Series and Parallel Inductors
Measurement of Loss
Insulation Resistance Measurement
Ampere's Circuital LawClosely Related Articles
Power Plant Fire Protection System
MVWS Fire Protection
Foam Fire Protection System
Fire Detection System
Gas Extinguishing System
Methods of Firing Steam Boiler
Fire Tube Boiler
Water Tube Boiler
Steam Boiler Function
Feed Circuit of Boiler
Boiler Feed Water Treatment
Coal Combustion Theory
Fluidized Bed Combustion
Condenser of Turbine
Surface Steam Condenser
Economics of Power Generation
Cooling Tower Performance
Components of Cooling Tower
Thermal Power Plant
Hydro Power Plant
Nuclear Power Station
Diesel Power Station
Seebeck Power Generation
Cost of Electrical Energy
Gas Turbine Power Plant
Solar Energy System
Types of Solar plant
Components of a Solar Generating System
Staebler Wronski Effect
Principle of Photovoltaic Cell
Characteristics of Solar Cell
Solar PV Module
Standalone Solar Electric System
Steam Dryness Fraction
Properties of Vapour
How to Calculate Steam Consumption During Plant Start Up
Steam Distribution System
Engineering Thermodynamics Part 2
First Law of Thermodynamics
Rankine Cycle and Regenerative Feed Heating
Rankine Cycle Cogeneration
Ideal Verses Actual Rankine Cycle
Wind Energy Generation
Theory of Wind Turbine
Hydrant System for Power Plant Fire Protection
Power Plant Fire Protection System (Part-II of III)This section comprises of water based fire protection system called hydrant system in thermal power plants. Flow Scheme for a Typical 660 MW Unit
Hydrant SystemHydrant system shall consist of a fire water ring main network of piping along with:
- Isolation gate valves installed above ground on RCC pedestals around areas to be protected.
- Hydrant valves (external/internal)
- Hose cabinets
- Branch pipe
- Nozzles and water monitors along with all accessories.
- Other accessories like MS painted hose box shall be provided as per TAC.
- External hydrants Hose houses or hose boxes shall be located all around the periphery of buildings and internal hydrants “hose box” shall be provided at each landing floor of staircases through above ground main.
- ESP areas,
- Boiler house
- Tall building
- Coal stock pile area
- Bunker building
- Junction tower/transfer towers and
- Other areas in the coal conveyor at locations where water can’t reach from hydrant system.
Hydrant System RequirementsHydrant system requirements shall be designed keeping the following aspects of design in mind in line with the TAC requirements:
- The hydrant network shall be sized to ensure that about 3.5 Kg/cm2 pressures are available at the hydraulically remotest point (as per TAC) in the system with the hydrant pump discharging the flow at rated pump capacity and head.
- The velocity in the hydrant main shall not exceed 5.0 m/s.
- At least two hydrants shall be provided with separate ring main for the main plants.
- Spacing of each outdoor hydrant shall be provided 45 meters distance. The internal hydrant/landing valves shall be provided 45 meters distance in case of TG halls, Mill bay, Boiler and other area 30 Meters distance at each floor space.
- Building shall be deemed to be protected by a hydrant if the hydrant is within 15 meters of the building.
- Each of the landing valves and external hydrant valves associated with the main plant like transformer yard, TG building and Boiler area to be provided with a hose box.
- Each ring mains to be terminated with an isolation valve and a blind flange at all the corners to enable future expansion/modification.
- Fire water booster system pump head shall be designed for farthest top most point of the boiler and pressure will be tested at that elevation.
- All the landings of boiler staircase, turbine buildings and other multi-storied structures, coal handling plant transfer points/junction towers, crusher house, bunker floors and other auxiliary buildings/non-plant buildings shall be provided with landing valves with hose box including the hose reels.
Spray SystemThe spray system works automatically. The deluge valves are operated and controlled by fire detection devices i.e. quartzite bulb detectors or by some other means of fire detection. The system could be pressurized till to the Deluge valves. It covers all transformers located area, turbine and its auxiliaries, all oil storage tanks, cooling units and purifiers units. The equipment used in the whole system is spray pumps, the pressure controlling unit, variety of valves and strainers. There are two methods of spray system:
- High Velocity Water spray system (HVWS system)
- Medium Velocity Water spray system (MVWS system)
High Velocity Water Spray System (HVWS)HVWS shall be designed as per TAC regulations. HVWS shall consists of above group piping, along with relevant fittings, deluge valves, isolation gate valves, spray nozzles, Quartzite bulb detector and pressure switches. HVWS system shall be equipped with the provision of automatically detect, control & extinguish any outburst of fire. The system shall allow hydraulically open the deluge valve thus allowing water to be sprayed on the equipment/area through projector nozzles in the form of a solid conical emulsifying spray.
Isolation gate valve and y-type strainer shall be provided on upstream and downstream side of the deluge valve. Fast acting butterfly valve shall be provided as a by-pass to deluge valve, so that this valve can be kept closed and can be operated manually in case of malfunction of deluge valve. The pressure at the hydraulically most remote point in the network shall not be less than 3.5 bars for outdoor transformers as per TAC. Placing of spray nozzles shall be such that their spray nozzles should cones overlap each other.
Areas covered under HVWS are:
- All oil filled Generator transformers and its surrounding areas.
- Unit auxiliary transformers.
- Unit transformers.
- Station auxiliary transformers.
- Stand-by maintenance transformers.
- Bus reactors.
- CHP auxiliary transformers.
- AHP auxiliary transformers.
- Station transformer (transformer rating 10 MVA and above).
- All type of oil storage tanks.
- Oil coolers and purifiers unit.
- Boiler's burner and its surroundings.
- Turbine Lube oil storage tanks and Turbine Oil purifier.
- Clean and dirty lube oil tanks.
- Boiler Feed Pumps lube oil tanks, coolers, consoles etc.
- Turbine Oil canal pipelines in main plant.
- Fuel Oil Pressurizing and Heating Units
Closely Related Articles Power Plant Fire Protection SystemMedium Velocity Water Spray or MVWS System for Fire ProtectionFoam Fire Protection SystemFire Detection and Alarm SystemGas Extinguishing SystemMore Related Articles Steam Boiler | Working principle and Types of BoilerMethods of Firing Steam BoilerFire Tube Boiler | Operation and Types of Fire Tube BoilerWater Tube Boiler | Operation and Types of Water Tube BoilerSteam Boiler Furnace Grate Firebox Combustion Chamber of FurnaceFeed Water and Steam Circuit of BoilerBoiler Feed Water Treatment Demineralization Reverse Osmosis Plant DeaeratorCoal Combustion TheoryFluidized Bed Combustion | Types and Advantages of Fluidized Bed CombustionSteam Condenser of TurbineJet Condenser | Low Level High Level Ejector Jet CondenserSurface Steam Condenser Economics of Power GenerationCooling Tower Useful Terms and Cooling Tower PerformanceCooling Tower Material and Main ComponentsElectric Power GenerationPower Plants and Types of Power PlantThermal Power Generation Plant or Thermal Power StationHydro Power Plant | Construction Working and History of Hydro power plantNuclear Power Station or Nuclear Power PlantDiesel Power StationWhy Supply Frequency is 50 Hz or 60 Hz?Economiser in Thermal Power Plant | EconomiserMHD Generation or Magneto Hydro Dynamic Power Generation Cogeneration | Combined Heat and PowerThermoelectric Power Generators or Seebeck Power GenerationCost of Electrical EnergyGas Turbine Power PlantNuclear ReactorSolar ElectricitySolar Energy System | History of Solar EnergyTypes of Solar Power StationComponents of a Solar Electric Generating SystemWhat is Photovoltaic Effect?Staebler Wronski EffectWorking Principle of Photovoltaic Cell or Solar CellSolar CellCharacteristics of a Solar Cell and Parameters of a Solar CellSolar Cell Manufacturing TechnologyWhat is a Solar PV Module?What is Standalone Solar Electric System?Solar LanternSteamSteam Dryness FractionSuperheated Steam and Steam Phase DiagramVapour Properties Mollier Chart Heat CapacitiesWhat is Steam Flashing?How to Calculate Steam Consumption During Plant Start Up Effective Steam Distribution SystemWhat is Water Hammer?Engineering Thermodynamics Part 1Science of Engineering Thermodynamics Part 2Basic Law of Conservation and First Law of Thermodynamics Carnot Cycle and Reversed Carnot CycleEnthalpy Entropy and Second Law of ThermodynamicsRankine CycleRankine Cycle and Regenerative Feed HeatingRankine Cycle for Closed Feed Water Heaters and Rankine Cycle CogenerationIdeal Verses Actual Rankine CycleRankine Cycle Efficiency Improvement TechniquesWind Energy Electricity GenerationTheory of Wind Turbine Wind Turbine | Working and Types of Wind TurbineBasic Construction of Wind TurbineNew Articles Series and Parallel Inductors Electric PowerMeasurement of Losses in Shunt ReactorThree Phase Shunt ReactorMeasurement of Insulation ResistanceAmpere's Circuital Law