High Voltage Direct Current Transmission | HVDC Transmission
The massive transmission of electricity in the form of DC over lengthy distances by means of submarine cables or overhead transmission line is the high voltage direct current transmission. This type of transmission is preferred over HVAC transmission for very long distance when considering the cost, losses and many other factors. The names Electrical super highway or Power super highway are often used for HVDC.
HVDC Transmission SystemWe know that AC power is generated in the generating station. This should first be converted into DC. The conversion is done with the help of rectifier. The DC power will flow through the overhead lines. At the user end, this DC has to be converted into AC. For that purpose, an inverter is placed at the receiving end.
Thus, there will be a rectifier terminal in one end of HVDC substation and an inverter terminal in the other end. The power of the sending end and user end will be always equal (Input Power = Output Power).
You may also be interested on
When there are two converter stations at both ends and a single transmission line is termed as two terminal DC systems. When there are two or more converter stations and DC transmission lines is termed as multi terminal DC substation. The components of the HVDC Transmission system and its function are explained below. Converters: The AC to DC and DC to AC conversion are done by the converters. It includes transformers and valve bridges. Smoothing Reactors: Each pole consist of smoothing reactors which are of inductors connected in series with the pole. It is used to avoid commutation failures occurring in inverters, reduces harmonics and avoids discontinuation of current for loads. Electrodes: They are actually conductors which are used to connect the system to the earth. Harmonic Filters: It is used to minimise the harmonics in voltage and current of the converters used.
DC Lines: It can be cables or overhead lines. Reactive Power Supplies: The reactive power used by the converters could be more than 50% of the total transferred active power. So the shunt capacitors provide this reactive power. AC Circuit Breakers: The fault in the transformer is cleared by the circuit breakers. It also used to disconnect the DC link.
HVDC System ConfigurationsThe classification of HVDC links are as follows:
Mono Polar LinksSingle conductor is required and water or ground act as the return path. If the earth resistivity is high, metallic return is used.
Bipolar LinksDouble converters of same voltage rating are used in each terminal. The converter junctions are grounded.
Homo Polar LinksIt consists of more than two conductors which is having equal polarity generally negative. Ground is the return path.
Multi Terminal LinksIt is used to connect more than two points and is rarely used.
Comparison of both HVAC and HVDC Transmission System
|HVDC Transmission System||HVAC Transmission System|
|Low losses.||Losses are high due to skin effect and corona.|
|Better Voltage regulation and Control ability.||Voltage regulation and Control ability is low.|
|Transmit more power over longer distance.||Transmit less power compared to HVDC system.|
|Less insulation is needed.||More insulation is required.|
|Reliability is high.||Low Reliability.|
|Asynchronous interconnection is possible.||Asynchronous interconnection is not possible.|
|Reduced line cost due to fewer conductors.||Line cost is high.|
|Towers are cheaper, simple and narrow.||Towers are bigger compared to HVDC.|
Disadvantages of HVDC Transmission
- Converters with small overload capacity are used.
- Circuit Breakers, Converters and AC filters are expensive especially for small distance transmission.
- No transformers for altering the voltage level.
- HVDC link is extremely complicated.
- Uncontrollable power flow.
Application of HVDC Transmission
- Undersea and underground cables
- AC network interconnections
- Interconnecting Asynchronous system
|A||AMITAVA NANDI commented on 08/06/2018|
More details about HVDC was expected.
|E||ER KUMAR LALIT commented on 24/04/2018|
I like the way about to explanation. Very useful for basic and provide the way to go in depth.
|I||IYONAGBE GODWIN ITAMAH commented on 09/04/2018|
Very efficient and useful information about HVDC.
|M||MUTHU PRIYA commented on 30/03/2018|
Very useful information.