Insulation Resistance Measurement
Ampere's Circuital Law
Mechanical Equivalent of Heat
Trees and Cotrees
IntegratorClosely Related Articles
Speed Regulation of DC Motor
Speed Control of DC Motor
DC Motor Working
Torque in DC Motor
Construction of DC Motor
Testing of DC Machine
Swinburne Test of DC Machine
Losses in DC Machine
Ward Leonard Method
Armature Reaction in DC Machine
Commutation in DC Machine
Methods of Improving Commutation
Starting Methods for DC Motor
3 Point Starter
4 Point Starter
Working of Motor
Types of DC Motor
DC Shunt Motor
DC Series Motor
DC Compound Motor
Brushless DC Motors
4 Point Starter | Working Principle and Construction of Four Point Starter
Working Principle of Four Point StarterThe 4 point starter like in the case of a 3 point starter also acts as a protective device that helps in safeguarding the armature of the shunt or compound excited DC motor against the high starting current produced in the absence of back emf at starting. The 4 point starter has a lot of constructional and functional similarity to a three point starter, but this special device has an additional point and a coil in its construction. This naturally brings about some difference in its functionality, though the basic operational characteristic remains the same. The basic difference in circuit of 4 point starter as compared to 3 point starter is that the holding coil is removed from the shunt field current and is connected directly across the line with current limiting resistance in series.
Now to go into the details of operation of 4 point starter, lets have a look at its constructional diagram, and figure out its point of difference with a 3 point starter.
Construction and Operation of Four Point StarterA 4 point starter as the name suggests has 4 main operational points, namely
- 'L' Line terminal. (Connected to positive of supply.)
- 'A' Armature terminal. (Connected to the armature winding.)
- 'F' Field terminal. (Connected to the field winding.)
- Like in the case of the 3 point starter, and in addition to it there is, A 4th point N. (Connected to the No Voltage Coil NVC)
Apart from this above mentioned fact, the 4 point and 3 point starters are similar in all other ways like possessing is a variable resistance, integrated into number of sections as shown in the figure above. The contact points of these sections are called studs and are shown separately as OFF, 1, 2, 3, 4, 5, RUN, over which the handle is free to be maneuvered manually to regulate the starting current with gathering speed. Now to understand its way of operating lets have a closer look at the diagram given above. Considering that supply is given and the handle is taken stud No.1, then the circuit is complete and line current that starts flowing through the starter. In this situation we can see that the current will be divided into 3 parts, flowing through 3 different points.
- 1 part flows through the starting resistance (R1+ R2+ R3…..) and then to the armature.
- A 2nd part flowing through the field winding F.
- And a 3rd part flowing through the no voltage coil in series with the protective resistance R.
So the point to be noted here is that with this particular arrangement any change in the shunt field circuit does not bring about any change in the no voltage coil as the two circuits are independent of each other. This essentially means that the electromagnet pull subjected upon the soft iron bar of the handle by the no voltage coil at all points of time should be high enough to keep the handle at its RUN position, or rather prevent the spring force from restoring the handle at its original OFF position, irrespective of how the field rheostat is adjusted. This marks the operational difference between a 4 point starter and a 3 point starter. As otherwise both are almost similar and are used for limiting the starting current to a shunt wound DC motor or compound wound DC motor, and thus act as a protective device.
Closely Related Articles DC Motor or Direct Current MotorSpeed Regulation of DC MotorSpeed Control of DC MotorWorking or Operating Principle of DC MotorTorque Equation of DC MotorConstruction of DC Motor | Yoke Poles Armature Field Winding Commutator Brushes of DC MotorTesting of DC MachineSwinburne Test of DC MachineLosses in DC MachineWard Leonard Method of Speed ControlArmature Reaction in DC MachineCommutation in DC Machine or Commutation in DC Generator or MotorMethods of Improving CommutationStarting Methods to limit Starting Current and Torque of DC Motor3 Point Starter | Working Principle and Construction of Three Point StarterMore Related Articles Electrical Motor | Types Classification and History of MotorWorking of Electric MotorTypes of DC Motor Separately Excited Shunt Series Compound DC MotorShunt Wound DC Motor | DC Shunt MotorSeries Wound DC Motor or DC Series MotorCompound Wound DC Motor or DC Compound MotorPermanent Magnet DC Motor or PMDC Motor | Working Principle ConstructionBrushless DC MotorsNew Articles Measurement of Insulation ResistanceAmpere's Circuital LawMechanical Equivalent of HeatTrees and Cotrees of Electric NetworkDifferentiatorIntegrator