Power System Stabilityon 24/2/2012 & Updated on Monday 30th of April 2018 at 06:33:49 PM
Even the most effective way to produce a bulk amount of power has been with the evolution of AC machine (i.e., synchronous generator). In the power plants, several synchronous generators with different voltage ratings are connected to the bus terminals having the same frequency and phase sequence as the generators, while the consumer ends are connected directly from those bus terminals. Therefore, for a stable operation, we have to synchronize the bus with the generators over the entire duration of the transmission. For this reason the power system stability is also referred to as synchronous stability and is defined as the ability of the system to return to synchronism after having undergone some disturbance due to switching on and off of load or due to line transience. To understand, stability well, another factor needs to consider, and that is the stability limit of the system. The stability limit defines the maximum power permissible to flow through a particular point or a part of the system for which it is subjected to line disturbances or faulty flow of power. Having understood these terminologies related to power system stability let us now look into the different types of stability.
The synchronous stability of a power system can be of several types depending upon the nature of the disturbance, and for successful analysis, it can be classified into the following three types as shown below:
Steady State Stability of a Power SystemThe steady-state stability of a power system is defined as the ability of the system to bring itself back to its stable configuration following a small disturbance in the network (like normal load fluctuation or action of automatic voltage regulator). It can only be considered only during a very gradual and infinitesimally small power change.
In case the power flow through the circuit exceeds the maximum power permissible, then there are chances that a particular machine or a group of machines will cease to operate in synchronism, and result in yet more disturbances. In such a situation, the steady-state limit of the system is said to have reached, or in other words, the steady state stability limit of a system refers to the maximum amount of power that is permissible through the system without loss of its steady state stability.
Transient Stability of a Power SystemTransient stability of a power system refers to the ability of the system to reach a stable condition following a large disturbance in the network condition. In all cases related to large changes in the system like sudden application or removal of the load, switching operations, line faults or loss due to excitation the transient stability of the system comes into play. It in fact deals in the ability of the system to retain synchronism following a disturbance sustaining for a reasonably long period. And the maximum power that is permissible to flow through the network without loss of stability following a sustained period of disturbance is referred to as the transient stability of the system. Going beyond that maximum permissible value for power flow, the system would temporarily be rendered as unstable.
Dynamic Stability of a Power SystemDynamic stability of a system denotes the artificial stability given to an inherently unstable system by automatically controlled means. It is concerned to small disturbances lasting for about 10 to 30 seconds.
Rating = 5 & Total votes = 6