Fluidized Bed Combustion | Types and Advantages of Fluidized Bed Combustion
Fluidization is a method of mixing fuel and air in a specific proportion, for obtaining combustion. A fluidized bed may be defined as the bed of solid particles behaving as a fluid. It operates on the principal that when an evenly distributed air is passed upward through a finely divided bed of solid particles at low velocity, the particles remain undisturbed, but if the velocity of air flow is steadily increased, a stage is reached when the individual particles are suspended in the air stream. If the air velocity is further increased, the bed becomes highly turbulent and rapid mixing of particles occur which appear like formation of bubbles in a boiling liquid and the process of combustion as a result is known as fluidized bed combustion.
The velocity of air, causing fluidization depends on a number of parameter, like :-
- Size of fuel particles.
- Density of air fuel mixture.
A fluidized furnace has an enclosed space with a base having openings to admit air. Crushed coal, ash and crushed dolomite or limestone is mixed in the bed furnace and high velocity combustion air is then passed through the bed, entering from the furnace bottom.
With the steady increase in the velocity of air, a stage will be reached when the pressure drop across the bed becomes equal to the weight per unit cross-section of the bed, and this particular critical velocity is called the minimum fluidizing velocity. With further increase in velocity of air, the bed will begin to expand and allow passage of additional air, in the form of bubbles. When the air velocity becomes 3 to 5 times the critical velocity, the bed resembles to that of a violently boiling liquid. A pictorial representation of fluidized bed combustion is given in the figure below :- The evaporator tubes of boiler are directly immersed in the fluidized bed and the tubes, being in direct contact with the burning coal particles, produce very high heat transfer rates. Because of this, the unit size is reduced to a great extent, and also produces combustion with very high efficiency.
Types of Fluidized Bed Combustion (FBC)Fluidized Bed combustion can be in 2 variants, namely :-
- Vertical type FBC:
These are generally used in smaller plant, and has the capacity to produce steam of up to 6 tonnes per hour only. Their vertical shape reduces the overall dimension of the steam boiler, and is extremely efficient in plants, where space provision is limited.
- Horizontal type FBC:
There are almost 10 times in capacity when compared to vertical type fluidized bed combustion. They can produce as much as 60 tonnes of steam per hour, and are placed horizontally with respect to the boiler tubes. The high capacity of the horizontal type Fluidized boilers coupled with their high efficiency, makes them an extremely desirable choice for the coal fired thermal power generating station.
Advantages and Dis-advantages of Fluidized Bed CombustionFBC is being used exhaustively these days in all major power stations all over the globe, owing to numerous advantages that it offers over the other pre-dominant methods of combustion. Few of those are :-
- High thermal efficiency.
- Easy ash removal system, to be transferred for made cement.
- Short commissioning and erection period.
- Fully automated and thus ensures safe operation, even at extreme temperatures.
- Efficient operation at temperatures down to 150oC (i.e. well below the ash fusion temperature).
- Reduced coal crushing etc. (pulverised coal is not a necessity here).
- The system can respond rapidly to changes in load demand, due to quick establishment of thermal equilibrium between air and fuel particles in the bed.
- The operation of fluidized bed furnace at lower temperature helps in reducing air pollution. The low temperature operation also reduces the formation of nitrogen oxides. By adding either dolomite (a calcium-magnesium carbonate) or lime stone (calcium carbonate) to the furnace the discharge of sulphur oxides to the atmosphere can also be reduced if desired.
|C||CHARLES KING commented on 24/05/2018|
THE PAGE IS GOOD BUT IT WOULD BE IMPROVED BY CITING SOME EXAMPLES OF ACTUAL WORKING APPLICATIONS AND THEIR SUCCESSES. I KNOW OF ONE UNIT THAT WAS INSTALLED NEAR NUCLA, CO.