# Measurement of Insulation Resistance

**insulation resistance**as the ratio of applied direct voltage across an insulation to the corresponding current through it.

NB: - The voltage, we apply for **measurement of insulation resistance**, is direct voltage. When we apply direct voltage across the insulation, a current starts passing through the insulation. This current has two main components.

- The current flowing through the leakage path over the surface of the solid insulator. This leakage path is formed mainly due to moisture, dust etc. which are naturally accumulated on the surface of the solid insulator.
- The current flowing through the volume of the insulator body.

- As the insulation materials are essentially dielectric in nature, there will be a capacitive charging current, appears just after application of test voltage. This current is instantaneous in nature. It will effectively disappear within few moments. Hence, this current does not have any effect on the reading of measurement if it is taken after 1 minute or more.
- There is another component of current called absorption current. It decays from high value to zero. The insulation resistance value taken within first few minutes of test is largely dominated by absorption current.
- Last but most important component of the current is conduction current. It remains steady throughout the
**insulation resistance test**. So after, charging current then absorption current becomes insignificant, the test result is mainly predominated by this conduction current.

## Method of Measuring Insulation Resistance

There are several instruments for measuring insulation resistance of an electrical equipment.- Direct-indicating ohmmeter with hand driven dc generator. This is locally known as hand driven megger since Megger is one of the best known manufacturer of this instrument.
- Direct-indicating ohmmeter with motor driven dc generator. This is locally known as motorized megger.
- Direct-indicating ohmmeter with self-contained battery.
- Direct-indicating ohmmeter with self-contained rectifier. This instrument takes power from an external AC supply.
- Resistance bridge circuit with self-contained galvanometer and battery.

**measurement of insulation resistance**with an external dc supply. In that case, we take voltage and current reading with the help of a dc voltmeter and a micro ranged dc ammeter, respectively.

In that case, we can calcula the insulation resistance with the help of ohm’s law Where V is the voltmeter reading and I is the ammeter reading.

The ammeter is micro ranged because, a very tiny current passes through the insulation during test and he current is in that range only. But at the moment of voltage application, the micrometer has to take initial capacitive charging current as well as absorption current. So the ammeter should be capable of withstanding both of these currents for at least initial duration. The voltmeter, ammeter and source should also be capable of withstanding short circuit current in the case of insulation failure if occurs during measurement.

When we use direct indicating ohmmeter of simply megger, the leads of the instrument are connected across the insulator to be tested. After driving the instrument the value of insulation resistance is indicated on the analog or digital dial of the instrument directly. In both of the above-mentioned methods of insulation resistance measurement, the reading is taken after a standard time delay to get more accurate and error-free reading.

Closely Related Articles Series and Parallel Inductors Electric PowerPhase Synchronizing Device or Controlled Switching DeviceElectric Current and Theory of Electricity | Heating and Magnetic EffectNature of ElectricityDrift Velocity Drift Current and Electron MobilityRMS or Root Mean Square Value of AC SignalMore Related Articles Working Principle of a CapacitorQuality Factor of Inductor and CapacitorTransient Behavior of CapacitorCylindrical CapacitorSpherical CapacitorCapacitors in Series and ParallelHow to Test Capacitors?Electrical Conductance Conductivity of Metal Semiconductor and Insulator | Band TheoryWhat is Electrical Resistance?Resistivity and Laws of ResistanceProperties of Electric ConductorTemperature Coefficient of ResistanceResistance Variation with TemperatureCircuit Elements - Active Passive Elements of Electrical CircuitElectrical DC Series and Parallel CircuitMagnetic FieldMagnetic FluxMagnetic PermeabilityHysteresis LoopMagnetic CircuitMagnetic SaturationEnergy Stored in a Magnetic FieldStatic Electric Field | Electrostatic Induction A Current Carrying Conductor within a Magnetic FieldMagnetic SusceptibilityHard Magnetic MaterialsSoft Magnetic MaterialsMagnetic Circuit with Air GapElectric ChargeCoulomb's Law | Explanation Statement Formulas Principle Limitation of Coulomb’s LawElectric Lines of ForceWhat is Electric Field?Electric Field Strength or Electric Field IntensityWhat is Flux? Types of Flux?Electric FluxElectric PotentialCapacitor and Capacitance | Types of CapacitorsEnergy Stored in CapacitorCharging a CapacitorDischarging a CapacitorFourier Series and Fourier TransformTrigonometric Fourier SeriesAnalysis of Exponential Fourier SeriesParity GeneratorDual NetworkTime ConstantElectric Circuit or Electrical NetworkSeries Parallel Battery CellsRL Series CircuitWhat is Inductor and Inductance | Theory of InductorRLC CircuitThree Phase Circuit | Star and Delta SystemRL Parallel CircuitRL Circuit Transfer Function Time Constant RL Circuit as FilterConstruction of AC Circuits and Working of AC CircuitsSeries RLC CircuitParallel RLC CircuitResonance in Series RLC CircuitPlanar and Non Planar Graphs of CircuitClipping CircuitMutual InductanceSelf InductanceSI System of UnitsElectrical International SymbolElectric Power Single and Three Phase Power Active Reactive ApparentVector Algebra | Vector DiagramRelationship of Line and Phase Voltages and Currents in a Star Connected SystemVector Diagram | Three Phase Vector DiagramTypes of Resistor Carbon Composition and Wire Wound ResistorVaristor Metal Oxide Varistor is Nonlinear ResistorCarbon Composition ResistorWire Wound ResistorVariable Resistors | Defination, Uses and Types of Variable ResistorsLight Dependent Resistor | LDR and Working Principle of LDRVoltage SourceIdeal Dependent Independent Voltage Current SourceVoltage or Electric Potential DifferenceVoltage Drop CalculationVoltage DividerVoltage MultiplierVoltage DoublerVoltage RegulatorVoltage FollowerVoltage Regulator 7805Voltage to Current ConverterNew Articles Series and Parallel Inductors Electric PowerMeasurement of Losses in Shunt ReactorThree Phase Shunt ReactorMeasurement of Insulation ResistanceAmpere's Circuital Law