Three Phase Circuit | Star and Delta System
There are two types of system available in electric circuit, single phase and three phase system. In single phase circuit, there will be only one phase, i.e the current will flow through only one wire and there will be one return path called neutral line to complete the circuit. So in single phase minimum amount of power can be transported. Here the generating station and load station will also be single phase. This is an old system using from previous time.In 1882, new invention has been done on polyphase system, that more than one phase can be used for generating, transmitting and for load system. Three phase circuit is the polyphase system where three phases are send together from the generator to the load.
Each phase are having a phase difference of 120o, i.e 120o angle electrically. So from the total of 360o, three phases are equally divided into 120o each. The power in three phase system is continuous as all the three phases are involved in generating the total power. The sinusoidal waves for 3 phase system is shown below- The three phases can be used as single phase each. So if the load is single phase, then one phase can be taken from the three phase circuit and the neutral can be used as ground to complete the circuit.
Why Three Phase is preferred Over Single Phase?There are various reasons for this question because there are numbers of advantages over single phase circuit. The three phase system can be used as three single phase line so it can act as three single phase system. The three phase generation and single phase generation is same in the generator except the arrangement of coil in the generator to get 120° phase difference. The conductor needed in three phase circuit is 75% that of conductor needed in single phase circuit. And also the instantaneous power in single phase system falls down to zero as in single phase we can see from the sinusoidal curve but in three phase system the net power from all the phases gives a continuous power to the load.
You may also be interested on
Till now we can say that there are three voltage source connected together to form a three phase circuit and actually it is inside the generator. The generator is having three voltage sources which are acting together in 120o phase difference. If we can arrange three single phase circuit with 120o phase difference, then it will become a three phase circuit. So 120o phase difference is must otherwise the circuit will not work, the three phase load will not be able to get active and it may also cause damage to the system. The size or metal quantity of three phase devices is not having much difference. Now if we consider the transformer, it will be almost same size for both single phase and three phase because transformer will make only the linkage of flux. So the three phase system will have higher efficiency compared to single phase because for the same or little difference in mass of transformer, three phase line will be out whereas in single phase it will be only one. And losses will be minimum in three phase circuit. So overall in conclusion the three phase system will have better and higher efficiency compared to the single phase system. In three phase circuit, connections can be given in two types:
- Star connection
- Delta connection
Star ConnectionIn star connection, there is four wire, three wires are phase wire and fourth is neutral which is taken from the star point. Star connection is preferred for long distance power transmission because it is having the neutral point. In this we need to come to the concept of balanced and unbalanced current in power system.
Delta ConnectionIn delta connection, there is three wires alone and no neutral terminal is taken. Normally delta connection is preferred for short distance due to the problem of unbalanced current in the circuit. The figure is shown below for delta connection. In the load station, ground can be used as neutral path if required. In delta connection, the line voltage is same with that of phase voltage. And the line current is √3 times of phase current. It is shown as expression below, In three phase circuit, star and delta connection can be arranged in four different ways-
- Star-Star connection
- Star-Delta connection
- Delta-Star connection
- Delta-Delta connection
|A||ASHAR commented on 10/06/2018|
Mobile app should be updated, because now its not working....it open but page not show.. thanks
|N||NABEEL SAIFI commented on 04/06/2018|
superb hats off
|A||ABHISHEK commented on 10/05/2018|
I think you have to mention some of the applications of star and delta connected in 3 phase supply
|W||WHIS commented on 18/02/2018|
Very helpful...Thank you! Keep it up. Well appreciated..