Collecting Oil Sample from Oil Immersed Electrical Equipment
Causes of Insulating Oil Deterioration
Acidity Test of Transformer Insulating Oil
Ring CounterClosely Related Articles
Principle of DC Generator
Construction of DC Generator | Yoke Pole Armature Brushes of DC Generator
Characteristics of Series Wound DC Generator
Characteristic of Separately Excited DC Generator
EMF Equation of DC Generator
Parallel Operation of DC Generators
Self Excited DC Generators
Phasor Diagram for Synchronous Generator
DC Generators Performance Curves
Types of DC Generators
Characteristic of Shunt Wound DC Generator
Magnetization Curve of DC Generator
Applications of DC Generators
Alternator Synchronous Generator | Definition and Types of Alternator
Working Principle of Alternator
Construction of Alternator
Armature Reaction in Alternator or Synchronous Generator
Rating of Alternator
Derivation of Various Power Conditions in Alternators and Synchronous Motors
Induction Generator | Application of Induction Generator
Parallel Operation of Alternator
Motor Generator Set | M G Set
Types of Winding
Types of DC Generators
- Field coils excited by permanent magnets – Permanent magnet DC generators.
- Field coils excited by some external source – Separately excited DC generators.
- Field coils excited by the generator itself – Self excited DC generators.
Permanent Magnet DC GeneratorWhen the flux in the magnetic circuit is established by the help of permanent magnets then it is known as Permanent magnet DC generator.
It consists of an armature and one or several permanent magnets situated around the armature. This type of DC generators generates very low power. So, they are rarely found in industrial applications. They are normally used in small applications like dynamos in motor cycles.
Separately Excited DC GeneratorThese are the generators whose field magnets are energized by some external DC source such as battery. A circuit diagram of separately excited DC generator is shown in figure. Ia = Armature current IL = Load current V = Terminal voltage Eg = Generated emf Voltage drop in the armature = Ia × Ra (R/sub>a is the armature resistance) Let, Then, Power generated, Power delivered to the external load,
Self-excited DC GeneratorsThese are the generators whose field magnets are energized by the current supplied by themselves. In these type of machines field coils are internally connected with the armature. Due to residual magnetism some flux is always present in the poles. When the armature is rotated some emf is induced. Hence some induced current is produced. This small current flows through the field coil as well as the load and thereby strengthening the pole flux. As the pole flux strengthened, it will produce more armature emf, which cause further increase of current through the field. This increased field current further raises armature emf and this cumulative phenomenon continues until the excitation reaches to the rated value. According to the position of the field coils the self-excited DC generators may be classified as…
- Series wound generators
- Shunt wound generators
- Compound wound generators
Series Wound GeneratorIn these type of generators, the field windings are connected in series with armature conductors as shown in figure below. So, whole current flows through the field coils as well as the load. As series field winding carries full load current it is designed with relatively few turns of thick wire. The electrical resistance of series field winding is therefore very low (nearly 0.5Ω ). Let, Rsc = Series winding resistance Isc = Current flowing through the series field Ra = Armature resistance Ia = Armature current IL = Load current V = Terminal voltage Eg = Generated emf Then, Voltage across the load, Power generated, Power delivered to the load,
Shunt Wound DC GeneratorsIn these type of DC generators the field windings are connected in parallel with armature conductors as shown in figure below. In shunt wound generators the voltage in the field winding is same as the voltage across the terminal. Let, Rsh = Shunt winding resistance Ish = Current flowing through the shunt field Ra = Armature resistance Ia = Armature current IL = Load current V = Terminal voltage Eg = Generated emf Here armature current Ia is dividing in two parts, one is shunt field current Ish and another is load current IL. So, The effective power across the load will be maximum when IL will be maximum. So, it is required to keep shunt field current as small as possible. For this purpose the resistance of the shunt field winding generally kept high (100 Ω) and large no of turns are used for the desired emf. Shunt field current, Voltage across the load, Power generated, Power delivered to the load,
Compound Wound DC GeneratorIn series wound generators, the output voltage is directly proportional with load current. In shunt wound generators, output voltage is inversely proportional with load current. A combination of these two types of generators can overcome the disadvantages of both. This combination of windings is called compound wound DC generator. Compound wound generators have both series field winding and shunt field winding. One winding is placed in series with the armature and the other is placed in parallel with the armature. This type of DC generators may be of two types- short shunt compound wound generator and long shunt compound wound generator.
Short Shunt Compound Wound DC GeneratorThe generators in which only shunt field winding is in parallel with the armature winding as shown in figure. Series field current, Shunt field current, Armature current, Voltage across the load, Power generated, Power delivered to the load,
Long Shunt Compound Wound DC GeneratorThe generators in which shunt field winding is in parallel with both series field and armature winding as shown in figure. Shunt field current, Armature current, Ia = series field current, Voltage across the load, Power generated, Power delivered to the load, In a compound wound generator, the shunt field is stronger than the series field. When the series field assists the shunt field, generator is said to be commutatively compound wound. On the other hand if series field opposes the shunt field, the generator is said to be differentially compound wound.
Closely Related Articles Principle of DC GeneratorConstruction of DC Generator | Yoke Pole Armature Brushes of DC GeneratorCharacteristics of Series Wound DC GeneratorCharacteristic of Separately Excited DC GeneratorEMF Equation of DC GeneratorParallel Operation of DC GeneratorsSelf Excited DC GeneratorsHopkinson TestPhasor Diagram for Synchronous GeneratorDC Generators Performance CurvesCharacteristic of Shunt Wound DC GeneratorMagnetization Curve of DC GeneratorApplications of DC GeneratorsMore Related Articles Alternator Synchronous Generator | Definition and Types of AlternatorWorking Principle of AlternatorConstruction of AlternatorArmature Reaction in Alternator or Synchronous Generator Rating of AlternatorDerivation of Various Power Conditions in Alternators and Synchronous MotorsInduction Generator | Application of Induction GeneratorParallel Operation of AlternatorMotor Generator Set | M G SetArmature Winding | Pole Pitch Coil Span Commutator PitchWave WindingWinding Factor | Pitch Factor | Distribution FactorLap Winding Simplex and Duplex Lap WindingFrog Leg Winding | Drum Winding | Gramme Ring WindingArmature Winding of AlternatorNew Articles Collecting Oil Sample from Oil Immersed Electrical EquipmentCauses of Insulating Oil DeteriorationAcidity Test of Transformer Insulating OilMagnetic FluxRing Counter