# Load Flow or Power Flow Analysis

Published on 24/2/2012 & updated on Monday 30th of April 2018 at 06:30:06 PMHOME / TRANSMISSION / TRANSMISSION EFFECT

Things you must know about load flow:

**Load flow**study is the steady state analysis of power system network.- Load flow study determines the operating state of the system for a given loading.
- Load flow solves a set of simultaneous non linear algebraic power equations for the two unknown variables (|V| and ∠δ ) at each node in a system.
- To solve non linear algebraic equations it is important to have fast, efficient and accurate numerical algorithms.
- The output of the load flow analysis is the voltage and phase angle, real and reactive power (both sides in each line), line losses and slack bus power.

__Related pages__

## Load Flow Steps

The study of load flow involves the following three steps:- Modeling of power system components and network.
- Development of load flow equations.
- Solving the
**load flow**equations using numerical techniques.

### Modeling of Power System Components

GeneratorLoad Transmission Line A Transmission line is represented as a nominal π model. Where, R + jX is the line impedance and Y/2 is called the half line charging admittance.

Off Nominal Tap Changing Transformer For a nominal transformer the relation But for an off nominal transformer Thus for an off nominal transformer we define the transformation ratio (a) as follows Now we would like to represent an off nominal transformer in a line by an equivalent model. Fig 2: Line Containing an Off Nominal Transformer We want to convert the above into an equivalent π model between bus p and q. Fig 3: Equivalent π Model of Line

Our aim is to find these values of admittances Y_{1}, Y_{2} and Y_{3} so that fig2 can be represented by fig 3
From Fig 2 we have,
Now consider Fig 3, from fig3 we have,
From eqn I and III on comparing the coefficients of E_{p} and E_{q} we get,
Similarly from equation II and IV we have
Some useful observations
From above analysis we see that Y_{2}, Y_{3} values can either be positive or negative depending on the value of transformation ratio.
Good question!
Y = - ve implies absorption of reactive power i.e it is behaving as an inductor.
Y = + ve implies generation of reactive power i.e it is behaving as a capacitor.
Modeling of a Network
Consider the two bus system as shown in figure above.
We have already seen that
Power generated at bus i is
Power demand at bus i is
Therefore we define the net power injected at bus i as follows

**Please Rate this Article**