Uninterruptible Power Supply | UPS
Fermi Dirac Distribution Function
Fault of Electric Cable
Energy Bands in Crystals
Gallium Arsenide Semiconductor
Atomic Energy Levels
Electric Power Generation
Power Plants and Types of Power Plant
Thermal Power Generation Plant or Thermal Power Station
Hydro Power Plant | Construction Working and History of Hydro power plant
Nuclear Power Station or Nuclear Power Plant
Diesel Power Station
Why Supply Frequency is 50 Hz or 60 Hz?
Economiser in Thermal Power Plant | Economiser
MHD Generation or Magneto Hydro Dynamic Power Generation
Cogeneration | Combined Heat and Power
Thermoelectric Power Generators or Seebeck Power Generation
Cost of Electrical Energy
Gas Turbine Power Plant
Steam Boiler | Working principle and Types of Boiler
Methods of Firing Steam Boiler
Fire Tube Boiler | Operation and Types of Fire Tube Boiler
Water Tube Boiler | Operation and Types of Water Tube Boiler
Steam Boiler Furnace Grate Firebox Combustion Chamber of Furnace
Feed Water and Steam Circuit of Boiler
Boiler Feed Water Treatment Demineralization Reverse Osmosis Plant Deaerator
Coal Combustion Theory
Fluidized Bed Combustion | Types and Advantages of Fluidized Bed Combustion
Steam Condenser of Turbine
Jet Condenser | Low Level High Level Ejector Jet Condenser
Surface Steam Condenser
Economics of Power Generation
Cooling Tower Useful Terms and Cooling Tower Performance
Cooling Tower Material and Main Components
Power Plant Fire Protection System
Hydrant System for Power Plant Fire Protection
Medium Velocity Water Spray or MVWS System for Fire Protection
Foam Fire Protection System
Fire Detection and Alarm System
Gas Extinguishing System
Solar Energy Solar Electricity
Solar Energy System | History of Solar Energy
Types of Solar Power Station
Components of a Solar Electric Generating System
What is photovoltaic effect?
Staebler Wronski Effect
Working Principle of Photovoltaic Cell or Solar Cell
Characteristics of a Solar Cell and Parameters of a Solar Cell
Solar Cell Manufacturing Technology
What is a Solar PV Module?
What is Standalone Solar Electric System?
Steam Dryness Fraction
Superheated Steam and Steam Phase Diagram
Vapour Properties Mollier Chart Heat Capacities
What is Steam Flashing?
How to Calculate Steam Consumption During Plant Start Up
Effective Steam Distribution System
What is Water Hammer?
Engineering Thermodynamics Part 1
Science of Engineering Thermodynamics Part 2
Basic Law of Conservation and First Law of Thermodynamics
Carnot Cycle and Reversed Carnot Cycle
Enthalpy Entropy and Second Law of Thermodynamics
Rankine Cycle and Regenerative Feed Heating
Rankine Cycle for Closed Feed Water Heaters and Rankine Cycle Cogeneration
Ideal Verses Actual Rankine Cycle
Rankine Cycle Efficiency Improvement Techniques
Basic Wind Energy
Wind Turbine | Working Types and History of Wind Turbine
Theory of Wind Turbine
Economiser in Thermal Power Plant | Economiser
The above two mentioned constraints lay emphasis on the fact, that there is a dire need, to economize the process of power generation, and an economizer is a device that aids in doing exactly the same. So, I guess it will be worthwhile for all of us to look into the process of economization in greater details.
What is an Economizer?An economiser is a mechanical device which is used as a heat exchanger by preheating a fluid to reduce energy consumption. In a steam boiler, it is a heat ex-changer device that heats up fluids or recovers residual heat from the combustion product i.e. flue gases in thermal power plant before being released through the chimney. Flue gases are the combustion exhaust gases produced at power plants consist of mostly nitrogen, carbon dioxide, water vapor, soot carbon monoxide etc. Hence, the economiser in thermal power plants, is used to economise the process of electrical power generation, as the name of the device is suggestive of. The recovered heat is in turn used to preheat the boiler feed water, that will eventually be converted to super-heated steam. Thus, saving on fuel consumption and economising the process to a large extent, as we are essentially gathering the waste heat and applying it to, where it is required. Nowadays however, in addition to that, the heat available in the exhaust flue gases can be economically recovered using air pre-heater which are essential in all pulverized coal fired boiler.
Working Principle of EconomizerAs shown in the figure above, the flue gases coming out of the steam boiler furnace carry a lot of heat. Function of economiser in thermal power plant is to recover some of the heat from the heat carried away in the flue gases up the chimney and utilize for heating the feed water to the boiler. It is simply a heat ex-changer with hot flue gas on shell side and water on tube side with extended heating surface like Fins or Gills. Economisers in thermal power plant must be sized for the volume and temperature of flue gas, the maximum pressure drop passed the stack, what kind of fuel is used in the boiler and how much energy needs to be recovered. When the water is boiled in steam boiler, the steam is produced which is then super-heated after which it is passed to the turbines. Then the exhausted steam from turbine blades, is passed through steam condenser of turbine in which the steam is condensed and this condensed water then is pre warmed first in feed water heater then in it before re-feeding in boiler. It is placed in the passage of flue gases in between the exit from the boiler and the entry to the chimney. In this a large number of small diameter thin walled tubes are placed between two headers. The flue gases flow outside the tubes usually in counter flow.
Process of Heat Transfer in Economizer, Evaporator and SuperheaterHeat transfer to water in steam generator takes place in 3 different regimes, as shown in the figure below. Water is at first pre-heated sensibly in the economizer in liquid phase at a certain pressure from state 4 to state 5 (refer to the diagram below) till it becomes a saturated liquid. It is then send to the evaporator, where this saturated liquid is boiled associating a change of phase from 5 to 6 by absorbing the latent heat of vaporization, at that particular pressure. Now this saturated vapor in state 6 is further heated in the super-heater, to bring it to state 1, i.e. in gaseous or vapor form. For unit mass of fluid, the heat transfer equation in the 3 types of heat ex-changers are given by, QEconomizer = h5 - h4 QEvaporator = h6 - h5 QSuperheater = h1 - h6 Out, of these 3 major heat ex-changer components, only the economizer operates with, zero fuel consumption, and thus it is one of the most vital and economical equipment in a thermal power plant
Types of Economizer
CI Gilled Tube EconomizerThe gilled tube economizers are made up of cast iron which are fabricated using graded cast iron fins, have following features,
- High optimum efficiency due to proper contact of gills with tubes.
- Commonly used in plants where intoxicated flue gas is generated due to the quality of fuel burnt.
Round Gilled Tube EconomizerThis is made by mild steel fabricated with square and round fins, welded on carbon steel seamless tubes, have the feature,
- Proper contact between the tubes and fins are ensured for optimum efficiency.
Coiled Tube Type EconomizerThese are used mostly in thermal power plants and large processing units. These coiled tube type Economizers are fabricated out of carbon steel seamless, have following features,
- These are very efficient in recovering the heat from gases.
- Occupy very little space.
Horizontal Finned Tube EconomizerIn this is carbon steel seamless tube sealed – welded with horizontal fins to make a complete assembly of economizer for heat transfer, have following features,
- Proper care is taken for making the contact of fins with tubes for perfect heat transfer.
- These are used mainly used by Thermal Power Plants.
Types of Economizers Based on Boiler EfficiencyThroughout this article, we have been having a qualitative discussion on the economical aspect of the economizer, let us now see how the different types of economizers can be judicially assembled along with the boiler, in order to perceive maximum boiler efficiency. They are broadly classified into two types, as has been described below.
Non - condensing EconomizerThe most widely used one, in a thermal power plant is the non-condensing economizer. These are basically heat ex-changer coils‚ that are finned around in the form of a spiral and are located inside the flue gas duct near the exit region of the boiler. They have the ability to reduces the fuel requirements of a boiler by transferring heat from the exit flue gas to the steam boiler feed water. It is used in the case of coal-fired boilers, where the lowest temperature to which flue gas can be cooled is about 250o F (120oC).
You can well understand form the discussion above that, cooling the flue gas below 250o F and transferring that additional heat to the boiler feed water would have resulted in greater efficiency, but in a coal fired power plant, this should not be done, since coal as a fuel contains sulphur in a very large extent as impurity. And the flue gas thus formed by burning this coal, results in the formation of sulphurous compounds as by product. Now if this flue gas is allowed to cool below 250o F, condensation of the gaseous compounds result in the formation of sulphuric acid, which is considered extremely corrosive against the metal surface. Since the installation and maintenance cost of a power plant is huge, it is note-worthy that a non-condensing economizer be installed to limit the cooling capacity of the flue gas to about 250o F, i.e above the condensation temperature and increase the overall boiler efficiency by about 3 to 6 %.
Condensing EconomizerThe condensing economizers are mainly used in natural gas fired thermal power plants, as they have the ability to improve the waste heat recovery by cooling the flue gas below its condensation temperature, which is about 80o F (25oC). This particular variant of economizers result in greater efficiency of around 10 to 15% and more economical operation as it reclaims both sensible heat from the flue gas and latent heat by condensing water vapor present in the flue gas. This is contradictory to the conventional non-condensing economizers as they increase the efficiency to only about 5 %. But the condensing variant with greater value of efficiency can only be used, when the flue gas does not contain any sulphurous, nitrate or other corrosive compounds.
Applications of EconomizerIt is used in all modern plants. The use of economizer results in saving fuel consumption, increases steaming rate and boiler efficiency.
Some of the common applications of economizer are given below, In steam power plants it captures the waste heat from boiler stack gases (flue gases) and transfers it to the boiler feed water. Air-side economizers HVAC (Heating, Ventilation and Air Condition) can save energy in buildings by using cool outside air as a means of cooling the indoor space. Refrigeration : This is commonly used in industrial refrigeration where vapor compression refrigeration is essential. Systems with economizers aim to produce part of the refrigeration work on high pressures, condition in which gas compressors are normally more efficient.
Advantages and Benefits of Economizer
- It recovers more heat of flue gases which normal air pre-heater can not do.
- Due increase in fuel prices, all power plants are facing pressure for increasing boiler efficiency. So by using economizer, this pressure can be minimized.
- Power plants where it is not used, large quantity of water is required to cool the flue gas before desulphurization which is minimized by using economizers.
- The efficiency of power plant reduced when steam air pre-heater required steam.