Diversity FactorPublished on 24/2/2012 and last updated on Thursday 17th of May 2018 at 02:11:14 PM
Let us consider an electrical substation. We can categorise the loads connected to that substation as domestic loads, commercial loads, industrial loads, municipal loads, irrigation loads and traction loads.
- Domestic loads consist of light, fans, refrigerators, heaters, televisions, air conditioners water pumps etc. The maximum demand for residential loads or domestic loads occurs typically at evening.
- Commercial loads consist of the lighting of shops and electrical appliances used in stores and restaurants. The consumption of load maximises during the evening as well as the daytime also.
- Industrial loads consist of heavy industrial machinery.
- Municipal loads consist of the street lighting system, water pumping system in water pumping stations. The consumption of these loads is not also consistent throughout 24 hours.
- Irrigation consumes power during daytime only.
- Traction loads become maximum during starting and ending of office hours just.
So we now understand that the maximum demands of all loads connected to a substation do not coincide. Instead, they occur in different periods during a 24-hour span. Because of this diversity of electrical loads, we can construct comparatively lower capacity substation or a similar utility for larger connected loads. Let us name an electrical substation as X. A, B, C and E are downstream substations connected to the substation X. The maximum demand of these substations is A megawatts, B megawatts, C megawatts D megawatt, and E megawatt respectively. The simultaneous maximum demand of the X substation is X megawatt. The diversity factor substitution would be
It is needless to say that the value of diversity factor must be greater than unity. It is always desirable to have diversity factor as bigger as possible, to facilitate the commercial viability electricity utility business.
Now you are going to show you one practical example of diversity factor. A power transformer is connected to the following loads. The industrial load is 1500 kW, the domestic load is 100 kW and the municipal load is 50 kW. The maximum demand for the power transformer is 1000 kW. The diversity factor of the transformer would be