permanently.
For saving these equipment and the power networks the fault current should be cleared from the system as quickly as possible. Again after the fault is cleared, the system must come to its normal working condition as soon as possible for supplying reliable quality power to the receiving ends. In addition to that for proper controlling of power system, different switching operations are required to be performed. So for timely disconnecting and reconnecting different parts of power system network for protection and control, there must be some special type of switching devices which can be operated safely under huge current carrying condition. During interruption of huge current, there would be large arcing in between switching contacts, so care should be taken to quench these arcs in circuit breaker in safe manner. The circuit breaker is the special device which does all the required switching operations during current carrying condition. This was the basic introduction to circuit breaker.
Working Principle of Circuit BreakerThe circuit breaker mainly consists of fixed contacts and moving contacts. In normal "ON" condition of circuit breaker, these two contacts are physically connected to each other due to applied mechanical pressure on the moving contacts. There is an arrangement stored potential energy in the operating mechanism of circuit breaker which is released if switching signal is given to the breaker. The potential energy can be stored in the circuit breaker by different ways like by deforming metal spring, by compressed air, or by hydraulic pressure. But whatever the source of potential energy, it must be released during operation. Release of potential energy makes sliding of the moving contact at extremely fast manner. All circuit breaker have operating coils (tripping coils and close coil), whenever these coils are energized by switching pulse, and the plunger inside them displaced. This operating coil plunger is typically attached to the operating mechanism of circuit breaker, as a result the mechanically stored potential energy in the breaker mechanism is released in forms of kinetic energy, which makes the moving contact to move as these moving contacts mechanically attached through a gear lever arrangement with the operating mechanism. After a cycle of operation of circuit breaker the total stored energy is released and hence the potential energy again stored in the operating mechanism of circuit breaker by means of spring charging motor or air compressor or by any other means. Till now we have discussed about mechanical working principle of circuit breaker. But there are electrical characteristics of a circuit breaker which also should be considered in this discussion of operation of circuit breaker.
Let's have a discussion on electrical principle of circuit breaker. The circuit breaker has to carry large rated or fault power. Due to this large power there is always dangerously high arcing between moving contacts and fixed contact during operation of circuit breaker. Again as we discussed earlier the arc in circuit breaker can be quenching safely if the dielectric strength between the current carrying contacts of circuit breaker increases rapidly during every current zero crossing of the alternating current. The dielectric strength of the media in between contacts can be increased in numbers of ways, like by compressing the ionized arcing media since compressing accelerates the deionization process of the media, by cooling the arcing media since cooling increase the resistance of arcing path or by replacing the ionized arcing media by fresh gasses. Hence a numbers of arc quenching processes should be involved in operation of circuit breaker.
Types of Circuit BreakerAccording different criteria there are different types of circuit breaker. According to their arc quenching media the circuit breaker can be divided as- According to their arc quenching media the circuit breaker can be divided as- According to their services the circuit breaker can be divided as-
- Outdoor circuit breaker
- Indoor breaker.
- Spring operated circuit breaker.
- Pneumatic circuit breaker.
- Hydrolic circuit breaker.
- High voltage circuit breaker.
- Medium voltage circuit breaker.
- Low voltage circuit breaker.
Closely Related Articles Circuit Breaker MaintenanceHigh Voltage Testing | Low Frequency Constant DC High Frequency Surge or Impulse TestSulfur Hexafluoride | SF6 Gas PropertiesRoutine Tests of Circuit BreakersRemote Controlling of Circuit Breaker by MicrocontrollerCircuit Breaker Operation Rating of Circuit Breaker | Short Circuit Breaking Making CurrentShort Circuit Current of Circuit BreakerAir Circuit Breaker Air Blast Circuit BreakerOil Circuit Breaker Bulk and Minimum Oil Circuit BreakerTypes and Operation of SF6 Circuit BreakerVacuum Circuit Breaker or VCB and Vacuum InterrupterResidual Current Circuit BreakerDielectric GasesMore Related Articles What is an Arc ? | Arc in Circuit BreakerArc Interruption TheoryVacuum Arc or Arc in VacuumElectrical Fuse HRC Fuse High Rupturing CapacityMiniature Circuit Breaker or MCBWorking Principle of Earth Leakage Circuit Breaker ELCB | Voltage and Current ELCB | RCCBElectrical Power Distribution System | Radial and Ring Main Electrical Switchgear ProtectionElectrical Isolator or Electrical Isolation SwitchLow Voltage Switchgear or LV SwitchgearMedium Voltage Switchgear High Voltage SwitchgearGIS or Gas Insulated SwitchgearMetal Enclosed SwitchgearVacuum Switchgear ZnO Gapless Lightning Arrester or Surge ArresterBIL or Basic Insulation Level Definition Table and CalculationNew Articles Measurement of Insulation ResistanceAmpere's Circuital LawMechanical Equivalent of HeatTrees and Cotrees of Electric NetworkDifferentiatorIntegrator