Parallel in Parallel Out (PIPO) Shift Register
Parallel in Serial Out (PISO) Shift Register
Serial in Parallel Out (SIPO) Shift Register
Why is Fluorescent Lamp Phosphor Coated?
Construction of Fluorescent Lamp
What is transformer? Definition and Working Principle of Transformer
EMF Equation of Transformer | Turns Voltage Transformation Ratio of Transformer
Theory of Transformer on Load and No Load Operation
Resistance and Leakage Reactance or Impedance of Transformer
Equivalent Circuit of Transformer referred to Primary and Secondary
Hysteresis Eddy Current Iron or Core Losses and Copper Loss in Transformer
Voltage Regulation of Transformer
Single Three Phase Transformer vs bank of three Single Phase Transformers
Parallel operation of Transformers
Magnetizing Inrush Current in Power Transformer
Current Transformer CT class Ratio Error Phase Angle Error in Current Transformer
Voltage Transformer or Potential Transformer Theory
Knee Point Voltage of Current Transformer PS Class
Accuracy Limit Factor and Instrument Security Factor of Current Transformer
Transformer Insulating Oil and Types of Transformer Oil
DGA or Dissolved Gas Analysis of Transformer Oil | Furfural or Furfuraldehyde Analysis
Transformer Accessories | Breather and Conservator Tank | Radiator
Silica Gel Breather of Transformer
Conservator Tank of Transformer
Radiator of Transformer | Function of Radiator
Magnetic Oil Gauge or MOG | Magnetic Oil Level Indicator of Transformer
Oil Winding and Remote Temperature Indicator of Transformer
Transformer Cooling System and Methods
On Load and No Load Tap Changer of Transformer | OLTC and NLTC
Tertiary Winding of Transformer | Three Winding Transformer
Core of Transformer and Design of Transformer Core
Restricted Earth Fault Protection of Transformer | REF Protection
Buchholz Relay in transformer | Buchholz Relay operation and principle
What is Earthing Transformer or Grounding Transformer
Differential Protection of Transformer | Differential Relays
Over Fluxing in Transformer
Transformer Testing | Type Test and Routine Test of Transformer
Transformer Winding Resistance Measurement
Voltage and Turn Ratio Test of Transformer
Vector Group Test of Power Transformer
Open and Short Circuit Test on Transformer
Insulation Dielectric Test of Transformer
Transformer Oil and Winding Temperature Rise Test
Impulse Test of Transformer
Maintenance of Transformer
Sweep Frequency Response Analysis Test | SFRA Test
Installation of Power Transformer
Commissioning of Power Transformer
Electrical Power Transformer | Definition and Types of Transformer
What is Auto Transformer ?
High Voltage Transformer
Distribution Transformer | All Day Efficiency of Distribution Transformer
Dry Type Transformer
Design of High Frequency Pulse Transformer
Air Core Transformer
Design of Inductor in Switched Mode Power Supply Systems
What is transformer? Definition and Working Principle of Transformer
Definition of TransformerElectrical power transformer is a static device which transforms electrical energy from one circuit to another without any direct electrical connection and with the help of mutual induction between two windings. It transforms power from one circuit to another without changing its frequency but may be in different voltage level.
This is a very short and simple definition of transformer, as we will go through this portion of tutorial related to electrical power transformer, we will understand more clearly and deeply "what is transformer ?" and basic theory of transformer.
Working Principle of TransformerThe working principle of transformer is very simple. It depends upon Faraday's law of electromagnetic induction. Actually, mutual induction between two or more winding is responsible for transformation action in an electrical transformer.
Faraday's Laws of Electromagnetic InductionAccording to these Faraday's laws,
"Rate of change of flux linkage with respect to time is directly proportional to the induced EMF in a conductor or coil".
Basic Theory of TransformerSay you have one winding which is supplied by an alternating electrical source. The alternating current through the winding produces a continually changing flux or alternating flux that surrounds the winding. If any other winding is brought nearer to the previous one, obviously some portion of this flux will link with the second. As this flux is continually changing in its amplitude and direction, there must be a change in flux linkage in the second winding or coil. According to Faraday's law of electromagnetic induction, there must be an EMF induced in the second. If the circuit of the later winding is closed, there must be an current flowing through it. This is the simplest form of electrical power transformer and this is the most basic of working principle of transformer.
For better understanding, we are trying to repeat the above explanation in a more brief way here. Whenever we apply alternating current to an electric coil, there will be an alternating flux surrounding that coil. Now if we bring another coil near the first one, there will be an alternating flux linkage with that second coil. As the flux is alternating, there will be obviously a rate of change in flux linkage with respect to time in the second coil. Naturally emf will be induced in it as per Faraday's law of electromagnetic induction. This is the most basic concept of the theory of transformer.
The winding which takes electrical power from the source, is generally known as primary winding of transformer. Here in our above example it is first winding. The winding which gives the desired output voltage due to mutual induction in the transformer, is commonly known as secondary winding of transformer. Here in our example it is second winding. The above mentioned form of transformer is theoretically possible but not practically, because in open air very tiny portion of the flux of the first winding will link with second; so the current that flows through the closed circuit of later, will be so small in amount that it will be difficult to measure.
The rate of change of flux linkage depends upon the amount of linked flux with the second winding. So, it is desired to be linked to almost all flux of primary winding to the secondary winding. This is effectively and efficiently done by placing one low reluctance path common to both of the winding. This low reluctance path is core of transformer, through which maximum number of flux produced by the primary is passed through and linked with the secondary winding. This is the most basic theory of transformer.
Main Constructional Parts of TransformerThe three main parts of a transformer are,
- Primary Winding of transformer - which produces magnetic flux when it is connected to electrical source.
- Magnetic Core of transformer - the magnetic flux produced by the primary winding, that will pass through this low reluctance path linked with secondary winding and create a closed magnetic circuit.
- Secondary Winding of transformer - the flux, produced by primary winding, passes through the core, will link with the secondary winding. This winding also wounds on the same core and gives the desired output of the transformer.