Resistance of Earth
Arc Suppression Coil or Petersen Coil
Winding Resistance Test of Shunt Reactor
Measurement of Reactance of a Shunt Reactor
Tests of Shunt ReactorClosely Related Articles
Types of Reactor
Applications of Reactors
Construction of Shunt Reactor
Tests of Shunt Reactor
Measurement of Reactance
Measurement of Resistance
Testing of Power Cable
Insulation Thickness Test
Types of Capacitor Bank
Testing of Capacitor Bank
Rating of Capacitor Bank
Switchable Capacitor Bank
Location of Capacitor Bank
Resistance of Earth
Types of Insulator
Dielectric Properties of Insulation
Transmission Tower Foundation
Towers in different Soils
Advantages of Three Phase System over Single Phase System
Inductance of Single Conductor
Inductance in Three Phase Line
Why Supply Frequency 50 or 60 Hz not Other Values than these?
Power System Stability
Load Flow Analysis
Flexible AC Transmission Systems
Tariff of Electricity
Inductance of Single Phase System
Load Flow and Y Bus
Equal Area Criterion
Steady State Stability
Electrical Transmission System
Short Transmission Line
Medium Transmission Line
Long Transmission Line
Performance of Transmission Line
Surge Impedance Loading
Advantages of Bundled Conductors
Ground Clearance of Different Transmission Lines
Arc Suppression Coil or Petersen Coil
The voltages of a three phase balanced system is shown in figure - 1. In underground high voltage and medium voltage cable network, there is always a capacitance between conductor and earth in each phase. Because of that there is always a capacitive current from phase to earth. In each phase the capacitive current leads the corresponding phase voltage by 900 as shown in figure - 2. Now suppose there is an earth fault at yellow phase of the system. Ideally, the voltage of yellow phase that is yellow phase to ground voltage becomes zero. Thus, null point of the system is shifted at the tip of the yellow phase vector, as shown in the figure – 3, below. As a result, the voltage in healthy phases (red and blue) becomes &sqrt;3 times of the original.
Naturally, the corresponding capacitive current in each healthy phase (red and blue) becomes &sqrt;3 of the original as shown in figure – 4, below.
The vector sum that is resultant of these two capacitive current now will be 3I, where I is taken as rated capacitive current per phase in the balanced system. That means, at healthy balanced condition of the system, IR = IY =
IB = I. This is illustrated in the figure – 5 below,
This resultant current then flows through the faulty path to the earth as shown below.
Now, if we connect one inductive coil of suitable inductance value (generally iron core inductor is used) between star point or neutral point of the system and ground, the scenario will be entirely changed. At faulty condition, the current through the inductor just equal and opposite in magnitude and phase of that of capacitive current through the faulty path. The inductive current also follow the faulty path of the system. The capacitive and inductive current cancels each other at the faulty path, hence there will not be any resultant current through the faulty path created due to capacitive action of the underground cable. The ideal situation is illustrated in the figure below.
This concept was first implemented by W. Petersen in 1917, that why the inductor coil is used for the purpose, called Petersen Coil.
The capacitive component of the fault current is high in the underground cabling system. When earth fault occurs, the magnitude of this capacitive current through the faulty path becomes 3 times more than rated phase to earth capacitive current of healthy phase. This causes significant shifting of zero crossing of current away from zero crossing of voltage in the system. Due to presence of this high capacitive current in the earth fault path there will be a series of re-striking at fault location. This may lead unwanted overvoltage in the system.
The inductance of the Petersen Coil is selected or adjusted at such value which causes the inductive current which can exactly neutralize the capacitive current.
Let us calculate the inductance of Petersen Coil for a 3 phase underground system.
For that let us consider capacitance between conductor and earth in each phase of a system, is C farad. Then the capacitive leakage current or charging current in each phase will be So, the capacitive current through the faulty path during single phase to earth fault is After fault, the star point will have phase voltage as the null point is shifted to fault point. So the voltage appears across the inductor is Vph. Hence, the inductive current through the coil is Now, for cancellation capacitive current of value 3I, IL must have same magnitude but 180° electrically apart. Therefore, When, design or configuration (in length and/or cross section and/or thickness and quality in insulation) of the system changes the inductance of the coil is to be adjusted accordingly. That is why often Petersen coil is provided with tap changing arrangement.
Closely Related Articles Types of Electrical ReactorSelection of Reactor for Different ApplicationsConstruction of a Shunt ReactorTests of Shunt ReactorMeasurement of Reactance of a Shunt ReactorWinding Resistance Test of Shunt ReactorMore Related Articles Electrical Power Cable Types of Overhead ConductorTesting of Electrical Power Cable | Type Test | Acceptance Test | Routine TestConductor Resistance Test of Electrical Power CablesTest for Thickness of Insulation of Power CableAnnealing Test for Wires and Conductors Tensile Test of ConductorsPersulphate Test of ConductorWrapping Test for ConductorsCapacitor Bank | Reactive Power CompensationTypes of Capacitor BankTesting of Capacitor BankSpecifications or Rating of Power Capacitor BankShunt Capacitor Switchable Capacitor Bank or Switched Capacitor BankLocation of Shunt CapacitorsResistance of EarthSystem EarthingEquipment Earthing Electrical Insulator | Insulating Material | Porcelain Glass Polymer InsulatorTypes of Electrical Insulator | Overhead InsulatorInsulation Coordination in Power SystemElectrical Insulator Testing | Cause of Insulator failureDielectric Properties of InsulationElectrical Power Substation Engineering and LayoutElectrical Bus System and Electrical Substation LayoutMobile Substation | Portable Substation | Mobile TransformerLoad Curve | Load Duration Curve | Daily Load CurveHigh Voltage Direct Current Transmission | HVDC TransmissionElectrical Transmission Tower Types and DesignMethods of Transmission Tower ErectionBasic Concept of Transmission Tower FoundationDesign of Foundations of Transmission Towers in different SoilsCorona Effect in Power SystemFerranti Effect in Power SystemAdvantages of Three Phase System over Single Phase SystemInductance in Single Conductor Power Transmission LineInductance in Three Phase Transmission LineWhy Supply Frequency 50 or 60 Hz not Other Values than these?Power System StabilityLoad Flow or Power Flow AnalysisTransient Stability in Power SystemFlexible AC Transmission Systems | FACTSTariff of Electricity in IndiaPower Factor | Calculation and Power Factor ImprovementSkin Effect in Transmission LinesInductance of Two Wire Single Phase Transmission LineAuto Reclosing Scheme of Transmission SystemLoad Flow and Y BusEqual Area CriterionSteady State StabilityElectrical Power Transmission System and NetworkTransmission Line in Power SystemVoltage in Power Electric LinesShort Transmission LineMedium Transmission LineLong Transmission LinePerformance of Transmission LineABCD Parameters of Transmission LineSag in Overhead ConductorSurge Impedance Loading or SILAdmittanceAdvantages of Bundled ConductorsBundled Conductors Used in Transmission LineGround Clearance of Different Transmission LinesNew Articles System EarthingArc Suppression Coil or Petersen CoilWinding Resistance Test of Shunt ReactorMeasurement of Reactance of a Shunt ReactorTests of Shunt Reactor