Insulation Resistance Measurement
Ampere's Circuital Law
Mechanical Equivalent of Heat
Trees and Cotrees
IntegratorClosely Related Articles
Methods of Firing Steam Boiler
Fire Tube Boiler
Water Tube Boiler
Steam Boiler Function
Feed Circuit of Boiler
Boiler Feed Water Treatment
Coal Combustion Theory
Fluidized Bed Combustion
Condenser of Turbine
Surface Steam Condenser
Economics of Power Generation
Cooling Tower Performance
Components of Cooling Tower
Power Plant Fire Protection System
MVWS Fire Protection
Foam Fire Protection System
Fire Detection System
Gas Extinguishing System
Thermal Power Plant
Hydro Power Plant
Nuclear Power Station
Diesel Power Station
Seebeck Power Generation
Cost of Electrical Energy
Gas Turbine Power Plant
Solar Energy System
Types of Solar plant
Components of a Solar Generating System
Staebler Wronski Effect
Principle of Photovoltaic Cell
Characteristics of Solar Cell
Solar PV Module
Standalone Solar Electric System
Steam Dryness Fraction
Properties of Vapour
How to Calculate Steam Consumption During Plant Start Up
Steam Distribution System
Engineering Thermodynamics Part 2
First Law of Thermodynamics
Rankine Cycle and Regenerative Feed Heating
Rankine Cycle Cogeneration
Ideal Verses Actual Rankine Cycle
Wind Energy Generation
Theory of Wind Turbine
Water Tube Boiler | Operation and Types of Water Tube Boiler
Advantages of Water Tube BoilerThere are many advantages of water tube boiler due to which these types of boiler are essentially used in large thermal power station.
- Larger heating surface can be achieved by using more numbers of water tubes.
- Due to convectional flow, movement of water is much faster than that of fire tube boiler, hence rate of heat transfer is high which results into higher efficiency.
- Very high pressure in order of 140 kg/cm2 can be obtained smoothly.
Working Principle of Water Tube BoilerThe working principle of water tube boiler is very interesting and simple. Let us draw a very basic diagram of water tube boiler. It consists of mainly two drums, one is upper drum called steam drum other is lower drum called mud drum. These upper drum and lower drum are connected with two tubes namely down-comer and riser tubes as shown in the picture.
Water in the lower drum and in the riser connected to it, is heated and steam is produced in them which comes to the upper drums naturally. In the upper drum the steam is separated from water naturally and stored above the water surface. The colder water is fed from feed water inlet at upper drum and as this water is heavier than the hotter water of lower drum and that in the riser, the colder water push the hotter water upwards through the riser. So there is one convectional flow of water in the boiler system. More and more steam is produced the pressure of the closed system increases which obstructs this convectional flow of water and hence rate production of steam becomes slower proportionately. Again if the steam is taken trough steam outlet, the pressure inside the system falls and consequently the convectional flow of water becomes faster which result in faster steam production rate. In this way the water tube boiler can control its own pressure. Hence this type of boiler is referred as self controlled machine.
Types of Water Tube BoilerThere are many types of water tube boiler .
- Horizontal Straight Tube Boiler.
- Bent Tube Boiler.
- Cyclone Fired Boiler.
- Longitudinal Drum Boiler
- Cross Drum Boiler.
- Two Drum Bent Tube Boiler.
- Three Drum Bent Tube Boiler.
- Low Head Three Drum Bent Tube Boiler.
- Four Drum Bent Tube Boiler.
Horizontal or Longitudinal or Babcock-Wilcox Water Tube Boiler
Construction of Babcock-Wilcox BoilerBabcock-Wilcox Boiler is also known as Longitudinal Drum Boiler or Horizontal Tubes Boiler. In this type of boiler, one cylindrical drum is longitudinally placed above the heat chamber. In rear of the drum down comer tube is filled and in front of the drum riser tube is fitted as shown in the figure. These down-comer tube and riser tube are connected to each other by 5o to 15o straight water tubes as shown in the figure.
Working Principle of Longitudinal Drum Water Tube BoilerWorking principle of Babcock – Wilcox Boiler depends upon thermonyphon principle. The longitudinally placed drum as mentioned in the construction of longitudinal drum boiler, is fed by colder mater at its rear feed water inlet. As the colder water is heavier it falls down through down-comer fitted at the rear part of the drum. From down-comer the water enters in to horizontal water tube where it becomes hot and lighter. As the water becomes lighter, it passes up through these inclined horizontal tubes and ultimately comes back to the boiler drum through riser. During travelling of water through inclined water tubes, it absorbs heat of the hot gases, surrounds the water tube, consequently steam bubbles are created in these tubes. These steam bubbles then come to the steam drum through riser and naturally separated from water and occupies the space above the water surface in the longitudinal drum of Babcock – Wilcox Boiler.
Cross Drum Water Tube Boiler
Construction of Cross Drum Water Tube BoilerCross Drum Boiler is essentially a variant of the Longitudinal Drum Boiler. In Cross Drum Boiler the steam drum is placed at cross ways to the heat source as shown in the figure. Here, the down-comer is fitted on the bottom of the drum and riser is fitted on the top of the drum via a horizontal tube as shown in the figure. 5o to 15o inclined water tubes are connected with down-comer and riser tubes in same manner of Babcock-Wilcox boiler.
Working Principle of Cross Drum BoilerThe working principle of cross drum boiler is same as longitudinal drum boiler.
- The feed water is fed to the cross drum through feed water inlet.
- Then this water comes down through the down-comer pipe and enters into inclined water tube placed in hot chamber.
- Here, the water becomes hot and steam is produced in the water which comes into steam chamber.
- Here in the steam drum steam is separated from water in natural way.
Bend Tube Boiler or Sterling BoilerBend Tube Boiler or Sterling Boiler is the developed version of water tube boiler. The working principle of bend tube boiler is more or less same as other water tube boilers, but it utilizes four drums.
Construction of Bend Tube BoilerThree drums are placed on the heat source as shown on the figure. Fourth drum is placed inside the heat chamber and this fourth drum is connected to upper three steam drums with help of bend water tube. Upper three drums are connected with equalizer tubes as shown in the figure. Steam is taken from equalizer tubes.
Working Principle of Bent Tube or Stirling BoilerThe feed water first enters into right most upper drum. Due to more density this water comes down in the lower water drum. The water within that water drum and the connecting pipes to the other two upper drums, are heated up and consequently steam bubbles are produced. This is the most basic working principle of bent tube boiler .
Capacity of Stirling BoilerCapacity of Stirling Boiler is much higher than Babcock - Wilcox boiler as high as 50,000kg per hour and pressure as high as 60kg/cm 2.
Closely Related Articles Steam Boiler | Working principle and Types of BoilerMethods of Firing Steam BoilerFire Tube Boiler | Operation and Types of Fire Tube BoilerSteam Boiler Furnace Grate Firebox Combustion Chamber of FurnaceFeed Water and Steam Circuit of BoilerBoiler Feed Water Treatment Demineralization Reverse Osmosis Plant DeaeratorCoal Combustion TheoryFluidized Bed Combustion | Types and Advantages of Fluidized Bed CombustionMore Related Articles Steam Condenser of TurbineJet Condenser | Low Level High Level Ejector Jet CondenserSurface Steam Condenser Economics of Power GenerationCooling Tower Useful Terms and Cooling Tower PerformanceCooling Tower Material and Main ComponentsPower Plant Fire Protection SystemHydrant System for Power Plant Fire ProtectionMedium Velocity Water Spray or MVWS System for Fire ProtectionFoam Fire Protection SystemFire Detection and Alarm SystemGas Extinguishing SystemElectric Power GenerationPower Plants and Types of Power PlantThermal Power Generation Plant or Thermal Power StationHydro Power Plant | Construction Working and History of Hydro power plantNuclear Power Station or Nuclear Power PlantDiesel Power StationWhy Supply Frequency is 50 Hz or 60 Hz?Economiser in Thermal Power Plant | EconomiserMHD Generation or Magneto Hydro Dynamic Power Generation Cogeneration | Combined Heat and PowerThermoelectric Power Generators or Seebeck Power GenerationCost of Electrical EnergyGas Turbine Power PlantNuclear ReactorSolar ElectricitySolar Energy System | History of Solar EnergyTypes of Solar Power StationComponents of a Solar Electric Generating SystemWhat is Photovoltaic Effect?Staebler Wronski EffectWorking Principle of Photovoltaic Cell or Solar CellSolar CellCharacteristics of a Solar Cell and Parameters of a Solar CellSolar Cell Manufacturing TechnologyWhat is a Solar PV Module?What is Standalone Solar Electric System?Solar LanternSteamSteam Dryness FractionSuperheated Steam and Steam Phase DiagramVapour Properties Mollier Chart Heat CapacitiesWhat is Steam Flashing?How to Calculate Steam Consumption During Plant Start Up Effective Steam Distribution SystemWhat is Water Hammer?Engineering Thermodynamics Part 1Science of Engineering Thermodynamics Part 2Basic Law of Conservation and First Law of Thermodynamics Carnot Cycle and Reversed Carnot CycleEnthalpy Entropy and Second Law of ThermodynamicsRankine CycleRankine Cycle and Regenerative Feed HeatingRankine Cycle for Closed Feed Water Heaters and Rankine Cycle CogenerationIdeal Verses Actual Rankine CycleRankine Cycle Efficiency Improvement TechniquesWind Energy Electricity GenerationTheory of Wind Turbine Wind Turbine | Working and Types of Wind TurbineBasic Construction of Wind TurbineNew Articles Measurement of Insulation ResistanceAmpere's Circuital LawMechanical Equivalent of HeatTrees and Cotrees of Electric NetworkDifferentiatorIntegrator