Published on 24/2/2012 and last updated on Tuesday 6th of March 2018 at 03:11:16 PM
A thermal power generating plant
works based on Rankine Cycle
. There are mainly three primary inputs given to a thermal power generating plants for producing electricity
. These three most essential elements are coal, air, and water. Coal is fuel here because we are going to draw the flow diagram of a coal thermal power generating plants
. Coal creates required heat energy by combustion in the furnace. Air is supplied to the furnace to accelerate combustion rate of the coal and to continue the flow of flue gases inside the heating system. Water is required in a thermal power plant inside a boiler to produce steam
. This steam drives the turbine. The turbine is coupled to the shaft of a generator which generates electrical power as the output of the system.
Depending on these three primary inputs there are three basic flow circuits work on a thermal power generating plant.
The coal is transported from coal supplying authorities to the coal storage yard of the generating plant. From here the coal is delivered to the pulverized coal plants with the help of conveyor. After removing unwanted substances from the coal, it is pulverized in coal dust. Pulverisation makes the coal more efficient for burning. After combustion of the coal, the ash is collected to the ash handling plant. Then the ash is finally collected to the ash storage yard.
Air is supplied to the furnace with forced draught fans. But it is not directly charged to the boiler furnace before it is charged to the boiler furnace it is passed through an air preheater. In air preheater, the heat of the exhaust flue gases is transferred to the inlet air before it enters in the furnace. In the furnace, this air supplies required oxygen for the combustion. Then this air carries the generated heat and flue gases due to the combustion through the boiler tubes surfaces. Here significant part of the heat is transferred to the boiler. The flue gases then pass through the superheater where the steam
coming from boiler gets further heated up to the spearheading temperatures. Then the flue gases come to economizer where some of the remaining portions of the heat of flue gases are utilized for increasing temperature of the water before it enters in the boiler. The flue gases then pass through air preheater where a portion remaining heat is transferred to the inlet air before it enters in the boiler furnace. After passing through the air preheater, the gases ultimately goes to the chimney by induced draught fans. Normally in thermal power plants
, forced draught is used at the entry of air from the atmosphere and induced draught is used at the exit of flue gases from the system through the chimney.
Water Steam Circuit
The water steam circuit of a thermal power generating plant is a semi-closed circuit. Here comparatively not much water is required to supply to the boiler from external sources since same water is reused again and again by condensing the steam after its mechanical work of rotating turbine. Here, water is first taken from a river or any other suitable natural source of water. This water then is taken to the water treatment plant for removing unwanted particles and substances from the water. This water is then fed to the boiler through economiser. In the boiler, the water is converted into steam. This steam
then goes to the super-heater, where the steam is heated up to the superheating temperature. The superheated steam then goes to the turbine through a series of nozzles. At the outlet of these nozzles, the high pressure and high-temperature steam suddenly expands and hence gets kinetic energy. Because of this kinetic energy, the steam rotates the turbine. The turbine is coupled with generator and generator produces alternating electricity
to the grid. Suddenly expanded steam exhaust from the turbine to the condenser. Where the steam is condensed back to the water with the help of water circulating cooling system associated with cooling towers. This condensed water is then fed back to the boiler through the economizer. The water supply from an external source of water is limited here because of using condensed steam in the boiler system of the thermal power generating plant