Rotor Earth Fault Protection of Alternator or Generator
The rotor of an alternator is wound by field winding. Any single earth fault occurring on the field winding or in the exciter circuit is not a big problem for the machine. But if more than one earth fault occur, there may be a chance of short circuiting between the faulty points on the winding. This short circuited portion of the winding may cause unbalance magnetic field and subsequently mechanical damage may occur in the bearing of the machine due to unbalanced rotation. Hence it is always essential to detect the earth fault occurred on the rotor field winding circuit and to rectify it for normal operation of the machine. There are various methods available for detecting rotor earth fault of alternator or generator. But basic principle of all the methods is same and that is closing a relay circuit through the earth fault path.
There are mainly three types of rotor earth fault protection scheme used for this purpose.
- Potentiometer method
- AC injection method
- DC injection method
Potentiometer Method of Rotor Earth Fault Protection in AlternatorThe scheme is very simple. Here, one resistor of suitable value is connected across the field winding as well as across exciter. The resistor is centrally tapped and connected to the ground via a voltage sensitive relay.
You may also be interested on
As it is seen in the figure below, any earth fault in the field winding as well as exciter circuit closes the relay circuit through earthed path. At the same time the voltage appears across the relay due to potentiometer action of the resistor. This simple method of rotor earth fault protection of alternator has a big disadvantage. This arrangement can only sense the earth fault occurred in the any point except the center of the field winding.
From the circuit it is also clear that in the case of earth fault on the center of the field circuit will not cause any voltage to be appeared across the relay. That means simple potentiometer methods of rotor earth fault protection, is blind to the faults at the center of the field winding. This difficulty can be minimized by using another tap on the resistor somewhere else from the center of the resistor via a push button. If this push button is pressed, the center tap is shift and the voltage will appear across the relay even in the event of central arc fault occurs on the field winding.