Step Up Transformeron 24/2/2012 & Updated on Sunday 15th of April 2018 at 08:54:42 AM
The transformer can transfer energy in both directions, from HV to LV side as well as inversely. That is the reason why it can work as voltage step up or step down transformer. Both transformer types have the same design and construction. Theoretically, we can operate any transformer as step-up as well as step-down type. It only depends on the energy flowing direction. The HV windings contain a huge number of turns compared with the LV windings. An LV winding wire has bigger cross-section than HV wire because of higher current value on the LV side. Usually, we place the LV windings close to the transformer core, and over them, we wound the HV windings.
Transformer turns ratio is approximately proportional to the voltage ratio. Where U1,2 are voltages and N1,2 are the turns numbers on HV and LV side). The primary side of a step-up transformer has a small number of turns (LV side) while secondary side has a large number of turns (HV side). That means energy flows from the LV to HV side. The most important application of step-up transformer is a generator step-up (GSU) transformer used in all generating plants. Those transformers usually have large turns ratio value. The voltage value produced in energy generation is increased and prepared to the long distance energy transmission. The energy produced in generating plant is at low voltage and high current values. Depending on the generating plant type, the GSU transformer has nominal primary voltage value from 6 up to 20 kV.
The nominal voltage value of GSU secondary side can be 110 kV, 220 kV, 410 kV depending on energy transmission system connected to the GSU secondary side. The current value on the primary GSU side is usually very high and depending on the nominal transformer power can reach even 30000 A. This current value is not practical for energy transmission and has to decrease because of the transmission power losses (R × I2). Long distance energy transmission would not be possible. Besides the GSU transformer also makes galvanic isolation between the generator and electrical network.
Applications of Step Up TransformerThe small step-up transformers can be used in electronic and electrical devices where the voltage boosting is required. But nowadays in the modern electronic device, power electronic circuits are more frequently used because of weight and dimension. As we told already, giant power step-up transformer is used as generating step-up transformer for stepping up the generated power to a higher voltage level for efficient transmission purposes.
Rating = 3.5 & Total votes = 4