Principle of Water Content Test of Insulating Oil
Collecting Oil Sample from Oil Immersed Electrical Equipment
Causes of Insulating Oil Deterioration
Acidity Test of Transformer Insulating Oil
Magnetic FieldClosely Related Articles
Electric Power Generation
Power Plants and Types of Power Plant
Thermal Power Generation Plant or Thermal Power Station
Hydro Power Plant | Construction Working and History of Hydro power plant
Nuclear Power Station or Nuclear Power Plant
Diesel Power Station
Why Supply Frequency is 50 Hz or 60 Hz?
Economiser in Thermal Power Plant | Economiser
MHD Generation or Magneto Hydro Dynamic Power Generation
Cogeneration | Combined Heat and Power
Thermoelectric Power Generators or Seebeck Power Generation
Cost of Electrical Energy
Gas Turbine Power Plant
Steam Boiler | Working principle and Types of Boiler
Methods of Firing Steam Boiler
Fire Tube Boiler | Operation and Types of Fire Tube Boiler
Water Tube Boiler | Operation and Types of Water Tube Boiler
Steam Boiler Furnace Grate Firebox Combustion Chamber of Furnace
Feed Water and Steam Circuit of Boiler
Boiler Feed Water Treatment Demineralization Reverse Osmosis Plant Deaerator
Coal Combustion Theory
Fluidized Bed Combustion | Types and Advantages of Fluidized Bed Combustion
Steam Condenser of Turbine
Jet Condenser | Low Level High Level Ejector Jet Condenser
Surface Steam Condenser
Economics of Power Generation
Cooling Tower Useful Terms and Cooling Tower Performance
Cooling Tower Material and Main Components
Power Plant Fire Protection System
Hydrant System for Power Plant Fire Protection
Medium Velocity Water Spray or MVWS System for Fire Protection
Foam Fire Protection System
Fire Detection and Alarm System
Gas Extinguishing System
Solar Energy System
Types of Solar Power Station
Components of a Solar Electric Generating System
Staebler Wronski Effect
Principle of Photovoltaic Cell
Characteristics of Solar Cell
Solar Cell Manufacturing Technology
Solar PV Module
Standalone Solar Electric System
Steam Dryness Fraction
Superheated Steam and Steam Phase Diagram
Vapour Properties Mollier Chart Heat Capacities
How to Calculate Steam Consumption During Plant Start Up
Effective Steam Distribution System
Engineering Thermodynamics Part 1
Engineering Thermodynamics Part 2
First Law of Thermodynamics
Enthalpy Entropy and Second Law of Thermodynamics
Rankine Cycle and Regenerative Feed Heating
Rankine Cycle for Closed Feed Water Heaters and Rankine Cycle Cogeneration
Ideal Verses Actual Rankine Cycle
Rankine Cycle Efficiency Improvement Techniques
Wind Energy Electricity Generation
Theory of Wind Turbine
Basic Construction of Wind Turbine
Thermoelectric Power Generators or Seebeck Power Generation
The power generated due to Seebeck power generation is single phase DC and given by I2RL or VI where RL is the load resistance. The output voltage and output power are increased either by increasing the temperature difference between the hot and cold ends or by connecting several thermoelectric power generators in series. The current will continue to flow as long as heat is supplied to the hot junction and removed from the cold junction. This current produced by thermoelectric or Seebeck power generation is DC in nature and can be converted into AC by using invertors and its voltage level can be further step up by using transformers. The energy conversion through thermoelectric or Seebeck power generation is reversible process i.e the direction of energy flow can be reversed. If we remove load and supply DC power across the terminals where load was connected, the heat can be easily drawn from the thermoelectric power generator.
Performance Analysis of Thermoelectric Power GeneratorConsider a thermoelectric power generator having heat source at one end and heat sink at other end. The heat source is kept at high temperature as compare to heat sink. Let the temperature difference between two junctions is ΔT. The sides of generating device are insulated so, the heat flows along the length only. The applied heat to the hot junction causes the electrons in the n type block and the holes in the p type block to flow away from the heat junction and thereby producing a electrical potential difference. The circuit is completed by connecting a load resistance, RL. The current will start flowing through this load resistance, RL.
The voltage of this generator is given by V = α ΔT where α is Seebeck coefficient and ΔT is the temperature difference between hot and cold junction. Let R is the internal resistance of the thermoelectric power generator then the current flowing through the external resistance RL is given by Substitute the value of voltage in above equation we get current, We know that power flow to external load is given by, PL = I2RL Substitute the value of I This power will be maximum when R = RL So, maximum power is given by In Seebeck Power Generation the term (α2 / R) is called figure of merit. For power to be maximum ΔT and (α2 / R) should have large value or we can say internal resistance should be low and this can be done by decreasing the length and increasing the diameter. ΔT can be increased by increasing the temperature difference between heat source and heat sink.
Efficiency of Thermoelectric Power GeneratorThe efficiency of thermoelectric power generator is defined as the ratio of power developed, PL across load resistance, RL to the heat flow, Q from the source
Materials Suitable for Thermoelectric Power GeneratorsThe most commonly used material for this generator is lead telluride. Lead telluride is a compound made of lead and tellurium having small amount of bismuth or sodium. Other compounds used for making thermoelectric power generators are bismuth telluride, bismuth sulphide, germanium telluride, zinc antimonite, tin telluride and indium arsenide etc.
Application of Thermoelectric Generators
- For increasing the fuel efficiency of cars, thermoelectric generators are used. These generator use heat produced when the vehicle is running.
- Seebeck Power Generation is used to supply power to spacecrafts.
- These generators are used to supply power to remote stations like weather stations, relay stations etc.
Limitations of Thermoelectric Power Generators
- High output resistance required - As explained earlier for getting high output voltage and power several thermoelectric generators are connected in series, which in turn increases the total output resistance. Therefore for transferring high power efficiently large resistances are needed. This problem can be overcome by connecting more thermoelectric elements in parallel rather in series because it causes decrease in effective resistance.
- Thermoelectric power generators generate less electric power for the same heat flow i.e they have low efficiency as compared to other mechanical generators. For the same energy input, the Seebeck Power Generation produces less output as compare to other energy converters.
- Low thermal characteristics - The heat dissipation of any device depends upon its thermal conductivity. Any good thermoelectric power generator has low thermal conductivity and hence poor heat dissipation. So, these generators are efficient only when small power is required.
- Thermoelectric generators are costly as compare to other generators.
Closely Related Articles Electric Power GenerationPower Plants and Types of Power PlantThermal Power Generation Plant or Thermal Power StationHydro Power Plant | Construction Working and History of Hydro power plantNuclear Power Station or Nuclear Power PlantDiesel Power StationWhy Supply Frequency is 50 Hz or 60 Hz?Economiser in Thermal Power Plant | EconomiserMHD Generation or Magneto Hydro Dynamic Power Generation Cogeneration | Combined Heat and PowerCost of Electrical EnergyGas Turbine Power PlantNuclear ReactorMore Related Articles Steam Boiler | Working principle and Types of BoilerMethods of Firing Steam BoilerFire Tube Boiler | Operation and Types of Fire Tube BoilerWater Tube Boiler | Operation and Types of Water Tube BoilerSteam Boiler Furnace Grate Firebox Combustion Chamber of FurnaceFeed Water and Steam Circuit of BoilerBoiler Feed Water Treatment Demineralization Reverse Osmosis Plant DeaeratorCoal Combustion TheoryFluidized Bed Combustion | Types and Advantages of Fluidized Bed CombustionSteam Condenser of TurbineJet Condenser | Low Level High Level Ejector Jet CondenserSurface Steam Condenser Economics of Power GenerationCooling Tower Useful Terms and Cooling Tower PerformanceCooling Tower Material and Main ComponentsPower Plant Fire Protection SystemHydrant System for Power Plant Fire ProtectionMedium Velocity Water Spray or MVWS System for Fire ProtectionFoam Fire Protection SystemFire Detection and Alarm SystemGas Extinguishing SystemSolar ElectricitySolar Energy System | History of Solar EnergyTypes of Solar Power StationComponents of a Solar Electric Generating SystemWhat is Photovoltaic Effect?Staebler Wronski EffectWorking Principle of Photovoltaic Cell or Solar CellSolar CellCharacteristics of a Solar Cell and Parameters of a Solar CellSolar Cell Manufacturing TechnologyWhat is a Solar PV Module?What is Standalone Solar Electric System?Solar LanternSteamSteam Dryness FractionSuperheated Steam and Steam Phase DiagramVapour Properties Mollier Chart Heat CapacitiesWhat is Steam Flashing?How to Calculate Steam Consumption During Plant Start Up Effective Steam Distribution SystemWhat is Water Hammer?Engineering Thermodynamics Part 1Science of Engineering Thermodynamics Part 2Basic Law of Conservation and First Law of Thermodynamics Carnot Cycle and Reversed Carnot CycleEnthalpy Entropy and Second Law of ThermodynamicsRankine CycleRankine Cycle and Regenerative Feed HeatingRankine Cycle for Closed Feed Water Heaters and Rankine Cycle CogenerationIdeal Verses Actual Rankine CycleRankine Cycle Efficiency Improvement TechniquesWind Energy Electricity GenerationTheory of Wind Turbine Wind Turbine | Working and Types of Wind TurbineBasic Construction of Wind TurbineNew Articles Principle of Water Content Test of Insulating OilCollecting Oil Sample from Oil Immersed Electrical EquipmentCauses of Insulating Oil DeteriorationAcidity Test of Transformer Insulating OilMagnetic Flux