Principle of Water Content Test of Insulating Oil
Collecting Oil Sample from Oil Immersed Electrical Equipment
Causes of Insulating Oil Deterioration
Acidity Test of Transformer Insulating Oil
Magnetic FieldClosely Related Articles
Electric Power Generation
Power Plants and Types of Power Plant
Thermal Power Generation Plant or Thermal Power Station
Hydro Power Plant | Construction Working and History of Hydro power plant
Nuclear Power Station or Nuclear Power Plant
Diesel Power Station
Why Supply Frequency is 50 Hz or 60 Hz?
Economiser in Thermal Power Plant | Economiser
MHD Generation or Magneto Hydro Dynamic Power Generation
Cogeneration | Combined Heat and Power
Thermoelectric Power Generators or Seebeck Power Generation
Cost of Electrical Energy
Gas Turbine Power Plant
Steam Boiler | Working principle and Types of Boiler
Methods of Firing Steam Boiler
Fire Tube Boiler | Operation and Types of Fire Tube Boiler
Water Tube Boiler | Operation and Types of Water Tube Boiler
Steam Boiler Furnace Grate Firebox Combustion Chamber of Furnace
Feed Water and Steam Circuit of Boiler
Boiler Feed Water Treatment Demineralization Reverse Osmosis Plant Deaerator
Coal Combustion Theory
Fluidized Bed Combustion | Types and Advantages of Fluidized Bed Combustion
Steam Condenser of Turbine
Jet Condenser | Low Level High Level Ejector Jet Condenser
Surface Steam Condenser
Economics of Power Generation
Cooling Tower Useful Terms and Cooling Tower Performance
Cooling Tower Material and Main Components
Power Plant Fire Protection System
Hydrant System for Power Plant Fire Protection
Medium Velocity Water Spray or MVWS System for Fire Protection
Foam Fire Protection System
Fire Detection and Alarm System
Gas Extinguishing System
Solar Energy System
Types of Solar Power Station
Components of a Solar Electric Generating System
Staebler Wronski Effect
Principle of Photovoltaic Cell
Characteristics of Solar Cell
Solar Cell Manufacturing Technology
Solar PV Module
Standalone Solar Electric System
Steam Dryness Fraction
Superheated Steam and Steam Phase Diagram
Vapour Properties Mollier Chart Heat Capacities
How to Calculate Steam Consumption During Plant Start Up
Effective Steam Distribution System
Engineering Thermodynamics Part 1
Engineering Thermodynamics Part 2
First Law of Thermodynamics
Enthalpy Entropy and Second Law of Thermodynamics
Rankine Cycle and Regenerative Feed Heating
Rankine Cycle for Closed Feed Water Heaters and Rankine Cycle Cogeneration
Ideal Verses Actual Rankine Cycle
Rankine Cycle Efficiency Improvement Techniques
Wind Energy Electricity Generation
Theory of Wind Turbine
Basic Construction of Wind Turbine
Electric Power Generation
Electric Power GenerationThe AC power is generated in 3 phase system as 3-phase AC electric power generation is most economical. 3 phase AC generator is commonly known as the alternator. An alternator has balanced three phase winding on its stator and an electromagnetic field is rotated inside the stator.
Due to this system, rotating magnetic field cuts the stator winding’s conductor and as a result, electricity is induced in the stator windings. From terminals of the stator three phase power is obtained. In an alternator, rotating electromagnet is energized by the DC source. The rotor is driven by some external means with the help of thermal, hydel, wind or other forms of energy. For example, in thermal power plant, the rotor of the alternator is rotated by means of a turbine shaft and the turbine is driven by means of high temperature and pressure steam. The steam is produced in a boiler by burning coal in the furnace.
As the stator winding is perfectly balanced, the three phase power produced in an alternator is also balanced that means phase difference between two conjugative phases is 120 degrees (electrical).
Frequency, Voltage and Interconnected SystemIf p is the number of poless and N is the RPM of an alternator, frequency of the generated voltage will be Np/120. In India the frequency of generated power or simply power frequency is 50 Hz. In USA it is 60 Hz. In modern power plants there are generally more than one number of alternators run in parallel. Not only in a single plant, may alternators, of other plants also be interconnected to run parallel. This arrangement improves flexibility and efficiency of the power system. When the power stations of different locations are interconnected by means of transmission lines, the total network is referred as a grid. In other word grid is a system by which alternators of all power plants connected to that grid run in parallel. If any of the alternators becomes out of service, still power can be fed by other alternators without affecting availability of the system. As many numbers of alternators are connected and run in parallel, the frequency and voltage of the system becomes much stable irrespective of degree of loading present in the system. The main drawback of the grid system is, when an alternator is connected to the grid, its frequency, voltage and phase sequence must match with that of the grid, and the process of matching the said parameters of alternator with the grid is not a simple task and the process is called synchronizing.
Conventional Source of Electric Power GenerationThere are mainly three conventional source of electric power generation, and they are thermal hydel, and nuclear energy.
Thermal Power GenerationIn thermal power plant coal or diesel is burnt to produce sufficient heat. This heat energy is utilized to produce high temperature and high pressure steam in the boiler. This steam is then passed through the turbine blades and the turbine shaft rotates due to this steam pressure. The rotor of an alternator is mechanically coupled with the turbine shaft and hence it also rotates. This rotation produces electric power.
Hydel Power GenerationHere the water head is used to rotate the rotor shaft of an alternator. Water head can be naturally available or it can be created. In hilly region water head can be naturally available in the hill top natural lakes. In plain land, it can be created by constructing dams across suitable rivers. In comparing to a thermal power plant, hydel plants are more echo-friendly as they are free from fuel combustion. Also the running cost of hydel plant is much cheaper than that of thermal plants as there is no need of fuel to be burnt. Although running cost of a hydel power plant is quite low, but initial constructional cost of this plant is quite high as compared to thermal power plant. There is huge involvement of money in construction of dams and other necessary civil buildings. Water turbine generally runs at a low speed, hence number of poles in the generator is higher to achieve fixed 50 Hz power frequency. The number of pole in a hydel alternator may be up to 20 or more.
Nuclear Power GenerationIt is estimated that, the coal reserve of our country will be exhausted within next 40 years if the coal is continued to be consumed in present rate. The solution of this situation is a nuclear power plant as thought. In a nuclear power station, Uranium235 is subjected to nuclear fission. In fission process, U235 is bombarded by a beam of neutrons. The collision of neutrons with the nucleus of U235 creates huge heat energy along with other neutrons. These newly created neutrons are called fission neutrons which again hit by other U235 nuclear and create mare heat energy and other fission neutrons. During fission process the nucleus of U235 is divided into two parts. The fission process is commutative in nature. That is why, a nuclear reaction is a chain reaction and hence it should be allowed to be occurred in a controlled manner. The moderates and control rods are used to control this chain reaction. Moderators are used to reduce the velocity of neutrons and control rods are used to absorb neutrons for maintaining, required number of neutrons for the process. Moderators are made of heavy water or pure carbon and control rods are made of cadmium or boron steel. The speed of the nuclear reaction can be controlled by inserting control rods up to a desire deep into the reaction chamber. By pushing down and pulling up the control rods, the output of the nuclear generating plant is controlled. Although this process is not manual, it is controlled by the automatic feedback control system. The heat generated during fission is taken out from the reactor by means of coolant consisting of liquid sodium or some gaseous fluids. The coolant is circulated between heat exchanger and the reactor. It takes heat from the reactor and gives the heat to the water in the heat exchanger. Thus the water in the heat exchanger is converted to high pressure and high temperature steam. This steam then drives a turbine and exhausts into a condenser where it is condensed into water and cooled down for re- feeding to the heater changes again via a feed water pump. The main advantage of nuclear power plant is its minimum fuel consumption. It has been observed that for running a 1000 MW thermal power plant, nearly 6 × 106 kg of coal to be burnt every day, whereas in a nuclear power plant only 2.5 kg of Uranium to be consumed daily for getting same output. But the initial investment of nuclear power plant is quite high. It produces electricity without causing any air pollution, but, it has always a chance of radiation hazard because of leakage in reactor chamber. Another major disadvantage of this plant is its disposals, as because its disposals are not free from radioactivity.
Non Conventional Source of Electrical Power GenerationAlthough the main sources of electric power generation are thermal, hydel, and nuclear power plants, but still there are many other non conventional sources of power available. These non conventional sources, like wind power, solar power, MHD generation, biomass, fuel cell, etc. are becoming the promising alternative sources for electric power generation.
Closely Related Articles Power Plants and Types of Power PlantThermal Power Generation Plant or Thermal Power StationHydro Power Plant | Construction Working and History of Hydro power plantNuclear Power Station or Nuclear Power PlantDiesel Power StationWhy Supply Frequency is 50 Hz or 60 Hz?Economiser in Thermal Power Plant | EconomiserMHD Generation or Magneto Hydro Dynamic Power Generation Cogeneration | Combined Heat and PowerThermoelectric Power Generators or Seebeck Power GenerationCost of Electrical EnergyGas Turbine Power PlantNuclear ReactorMore Related Articles Steam Boiler | Working principle and Types of BoilerMethods of Firing Steam BoilerFire Tube Boiler | Operation and Types of Fire Tube BoilerWater Tube Boiler | Operation and Types of Water Tube BoilerSteam Boiler Furnace Grate Firebox Combustion Chamber of FurnaceFeed Water and Steam Circuit of BoilerBoiler Feed Water Treatment Demineralization Reverse Osmosis Plant DeaeratorCoal Combustion TheoryFluidized Bed Combustion | Types and Advantages of Fluidized Bed CombustionSteam Condenser of TurbineJet Condenser | Low Level High Level Ejector Jet CondenserSurface Steam Condenser Economics of Power GenerationCooling Tower Useful Terms and Cooling Tower PerformanceCooling Tower Material and Main ComponentsPower Plant Fire Protection SystemHydrant System for Power Plant Fire ProtectionMedium Velocity Water Spray or MVWS System for Fire ProtectionFoam Fire Protection SystemFire Detection and Alarm SystemGas Extinguishing SystemSolar ElectricitySolar Energy System | History of Solar EnergyTypes of Solar Power StationComponents of a Solar Electric Generating SystemWhat is Photovoltaic Effect?Staebler Wronski EffectWorking Principle of Photovoltaic Cell or Solar CellSolar CellCharacteristics of a Solar Cell and Parameters of a Solar CellSolar Cell Manufacturing TechnologyWhat is a Solar PV Module?What is Standalone Solar Electric System?Solar LanternSteamSteam Dryness FractionSuperheated Steam and Steam Phase DiagramVapour Properties Mollier Chart Heat CapacitiesWhat is Steam Flashing?How to Calculate Steam Consumption During Plant Start Up Effective Steam Distribution SystemWhat is Water Hammer?Engineering Thermodynamics Part 1Science of Engineering Thermodynamics Part 2Basic Law of Conservation and First Law of Thermodynamics Carnot Cycle and Reversed Carnot CycleEnthalpy Entropy and Second Law of ThermodynamicsRankine CycleRankine Cycle and Regenerative Feed HeatingRankine Cycle for Closed Feed Water Heaters and Rankine Cycle CogenerationIdeal Verses Actual Rankine CycleRankine Cycle Efficiency Improvement TechniquesWind Energy Electricity GenerationTheory of Wind Turbine Wind Turbine | Working and Types of Wind TurbineBasic Construction of Wind TurbineNew Articles Principle of Water Content Test of Insulating OilCollecting Oil Sample from Oil Immersed Electrical EquipmentCauses of Insulating Oil DeteriorationAcidity Test of Transformer Insulating OilMagnetic Flux