Principle of Water Content Test of Insulating Oil
Collecting Oil Sample from Oil Immersed Electrical Equipment
Causes of Insulating Oil Deterioration
Acidity Test of Transformer Insulating Oil
Magnetic FieldClosely Related Articles
Steam Dryness Fraction
Superheated Steam and Steam Phase Diagram
Vapour Properties Mollier Chart Heat Capacities
How to Calculate Steam Consumption During Plant Start Up
Effective Steam Distribution System
Steam Boiler | Working principle and Types of Boiler
Methods of Firing Steam Boiler
Fire Tube Boiler | Operation and Types of Fire Tube Boiler
Water Tube Boiler | Operation and Types of Water Tube Boiler
Steam Boiler Furnace Grate Firebox Combustion Chamber of Furnace
Feed Water and Steam Circuit of Boiler
Boiler Feed Water Treatment Demineralization Reverse Osmosis Plant Deaerator
Coal Combustion Theory
Fluidized Bed Combustion | Types and Advantages of Fluidized Bed Combustion
Steam Condenser of Turbine
Jet Condenser | Low Level High Level Ejector Jet Condenser
Surface Steam Condenser
Economics of Power Generation
Cooling Tower Useful Terms and Cooling Tower Performance
Cooling Tower Material and Main Components
Power Plant Fire Protection System
Hydrant System for Power Plant Fire Protection
Medium Velocity Water Spray or MVWS System for Fire Protection
Foam Fire Protection System
Fire Detection and Alarm System
Gas Extinguishing System
Electric Power Generation
Power Plants and Types of Power Plant
Thermal Power Generation Plant or Thermal Power Station
Hydro Power Plant | Construction Working and History of Hydro power plant
Nuclear Power Station or Nuclear Power Plant
Diesel Power Station
Why Supply Frequency is 50 Hz or 60 Hz?
Economiser in Thermal Power Plant | Economiser
MHD Generation or Magneto Hydro Dynamic Power Generation
Cogeneration | Combined Heat and Power
Thermoelectric Power Generators or Seebeck Power Generation
Cost of Electrical Energy
Gas Turbine Power Plant
Solar Energy System
Types of Solar Power Station
Components of a Solar Electric Generating System
Staebler Wronski Effect
Principle of Photovoltaic Cell
Characteristics of Solar Cell
Solar Cell Manufacturing Technology
Solar PV Module
Standalone Solar Electric System
Engineering Thermodynamics Part 1
Engineering Thermodynamics Part 2
First Law of Thermodynamics
Enthalpy Entropy and Second Law of Thermodynamics
Rankine Cycle and Regenerative Feed Heating
Rankine Cycle for Closed Feed Water Heaters and Rankine Cycle Cogeneration
Ideal Verses Actual Rankine Cycle
Rankine Cycle Efficiency Improvement Techniques
Wind Energy Electricity Generation
Theory of Wind Turbine
Basic Construction of Wind Turbine
Effective Steam Distribution System
Thus designing of steam distribution is to be given due importance along with installation and subsequently maintenance during operation. In the above shown Steam distribution network steam carry pipes are the major contributors factors in deciding the cost and the quality of steam reaching the process. The success of any steam distribution system is depend upon meeting the end process steam pressure requirement of the process plant. Thus distribution system is influenced by the factors like:
- Steam Generating working pressure.
- Minimum pressure requirement at process end.
- Pipe network frictional-resistance.
- Condensation in the steam piping due to transfer of steam heat to the outside environment.
- Therefore necessary compensation should be kept for the above pressure loss while deciding the “Maximum working pressure of the boiler”.
Advantage of Steam Generation at High PressureFollowing are the advantages of steam generation at high pressure:
- Steam generation at higher pressure occupies relatively less volume than a lower pressure.
- Steam generated at higher pressure requires smaller size steam distribution lines.
- Higher steam parameters improves the quality of steam
- Smaller diameter steam lines require lower capital investment on pipes, flanges, supports and insulation.
Disadvantages of Steam Generation at High PressureBecause of the high steam pressure following losses are increased:
- Flue gas losses
- Running losses
Pressure Reducing Valve (PRV)In the above pressure reducing station separator is installed upstream of the reducing valve to prevent entrained and ensuring high quality steam to pass through. Safety valve on the down stream side protects the system, if PRV doesn’t work.
Sizing of Steam Distribution PipingSteam piping plays a important role in meeting the end requirement of the process. Following are the critical aspects of this: Proper steam pipe sizing to avoid any over or under-sizing of the steam mains. Consequence of Over-Size Steam Pipe
- Results in larger diameter pipes, valves and other fittings and shall be more expensive.
- Requirement of increased pipe support, insulation etc.
- Cost of erection and installation shall be more.
- Cost of 80 mm pipe installation accounts for nearly 45 % higher than the cost of installing 50 mm.
- Bigger size steam pipe generates more condensate and results in requirement of more steam trapping or else wet steam shall be delivered at the point of use .50 mm.
- Similarly heat loss from the insulated pipe (80 mm) pipe work shall be approximately 20 % higher than that of 50 mm pipe.
- When the line size is undersized then we get the lower pressure at the point of use. So it the due this the performance of the process and equipment may suffer.
- Possibility of steam starvation can't be ignored.
- Chances of greater risk of water hammer, erosion and noise due to under size steam pipe size.
Closely Related Articles SteamSteam Dryness FractionSuperheated Steam and Steam Phase DiagramVapour Properties Mollier Chart Heat CapacitiesWhat is Steam Flashing?How to Calculate Steam Consumption During Plant Start Up What is Water Hammer?More Related Articles Steam Boiler | Working principle and Types of BoilerMethods of Firing Steam BoilerFire Tube Boiler | Operation and Types of Fire Tube BoilerWater Tube Boiler | Operation and Types of Water Tube BoilerSteam Boiler Furnace Grate Firebox Combustion Chamber of FurnaceFeed Water and Steam Circuit of BoilerBoiler Feed Water Treatment Demineralization Reverse Osmosis Plant DeaeratorCoal Combustion TheoryFluidized Bed Combustion | Types and Advantages of Fluidized Bed CombustionSteam Condenser of TurbineJet Condenser | Low Level High Level Ejector Jet CondenserSurface Steam Condenser Economics of Power GenerationCooling Tower Useful Terms and Cooling Tower PerformanceCooling Tower Material and Main ComponentsPower Plant Fire Protection SystemHydrant System for Power Plant Fire ProtectionMedium Velocity Water Spray or MVWS System for Fire ProtectionFoam Fire Protection SystemFire Detection and Alarm SystemGas Extinguishing SystemElectric Power GenerationPower Plants and Types of Power PlantThermal Power Generation Plant or Thermal Power StationHydro Power Plant | Construction Working and History of Hydro power plantNuclear Power Station or Nuclear Power PlantDiesel Power StationWhy Supply Frequency is 50 Hz or 60 Hz?Economiser in Thermal Power Plant | EconomiserMHD Generation or Magneto Hydro Dynamic Power Generation Cogeneration | Combined Heat and PowerThermoelectric Power Generators or Seebeck Power GenerationCost of Electrical EnergyGas Turbine Power PlantNuclear ReactorSolar ElectricitySolar Energy System | History of Solar EnergyTypes of Solar Power StationComponents of a Solar Electric Generating SystemWhat is Photovoltaic Effect?Staebler Wronski EffectWorking Principle of Photovoltaic Cell or Solar CellSolar CellCharacteristics of a Solar Cell and Parameters of a Solar CellSolar Cell Manufacturing TechnologyWhat is a Solar PV Module?What is Standalone Solar Electric System?Solar LanternEngineering Thermodynamics Part 1Science of Engineering Thermodynamics Part 2Basic Law of Conservation and First Law of Thermodynamics Carnot Cycle and Reversed Carnot CycleEnthalpy Entropy and Second Law of ThermodynamicsRankine CycleRankine Cycle and Regenerative Feed HeatingRankine Cycle for Closed Feed Water Heaters and Rankine Cycle CogenerationIdeal Verses Actual Rankine CycleRankine Cycle Efficiency Improvement TechniquesWind Energy Electricity GenerationTheory of Wind Turbine Wind Turbine | Working and Types of Wind TurbineBasic Construction of Wind TurbineNew Articles Principle of Water Content Test of Insulating OilCollecting Oil Sample from Oil Immersed Electrical EquipmentCauses of Insulating Oil DeteriorationAcidity Test of Transformer Insulating OilMagnetic Flux