Online Electrical Engineering
Design of Inductor in Switched Mode Power Supply Systems
Electrical Power Transformer | Definition and Types of Transformer
What is transformer? Definition & Working Principle of Transformer
Theory of Transformer on load and no load operation
EMF Equation of Transformer | Turns Voltage Transformation Ratio of Transformer
Resistance & Leakage Reactance or Impedance of Transformer
Equivalent Circuit of Transformer referred to Primary and Secondary
Hysteresis Eddy Current Iron or Core Losses and Copper Loss in Transformer
Open and Short Circuit Test on Transformer
Voltage Regulation of Transformer
Over Fluxing in Transformer
Parallel operation of Transformers
Transformer Accessories | Breather and Conservator Tank | Radiator
Transformer Insulating Oil and Types of Transformer Oil
Silica Gel Breather of Transformer
Conservator Tank of Transformer
Radiator of Transformer | Function of Radiator
Magnetic Oil Gauge or MOG | Magnetic Oil Level Indicator of Transformer
Oil Winding and Remote Temperature Indicator of Transformer
On Load and No Load Tap Changer of Transformer | OLTC and NLTC
Transformer Cooling System and Methods
Maintenance of Transformer
What is Auto Transformer ?
Buchholz Relay in transformer | Buchholz Relay operation and principle
Transformer Testing | Type Test and Routine Test of Transformer
Voltage and Turn Ratio Test of Transformer
Transformer Winding Resistance Measurement
Insulation Dielectric Test of Transformer
Transformer Oil and Winding Temperature Rise Test
Impulse Test of Transformer
Vector Group Test of Power Transformer
Sweep Frequency Response Analysis Test | SFRA Test
DGA or Dissolved Gas Analysis of Transformer Oil | Furfural or Furfuraldehyde Analysis
Distribution Transformer | All Day Efficiency of Distribution Transformer
Installation of Power Transformer
Commissioning of Power Transformer
Magnetizing Inrush Current in Power Transformer
Tertiary Winding of Transformer | Three Winding Transformer
Single Three Phase Transformer vs bank of three Single Phase Transformers
What is Earthing Transformer or Grounding Transformer
Air Core Transformer
High Voltage Transformer
Current Transformer CT class Ratio Error Phase Angle Error in Current Transformer
Voltage Transformer or Potential Transformer Theory
Accuracy Limit Factor and Instrument Security Factor of Current Transformer
Knee Point Voltage of Current Transformer PS Class
Differential Protection of Transformer | Differential Relays
Restricted Earth Fault Protection of Transformer | REF Protection
Core of Transformer and Design of Transformer Core
Design of High Frequency Pulse Transformer
Theory of Transformer on load and no load operation
Under Electrical Transformer
Theory of Transformer
We have discussed about the theory of ideal transformer for better understanding of actual elementary theory of transformer. Now we will go through the practical aspects one by one of an electrical power transformer and try to draw vector diagram of transformer in every step. As we said that, in an ideal transformer; there are no core losses in transformer i.e. loss free core of transformer. But in practical transformer, there are hysteresis and eddy current losses in transformer core.
Theory of Transformer on No-Load
Theory of Transformer On No-load, and Having No Winding Resistance and No Leakage Reactance of Transformer
Let us consider one electrical transformer with only core losses, which means, it has only core losses but no copper loss and no leakage reactance of transformer. When an alternating source is applied in the primary, the source will supply the current for magnetizing the core of transformer. But this current is not the actual magnetizing current, it is little bit greater than actual magnetizing current. Actually, total current supplied from the source has two components, one is magnetizing current which is merely utilized for magnetizing the core and other component of the source current is consumed for compensating the core losses in transformer. Because of this core loss component, the source current in transformer on no-load condition supplied from the source as source current is not exactly at 90° lags of supply voltage, but it lags behind an angle θ is less than 90°. If total current supplied from source is Io, it will have one component in phase with supply voltage V1 and this component of the current Iw is core loss component. This component is taken in phase with source voltage, because it is associated with active or working losses in transformer. Other component of the source current is denoted as Iμ.
This component produces the alternating magnetic flux in the core, so it is watt-less; means it is reactive part of the transformer source current.
Hence Iμ will be in quadrature with V1 and in phase with alternating flux Φ.
Hence, total primary current in transformer on no-load condition can be represented as
Now you have seen how simple is to explain the theory of transformer in no-load.
Theory of Transformer on Load
Theory of Transformer On Load But Having No Winding Resistance and Leakage ReactanceNow we will examine the behavior of above said transformer on load, that means load is connected to the secondary terminals. Consider, transformer having core loss but no copper loss and leakage reactance. Whenever load is connected to the secondary winding, load current will start to flow through the load as well as secondary winding. This load current solely depends upon the characteristics of the load and also upon secondary voltage of the transformer. This current is called secondary current or load current, here it is denoted as I2. As I2 is flowing through the secondary, a self mmf in secondary winding will be produced. Here it is N2I2, where, N2 is the number of turns of the secondary winding of transformer.
This mmf or magneto motive force in the secondary winding produces flux φ2. This φ2 will oppose the main magnetizing flux and momentarily weakens the main flux and tries to reduce primary self induced emf E1. If E1 falls down below the primary source voltage V1, there will be an extra current flowing from source to primary winding. This extra primary current I2′ produces extra flux φ′ in the core which will neutralize the secondary counter flux φ2. Hence the main magnetizing flux of core, Φ remains unchanged irrespective of load.
So total current, this transformer draws from source can be divided into two components, first one is utilized for magnetizing the core and compensating the core loss i.e. Io. It is no-load component of the primary current. Second one is utilized for compensating the counter flux of the secondary winding. It is known as load component of the primary current.
Where θ2 is the angle between Secondary Voltage and Secondary Current of transformer.
Now we will proceed one further step toward more practical aspect of a transformer.
Theory of Transformer On Load, With Resistive Winding, But No Leakage ReactanceNow, consider the winding resistance of transformer but no leakage reactance. So far we have discussed about the transformer which has ideal windings, means winding with no resistance and leakage reactance, but now we will consider one transformer which has internal resistance in the winding but no leakage reactance. As the windings are resistive, there would be a voltage drop in the windings.
We have proved earlier that, total primary current from the source on load is I1. The voltage drop in the primary winding with resistance, R1 is R1I1. Obviously, induced emf across primary winding E1, is not exactly equal to source voltage V1. E1 is less than V1 by voltage drop I1R1.
Again in the case of secondary, the voltage induced across the secondary winding, E2 does not totally appear across the load since it also drops by an amount I2R2, where R2 is the secondary winding resistance and I2 is secondary current or load current.
Similarly, voltage equation of the secondary side of the transformer will be
Theory of Transformer On Load, With Resistance As Well As Leakage Reactance in Transformer WindingsNow we will consider the condition, when there is leakage reactance of transformer as well as winding resistance of transformer.
Let leakage reactances of primary and secondary windings of the transformer are X1 and X2 respectively.
Hence total impedance of primary and secondary winding of transformer with resistance R1 and R2 respectively, can be represented as,
We have already established the voltage equation of a transformer on load, with only resistances in the windings, where voltage drops in the windings occur only due to resistive voltage drop. But when we consider leakage reactances of transformer windings, voltage drop occurs in the winding not only because of resistance, it is because of impedance of transformer windings. Hence, actual voltage equation of a transformer can easily be determined by just replacing resistances R1 & R2 in the previously established voltage equations by Z1 and Z2.
Therefore, the voltage equations are,