Basic Construction of Wind Turbine
Characteristics of SensorsClosely Related Articles
Solar Energy System | History of Solar Energy
Types of Solar Power Station
Components of a Solar Electric Generating System
What is photovoltaic effect?
Staebler Wronski Effect
Working Principle of Photovoltaic Cell or Solar Cell
Characteristics of a Solar Cell and Parameters of a Solar Cell
Solar Cell Manufacturing Technology
What is a Solar PV Module?
What is Standalone Solar Electric System?
Steam Boiler | Working principle and Types of Boiler
Methods of Firing Steam Boiler
Fire Tube Boiler | Operation and Types of Fire Tube Boiler
Water Tube Boiler | Operation and Types of Water Tube Boiler
Steam Boiler Furnace Grate Firebox Combustion Chamber of Furnace
Feed Water and Steam Circuit of Boiler
Boiler Feed Water Treatment Demineralization Reverse Osmosis Plant Deaerator
Coal Combustion Theory
Fluidized Bed Combustion | Types and Advantages of Fluidized Bed Combustion
Steam Condenser of Turbine
Jet Condenser | Low Level High Level Ejector Jet Condenser
Surface Steam Condenser
Economics of Power Generation
Cooling Tower Useful Terms and Cooling Tower Performance
Cooling Tower Material and Main Components
Power Plant Fire Protection System
Hydrant System for Power Plant Fire Protection
Medium Velocity Water Spray or MVWS System for Fire Protection
Foam Fire Protection System
Fire Detection and Alarm System
Gas Extinguishing System
Electric Power Generation
Power Plants and Types of Power Plant
Thermal Power Generation Plant or Thermal Power Station
Hydro Power Plant | Construction Working and History of Hydro power plant
Nuclear Power Station or Nuclear Power Plant
Diesel Power Station
Why Supply Frequency is 50 Hz or 60 Hz?
Economiser in Thermal Power Plant | Economiser
MHD Generation or Magneto Hydro Dynamic Power Generation
Cogeneration | Combined Heat and Power
Thermoelectric Power Generators or Seebeck Power Generation
Cost of Electrical Energy
Gas Turbine Power Plant
Steam Dryness Fraction
Superheated Steam and Steam Phase Diagram
Vapour Properties Mollier Chart Heat Capacities
What is Steam Flashing?
How to Calculate Steam Consumption During Plant Start Up
Effective Steam Distribution System
What is Water Hammer?
Engineering Thermodynamics Part 1
Science of Engineering Thermodynamics Part 2
Basic Law of Conservation and First Law of Thermodynamics
Carnot Cycle and Reversed Carnot Cycle
Enthalpy Entropy and Second Law of Thermodynamics
Rankine Cycle and Regenerative Feed Heating
Rankine Cycle for Closed Feed Water Heaters and Rankine Cycle Cogeneration
Ideal Verses Actual Rankine Cycle
Rankine Cycle Efficiency Improvement Techniques
Wind Energy Electricity Generation
Theory of Wind Turbine
Wind Turbine | Working and Types of Wind Turbine
Basic Construction of Wind Turbine
What is a Solar PV Module?
In a solar module the solar cells are connected in same fashion as the battery cell units in a battery bank system. That means positive terminals of one cell connected to negative terminal voltage of solar module is simple sum of the voltage of individual cells connected in series in the module. The normal output voltage of a solar cell is approximately 0.5 V hence if 6 such cells are connected in series then the output voltage of the cell would be 0.5 × 6 = 3 Volt.
Ratings of Solar ModuleThe output from a solar module depends upon some conditions such as ambient temperature and intensity of incidence light. Hence the rating of a solar module must be specified under such conditions. It is standardized practice to express rating of PV or solar module at 25oC temperature and 1000 w/m2 light radiation. The solar modules are rated with their output open circuit voltage (Voc), short circuit current (Isc) and peak power (Wp). That means these three parameters (Voc, Isc and Wp) can be delivered by a solar module safely at 25oC and 1000 w/m2 solar radiations. These conditions i.e. 25oC temperature and 1000 w/m2 solar radiations are collectively called Standard Test Conditions. The Standard Test Conditions may not be available at site where the solar modules to be installed. This is because the solar radiations and temperature vary with location and time.
V-I Characteristic of Solar ModuleIf we draw a graph by taking X-axis as voltage axis and Y-axis as currents of a solar module, then the graph will represent V-I characteristic of a solar module.
Short Circuit Current of PV ModuleUnder Standard Test Condition positive and negative terminal of a solar module are short circuited, then the current delivered by the module is short circuit current. Bigger value of this current indicates betterness of the module. Although under standard test condition, this current also depends upon the area of the module exposed to the light. As it depends upon area, it is better to express by short circuit current per unit area. This is deneted as Jsc. Hence, Where, A is the area of the module exposed to the standard light radiation (1000w/m2). Short circuit current of a pv module also depends upon solar cell manufacturing technology.
Open Circuit Voltage (Voc)The voltage output of a solar module under standard test condition, when the terminals of the modules are not connected with any load. This rating of solar module mainly depends upon the technology used to manufacture solar cells of the module. More Voc indicates betterness of the solar module. This open circuit voltage of a solar module also depends upon operating temperature.
Maximum Power PointThis is the maximum amount of power which can deliver by the module Under Standard Test Conditions. For a fixed dimension of a module higher the maximum power better the module. Maximum power also called peak power and this is denoted as Wm or Wp. A solar module can be operated in any voltage and current combination upto Voc and Isc. But for a particular current and voltage combination under standard conditions the output power is maximum. If we proceed through y-axis of the V-I characteristic of a solar module, we will find the power output increases nearly linearly with current but after a certain current power output will fall down as it approaches to the short circuit current as at short circuit condition the voltage is considered to be ideally zero across the terminals of the solar module. So it is clear that maximum output power of a solar module does not occur at maximum current i.e. short circuit current instead it occurs at certain current which is less than short circuit current (Isc). This current at which maximum output power occurs is denoted as Im. Similarly maximum power of a solar cell does not occur at open circuit voltage as it is open circuit condition and current through the cell is considered to be ideally zero, at this condition. But similarly as previous case, maximum power in a solar module occurs at a voltage lower than open circuit voltage (Voc). The voltage at which maximum power output occurs is denoted as Vm. The maximum power of a solar module is given as The current and voltage at which maximum power occurs are referred as, current and voltage at maximum power point respectively.
Fill Factor of a Solar ModuleFill factor of a solar module is defined as the ratio of maximum power (Pm = Vm x Im) to product of open circuit voltage (Voc) and short circuit current (Isc). Higher the Fill Factor(FF), better is the solar module.
Efficiency of Solar ModuleEfficiency of solar module is defined as the ratio of maximum power at standard test condition, to the input power. Input power of a solar module is solar radiation which is considered as 1000 w/m2. So, actual input power to the cell is 1000A W. Where, A is the exposed area of the solar module. Therefore, efficiency,
Number of Cells in ModuleNumber of cells in a module depends upon the standard voltage requirement per module. In 1980’s solar modules were mainly manufactured for charging 12 Volt batteries. But for charging a 12 Volt battery it is required to have sufficiently higher output voltage of the module than 12 Volt. It was standard practice to design a solar module with maximum voltage rating (Vm) of 15 Volt. This module of 15 Volt becomes standard module from those days. The number of solar cells to be connected in series to achieve standard voltage output depends upon the open-circuit voltage (Voc) of the individual cells. The Voc of a solar cell depends upon mainly its manufacturing techniques. The table below shows the open-circuit voltage of different solar cells at standard test conditions.
|Solar Cell Types||Open Circuit Voltage at STC|
|Mono Crystalline Silicon Solar Cell||0.55 to 0.68 V|
|Poly Crystalline Silicon Solar Cell||0.55 to 0.65 V|
|Amorphous Silicon Solar Cell||0.7 to 1.1 V|
|Cadmium Telluride Solar Cell||0.8 to 1.0 V|
|Copper Indium Gallium Selenide Solar Cell||0.5 to 0.7 V|
|Gallium Indium Phosphide/ Gallium Arsenide / Gallium Solar Cell||1 to 2.5 V|