Insulation Dielectric Test of TransformerPublished on 24/2/2012 and last updated on Thursday 3rd of May 2018 at 04:56:50 PM
The dielectric test of transformer is generally performed in two different steps, likewise, separate source voltage withstand test and induced voltage withstand test of transformer, which we have discussed one by one below.Please Rate this Article
Separate Source Voltage Withstand Test of TransformerThis dielectric test is intended to check the the ability of main insulation to earth and between winding.
- All three line terminals of the winding to be tested are connected together.
- Other winding terminals which are not under test and also tank of the transformer should be connected to earth.
- Then a single-phase power frequency voltage of shape approximately sinusoidal is applied for 60 seconds to the terminals of the winding under test.
- The test shall be performed on all the windings one by one.
- The test is successful if no break down in the dielectric of the insulation occurs during test.
The values of test voltage for different fully insulated winding are furnished below in the table.
|Rated short duration |
power frequency withstand
|415V||1.1 KV||3 KV|
|11 KV||12 KV||28 KV|
|33 KV||36 KV||70 KV|
|132 KV||145 KV||230 / 275 KV|
|220 KV||245 KV||360 / 395 KV|
|400 KV||420 KV||570 / 630 KV|
|Winding with graded insulation, which has neutral intended for direct earthing, |
is tested at 38KV
Induced Voltage Test of TransformerThe induced voltage test of transformer is intended to check the inter turn and line end insulation as well as main insulation to earth and between windings-
- Keep the primary winding of transformer open circuited.
- Apply three phase voltage to the secondary winding. The applied voltage should be twice of rated voltage of secondary winding in magnitude and frequency.
- The duration of the test shall be 60 second.
- The test shall start with a voltage lower than 1/3 the full test voltage, and it shall be quickly increased up to desired value.