Resistance of Earth
Arc Suppression Coil or Petersen Coil
Winding Resistance Test of Shunt Reactor
Measurement of Reactance of a Shunt Reactor
Tests of Shunt ReactorClosely Related Articles
Types of Reactor
Applications of Reactors
Construction of Shunt Reactor
Tests of Shunt Reactor
Measurement of Reactance
Measurement of Resistance
Testing of Power Cable
Insulation Thickness Test
Types of Capacitor Bank
Testing of Capacitor Bank
Rating of Capacitor Bank
Switchable Capacitor Bank
Location of Capacitor Bank
Resistance of Earth
Types of Insulator
Dielectric Properties of Insulation
Transmission Tower Foundation
Towers in different Soils
Advantages of Three Phase System over Single Phase System
Inductance of Single Conductor
Inductance in Three Phase Line
Why Supply Frequency 50 or 60 Hz not Other Values than these?
Power System Stability
Load Flow Analysis
Flexible AC Transmission Systems
Tariff of Electricity
Inductance of Single Phase System
Load Flow and Y Bus
Equal Area Criterion
Steady State Stability
Electrical Transmission System
Short Transmission Line
Medium Transmission Line
Long Transmission Line
Performance of Transmission Line
Surge Impedance Loading
Advantages of Bundled Conductors
Ground Clearance of Different Transmission Lines
Winding Resistance Test of Shunt Reactor
- Calculation of copper losses.
- Calculation of winding temperature at the end of the winding temperature rise test cycle.
- Indication of any damage occurs in the winding system.
Principle of Winding Resistance MeasurementPreviously, winding resistance was measured by Kelvin Bridge method but it was quite laborious and time consuming. In present days, constant current resistance measuring kit is used for that. In this measurement constant current is injected between two terminals of the winding across which the resistance to be measured. It may be between two phase terminals or between phase and neutral terminals. The resistance is measured by the ratio of voltage measured between the terminals and that injected current. There are different resistance measuring instruments available. The basic principle is same. The instruments show resistance value directly on the display screen after calculation
Reactor, transformer or other similar equipment has high value of reactance. So, the DC resistance value can only be obtained after the injected current reaches its steady state constant value. So, the reading cannot be taken instantaneously, we have to wait for sufficient time to get constant injected current through the winding. This is why, prolong time is taken by the winding measurement test in the case of large transformer or reactor. From, the above equation, it is clear that induction portion of the voltage only becomes zero when current gets its steady state constant value. Then, only we can get reliable value of resistance R from ration V/I.
When to Measure Winding Resistance?There may be a chance of damage occurs in the winding (loose connection or open connection), tap changer (In case of transformer) or connectors during loading the equipment on the transport vehicle in factory, during unloading the equipment from the vehicle at site or during erection at site. This damage may lead a change in DC resistance of the path through them. That is why it is mandatory to conduct DC resistance measurement test before commissioning of the equipment. The result of the field test must be tallied with factory test result. To ensure each tap changer contact is intact after transportation and erection, the winding resistance measurement should be conducted at each tap position in case of power transformer. The test result should be kept as future reference.
Some time there is huge fault occurs in the equipment. During which there may be a chance of damage in the windings and its connections points. So, it may be recommended to perform winding resistance test after the fault to ensure about healthiness of the current carrying path of the equipment before re-energizing. It also helps to analyze the phase and location of the fault.
Closely Related Articles Types of Electrical ReactorSelection of Reactor for Different ApplicationsConstruction of a Shunt ReactorTests of Shunt ReactorMeasurement of Reactance of a Shunt ReactorArc Suppression Coil or Petersen CoilMore Related Articles Electrical Power Cable Types of Overhead ConductorTesting of Electrical Power Cable | Type Test | Acceptance Test | Routine TestConductor Resistance Test of Electrical Power CablesTest for Thickness of Insulation of Power CableAnnealing Test for Wires and Conductors Tensile Test of ConductorsPersulphate Test of ConductorWrapping Test for ConductorsCapacitor Bank | Reactive Power CompensationTypes of Capacitor BankTesting of Capacitor BankSpecifications or Rating of Power Capacitor BankShunt Capacitor Switchable Capacitor Bank or Switched Capacitor BankLocation of Shunt CapacitorsResistance of EarthSystem EarthingEquipment Earthing Electrical Insulator | Insulating Material | Porcelain Glass Polymer InsulatorTypes of Electrical Insulator | Overhead InsulatorInsulation Coordination in Power SystemElectrical Insulator Testing | Cause of Insulator failureDielectric Properties of InsulationElectrical Power Substation Engineering and LayoutElectrical Bus System and Electrical Substation LayoutMobile Substation | Portable Substation | Mobile TransformerLoad Curve | Load Duration Curve | Daily Load CurveHigh Voltage Direct Current Transmission | HVDC TransmissionElectrical Transmission Tower Types and DesignMethods of Transmission Tower ErectionBasic Concept of Transmission Tower FoundationDesign of Foundations of Transmission Towers in different SoilsCorona Effect in Power SystemFerranti Effect in Power SystemAdvantages of Three Phase System over Single Phase SystemInductance in Single Conductor Power Transmission LineInductance in Three Phase Transmission LineWhy Supply Frequency 50 or 60 Hz not Other Values than these?Power System StabilityLoad Flow or Power Flow AnalysisTransient Stability in Power SystemFlexible AC Transmission Systems | FACTSTariff of Electricity in IndiaPower Factor | Calculation and Power Factor ImprovementSkin Effect in Transmission LinesInductance of Two Wire Single Phase Transmission LineAuto Reclosing Scheme of Transmission SystemLoad Flow and Y BusEqual Area CriterionSteady State StabilityElectrical Power Transmission System and NetworkTransmission Line in Power SystemVoltage in Power Electric LinesShort Transmission LineMedium Transmission LineLong Transmission LinePerformance of Transmission LineABCD Parameters of Transmission LineSag in Overhead ConductorSurge Impedance Loading or SILAdmittanceAdvantages of Bundled ConductorsBundled Conductors Used in Transmission LineGround Clearance of Different Transmission LinesNew Articles System EarthingArc Suppression Coil or Petersen CoilWinding Resistance Test of Shunt ReactorMeasurement of Reactance of a Shunt ReactorTests of Shunt Reactor