Principle of Water Content Test of Insulating Oil
Collecting Oil Sample from Oil Immersed Electrical Equipment
Causes of Insulating Oil Deterioration
Acidity Test of Transformer Insulating Oil
Magnetic FieldClosely Related Articles
Power Plant Fire Protection System
Hydrant System for Power Plant Fire Protection
Medium Velocity Water Spray or MVWS System for Fire Protection
Foam Fire Protection System
Fire Detection and Alarm System
Gas Extinguishing System
Steam Boiler | Working principle and Types of Boiler
Methods of Firing Steam Boiler
Fire Tube Boiler | Operation and Types of Fire Tube Boiler
Water Tube Boiler | Operation and Types of Water Tube Boiler
Steam Boiler Furnace Grate Firebox Combustion Chamber of Furnace
Feed Water and Steam Circuit of Boiler
Boiler Feed Water Treatment Demineralization Reverse Osmosis Plant Deaerator
Coal Combustion Theory
Fluidized Bed Combustion | Types and Advantages of Fluidized Bed Combustion
Steam Condenser of Turbine
Jet Condenser | Low Level High Level Ejector Jet Condenser
Surface Steam Condenser
Economics of Power Generation
Cooling Tower Useful Terms and Cooling Tower Performance
Cooling Tower Material and Main Components
Electric Power Generation
Power Plants and Types of Power Plant
Thermal Power Generation Plant or Thermal Power Station
Hydro Power Plant | Construction Working and History of Hydro power plant
Nuclear Power Station or Nuclear Power Plant
Diesel Power Station
Why Supply Frequency is 50 Hz or 60 Hz?
Economiser in Thermal Power Plant | Economiser
MHD Generation or Magneto Hydro Dynamic Power Generation
Cogeneration | Combined Heat and Power
Thermoelectric Power Generators or Seebeck Power Generation
Cost of Electrical Energy
Gas Turbine Power Plant
Solar Energy System
Types of Solar Power Station
Components of a Solar Electric Generating System
Staebler Wronski Effect
Principle of Photovoltaic Cell
Characteristics of Solar Cell
Solar Cell Manufacturing Technology
Solar PV Module
Standalone Solar Electric System
Steam Dryness Fraction
Superheated Steam and Steam Phase Diagram
Vapour Properties Mollier Chart Heat Capacities
How to Calculate Steam Consumption During Plant Start Up
Effective Steam Distribution System
Engineering Thermodynamics Part 1
Engineering Thermodynamics Part 2
First Law of Thermodynamics
Enthalpy Entropy and Second Law of Thermodynamics
Rankine Cycle and Regenerative Feed Heating
Rankine Cycle for Closed Feed Water Heaters and Rankine Cycle Cogeneration
Ideal Verses Actual Rankine Cycle
Rankine Cycle Efficiency Improvement Techniques
Wind Energy Electricity Generation
Theory of Wind Turbine
Basic Construction of Wind Turbine
Power Plant Fire Protection System
Thermal Power Plants are characterized by their complex overall system made of a range of different operating modules. In addition to these conditions such as extremely hot surfaces, lubricating oils and coal and coal dust pose huge fire risks. Elements of Fire Protection System is covered in this Portion of Part-I. This section comprises of following which broadly are the elements of the fire protection system:
Fire Water Reservoir or Fire water Pump HouseWater pump house plays an important role in fire protection system, so the complete fire pump arrangement shall be in line with the requirements of TAC. Water storage tank is required for storage of water and water will be drawn as and when required for fire protection. All the fire pumps should work automatically by use of Pressure switches; however stopping of all the fire pumps shall be manual only. The possible sources of supply of water to storage tank will be from two different sources:
- From raw water pump discharge header.
- From CW blow down the system.
The fire water storage tank shall be provided with two equal compartments and both the compartments shall be interconnected through separate isolation valve and each compartment shall be connected to a common suction header of fire water pumps so that any fire pump can be fed by either fire water storage compartment as per TAC regulations. At least two (2) headers shall be taken out of pump house for making loops around various risks. Each loop shall be interconnected for better reliability of the system. To isolate the system due to damage/repair, suitable nos. of gate valve should be provided.
Pumps Installed in Fire Water Pump HouseDedicated fire water pumps shall be provided for the fire hydrant and spray system. Blind flange with valve connection for future expansion shall be provided in the fire hydrant and spray system network. The installed fire water pump capacity and head shall be designed as per system requirement/TAC recommendations.
Following are the fire water pumps installed in the fire water pump house:
- Electric motor driven main fire water pump.
- Diesel engine driven pumps
- All diesel engine driven pumps shall be provided with 2 × 100% battery chargers and batteries.
- Electric motor driven fire water jockey pumps (one working and one stand by).
- Air compressor for pressurizing hydro-pneumatic tank.
Fire Water Pumps Data SheetFor selection of rated capacity, rpm and material construction are:
|S.No.||Description||Electric Motor driven pump||Diesel engine driven pump||Jockey pump||1.0||General Information||1.1||Rated Capacity/Nos||Contractor to decide (minimum 3 nos.) for hydrant cum MVWS system and minimum 1 no for HVWS system||Contractor to decide (minimum 2 nos. for hydrant cum MVWS system and minimum 1 no for HVWS system)||Contractor to decide||1.2||Rated speed (rpm)||1500||1500||2900||1.3||Total head at the pump discharge MWC||As per system requirement||As per system requirement||As per system requirement||1.4||TAC approval required||yes||yes||yes||1.5||Used for service like||Hydrant and spray system||Hydrant and spray system||Common for Hydrant and spray system||2.0||Material of construction||2.1||Casing||SS304||SS304||SS304||2.2||Impeller||Stainless steel||Stainless steel||Stainless steel||2.3||Shaft||Stainless steel||Stainless steel||Stainless steel|
Control and operating philosophyFire water ring main network shall be a pressurized system provided with automatic starting of fire water pumps. The mode of operation of fire water pumping system for following shall be described in Part-II and III.
- Hydrant and MVWSS
- Hydrant and HVWSS
- Fixed Foam system
- Fire water booster pump
- All hydrant, spray and foam system pipe mains/pipes shall be routed above ground on top of the concrete pedestals at regular intervals.
- In main plant area and coal stock yard area pipe lines shall be routed in RCC pipe trenches filled with sand and covered with pre-cast RCC removable covers. Pipe trenches crossing through road or rail shall be through Hume pipes.
- Fire water pipes shall be of carbon steel conforming to IS:1239 (medium grade) and IS:3589.
- All above ground piping shall be adequately supported by concrete pedestals at regular intervals.
- All buried pipes shall be double coated and wrapped as per IS:10221 or IS:15337.
- The entire pipe net work shall be hydraulically designed in such manner that the velocity of water in any section does not exceed 5.0 m/sec.
- Fire pump pressure has to be decided in such a manner that the requirement of the highest pressure at the remotest and highest hydrant can be meet at the same time in line with the TAC requirements.
- Hose cabinet shall be provided with 16 SWG thick body and 3 mm glass. The hose shall be provided with key box and pedestal. Fire hose shall be of IS 636 type-A.
Hydrant System(is covered in part-II)
Spray System(is covered in part-II)
Fix Foam system(is covered in part-III)
Potable and mobile extinguisher(is covered in part-III)
Closely Related Articles Hydrant System for Power Plant Fire ProtectionMedium Velocity Water Spray or MVWS System for Fire ProtectionFoam Fire Protection SystemFire Detection and Alarm SystemGas Extinguishing SystemMore Related Articles Steam Boiler | Working principle and Types of BoilerMethods of Firing Steam BoilerFire Tube Boiler | Operation and Types of Fire Tube BoilerWater Tube Boiler | Operation and Types of Water Tube BoilerSteam Boiler Furnace Grate Firebox Combustion Chamber of FurnaceFeed Water and Steam Circuit of BoilerBoiler Feed Water Treatment Demineralization Reverse Osmosis Plant DeaeratorCoal Combustion TheoryFluidized Bed Combustion | Types and Advantages of Fluidized Bed CombustionSteam Condenser of TurbineJet Condenser | Low Level High Level Ejector Jet CondenserSurface Steam Condenser Economics of Power GenerationCooling Tower Useful Terms and Cooling Tower PerformanceCooling Tower Material and Main ComponentsElectric Power GenerationPower Plants and Types of Power PlantThermal Power Generation Plant or Thermal Power StationHydro Power Plant | Construction Working and History of Hydro power plantNuclear Power Station or Nuclear Power PlantDiesel Power StationWhy Supply Frequency is 50 Hz or 60 Hz?Economiser in Thermal Power Plant | EconomiserMHD Generation or Magneto Hydro Dynamic Power Generation Cogeneration | Combined Heat and PowerThermoelectric Power Generators or Seebeck Power GenerationCost of Electrical EnergyGas Turbine Power PlantNuclear ReactorSolar ElectricitySolar Energy System | History of Solar EnergyTypes of Solar Power StationComponents of a Solar Electric Generating SystemWhat is Photovoltaic Effect?Staebler Wronski EffectWorking Principle of Photovoltaic Cell or Solar CellSolar CellCharacteristics of a Solar Cell and Parameters of a Solar CellSolar Cell Manufacturing TechnologyWhat is a Solar PV Module?What is Standalone Solar Electric System?Solar LanternSteamSteam Dryness FractionSuperheated Steam and Steam Phase DiagramVapour Properties Mollier Chart Heat CapacitiesWhat is Steam Flashing?How to Calculate Steam Consumption During Plant Start Up Effective Steam Distribution SystemWhat is Water Hammer?Engineering Thermodynamics Part 1Science of Engineering Thermodynamics Part 2Basic Law of Conservation and First Law of Thermodynamics Carnot Cycle and Reversed Carnot CycleEnthalpy Entropy and Second Law of ThermodynamicsRankine CycleRankine Cycle and Regenerative Feed HeatingRankine Cycle for Closed Feed Water Heaters and Rankine Cycle CogenerationIdeal Verses Actual Rankine CycleRankine Cycle Efficiency Improvement TechniquesWind Energy Electricity GenerationTheory of Wind Turbine Wind Turbine | Working and Types of Wind TurbineBasic Construction of Wind TurbineNew Articles Principle of Water Content Test of Insulating OilCollecting Oil Sample from Oil Immersed Electrical EquipmentCauses of Insulating Oil DeteriorationAcidity Test of Transformer Insulating OilMagnetic Flux