Ampere's Circuital Law
Mechanical Equivalent of Heat
Trees and Cotrees
PSD or CSDClosely Related Articles
Thermal Power Plant
Hydro Power Plant
Nuclear Power Station
Diesel Power Station
Seebeck Power Generation
Cost of Electrical Energy
Gas Turbine Power Plant
Methods of Firing Steam Boiler
Fire Tube Boiler
Water Tube Boiler
Steam Boiler Function
Feed Circuit of Boiler
Boiler Feed Water Treatment
Coal Combustion Theory
Fluidized Bed Combustion
Condenser of Turbine
Surface Steam Condenser
Economics of Power Generation
Cooling Tower Performance
Components of Cooling Tower
Power Plant Fire Protection System
MVWS Fire Protection
Foam Fire Protection System
Fire Detection System
Gas Extinguishing System
Solar Energy System
Types of Solar plant
Components of a Solar Generating System
Staebler Wronski Effect
Principle of Photovoltaic Cell
Characteristics of Solar Cell
Solar PV Module
Standalone Solar Electric System
Steam Dryness Fraction
Properties of Vapour
How to Calculate Steam Consumption During Plant Start Up
Steam Distribution System
Engineering Thermodynamics Part 2
First Law of Thermodynamics
Rankine Cycle and Regenerative Feed Heating
Rankine Cycle Cogeneration
Ideal Verses Actual Rankine Cycle
Wind Energy Generation
Theory of Wind Turbine
MHD Generation or Magneto Hydro Dynamic Power Generation
History of MHD GenerationThe concept of MHD power generation was introduced for the very first time by Michael Faraday in the year 1832 in his Bakerian lecture to the Royal Society. He in fact carried out an experiment at the Waterloo Bridge in Great Britain for measuring the current, from the flow of the river Thames in earth's magnetic field.
This experiment in a way outlined the basic concept behind MHD generation over the years then, several research work had been conducted on this topic, and later in August 13, 1940 this concept of magneto hydro dynamic power generation, was imbibed as the most widely accepted process for the conversion of heat energy directly into electrical energy without a mechanical sub-link.
Principle of MHD GenerationThe principal of MHD power generation is very simple and is based on Faraday’s law of electromagnetic induction, which states that when a conductor and a magnetic field moves relative to each other, then voltage is induced in the conductor, which results in flow of current across the terminals. As the name implies,the magneto hydro dynamics generator shown in the figure below, is concerned with the flow of a conducting fluid in the presence of magnetic and electric fields. In conventional generator or alternator, the conductor consists of copper windings or stripswhile in an MHD generator the hot ionized gas or conducting fluid replaces the solid conductor. A pressurized, electrically conducting fluid flows through a transverse magnetic field in a channel or duct. Pair of electrodes are located on the channel walls at right angle to the magnetic field and connected through an external circuit to deliver power to a load connected to it. Electrodes in the MHD generator perform the same function as brushes in a conventional DC generator. The MHD generator develops DC power and the conversion to AC is done using an inverter.
The power generated per unit length by MHD generator is approximately given by, Where, u is the fluid velocity, B is the magnetic flux density, σ is the electrical conductivity of conducting fluid and P is the density of fluid. It is evident from the equation above, that for the higher power density of an MHD generator there must be a strong magnetic field of 4-5 tesla and high flow velocity of conducting fluid besides adequate conductivity.
MHD Cycles and Working FluidsThe MHD cycles can be of two types, namely
- Open Cycle MHD.
- Closed Cycle MHD.
Open Cycle MHD SystemIn open cycle MHD system, atmospheric air at very high temperature and pressure is passed through the strong magnetic field. Coal is first processed and burnet in the combustor at a high temperature of about 2700oC and pressure about 12 ATP with pre-heated air from the plasma. Then a seeding material such as potassium carbonate is injected to the plasma to increase the electrical conductivity. The resulting mixture having an electrical conductivity of about 10 Siemens/m is expanded through a nozzle, so as to have a high velocity and then passed through the magnetic field of MHD generator. During the expansion of the gas at high temperature, the positive and negative ions move to the electrodes and thus constitute an electric current. The gas is then made to exhaust through the generator. Since the same air cannot be reused again hence it forms an open cycle and thus is named as open cycle MHD.
Closed Cycle MHD SystemAs the name suggests the working fluid in a closed cycle MHD is circulated in a closed loop. Hence, in this case inert gas or liquid metal is used as the working fluid to transfer the heat. The liquid metal has typically the advantage of high electrical conductivity, hence the heat provided by the combustion material need not be too high. Contrary to the open loop system there is no inlet and outlet for the atmospheric air. Hence, the process is simplified to a great extent, as the same fluid is circulated time and again for effective heat transfer.
Advantages of MHD GenerationThe advantages of MHD generation over the other conventional methods of generation are given below.
- Here only working fluid is circulated, and there are no moving mechanical parts. This reduces the mechanical losses to nil and makes the operation more dependable.
- The temperature of working fluid is maintained by the walls of MHD.
- It has the ability to reach full power level almost directly.
- The price of MHD generators is much lower than conventional generators.
- MHD has very high efficiency, which is higher than most of the other conventional or non-conventional method of generation.
Closely Related Articles Electric Power GenerationPower Plants and Types of Power PlantThermal Power Generation Plant or Thermal Power StationHydro Power Plant | Construction Working and History of Hydro power plantNuclear Power Station or Nuclear Power PlantDiesel Power StationWhy Supply Frequency is 50 Hz or 60 Hz?Economiser in Thermal Power Plant | EconomiserCogeneration | Combined Heat and PowerThermoelectric Power Generators or Seebeck Power GenerationCost of Electrical EnergyGas Turbine Power PlantNuclear ReactorMore Related Articles Steam Boiler | Working principle and Types of BoilerMethods of Firing Steam BoilerFire Tube Boiler | Operation and Types of Fire Tube BoilerWater Tube Boiler | Operation and Types of Water Tube BoilerSteam Boiler Furnace Grate Firebox Combustion Chamber of FurnaceFeed Water and Steam Circuit of BoilerBoiler Feed Water Treatment Demineralization Reverse Osmosis Plant DeaeratorCoal Combustion TheoryFluidized Bed Combustion | Types and Advantages of Fluidized Bed CombustionSteam Condenser of TurbineJet Condenser | Low Level High Level Ejector Jet CondenserSurface Steam Condenser Economics of Power GenerationCooling Tower Useful Terms and Cooling Tower PerformanceCooling Tower Material and Main ComponentsPower Plant Fire Protection SystemHydrant System for Power Plant Fire ProtectionMedium Velocity Water Spray or MVWS System for Fire ProtectionFoam Fire Protection SystemFire Detection and Alarm SystemGas Extinguishing SystemSolar ElectricitySolar Energy System | History of Solar EnergyTypes of Solar Power StationComponents of a Solar Electric Generating SystemWhat is Photovoltaic Effect?Staebler Wronski EffectWorking Principle of Photovoltaic Cell or Solar CellSolar CellCharacteristics of a Solar Cell and Parameters of a Solar CellSolar Cell Manufacturing TechnologyWhat is a Solar PV Module?What is Standalone Solar Electric System?Solar LanternSteamSteam Dryness FractionSuperheated Steam and Steam Phase DiagramVapour Properties Mollier Chart Heat CapacitiesWhat is Steam Flashing?How to Calculate Steam Consumption During Plant Start Up Effective Steam Distribution SystemWhat is Water Hammer?Engineering Thermodynamics Part 1Science of Engineering Thermodynamics Part 2Basic Law of Conservation and First Law of Thermodynamics Carnot Cycle and Reversed Carnot CycleEnthalpy Entropy and Second Law of ThermodynamicsRankine CycleRankine Cycle and Regenerative Feed HeatingRankine Cycle for Closed Feed Water Heaters and Rankine Cycle CogenerationIdeal Verses Actual Rankine CycleRankine Cycle Efficiency Improvement TechniquesWind Energy Electricity GenerationTheory of Wind Turbine Wind Turbine | Working and Types of Wind TurbineBasic Construction of Wind TurbineNew Articles Ampere's Circuital LawMechanical Equivalent of HeatTrees and Cotrees of Electric NetworkDifferentiatorIntegratorPhase Synchronizing Device or Controlled Switching Device