# Inductance in Transmission Line

Published on 24/2/2012 and last updated on 10/11/2018## Reason of Transmission Line Inductance

Generally, electric power is transmitted through the transmission line with AC high voltage and current. High valued alternating current while flowing through the conductor sets up magnetic flux of high strength with alternating nature. This high valued alternating magnetic flux makes a linkage with other adjacent conductors parallel to the main conductor. Flux linkage in a conductor happens internally and externally. Internally flux linkage is due to self-current and externally flux linkage due to external flux. Now the term inductance is closely related to the flux linkage, denoted by λ. Suppose a coil with N number of turn is linked by flux Φ due to current I, then, But for transmission line N = 1. We have to calculate only the value of flux Φ, and hence, we can get the transmission line inductance.## Calculation of Inductance of Single Conductor

#### Calculation of Internal Inductance due to Internal Magnetic Flux of a Conductor

Suppose a conductor is carrying current I through its length l, x is the internal variable radius of the conductor and r is the original radius of the conductor. Now the cross-sectional area with respect to radius x is πx^{2}square – unit and current I

_{x}is flowing through this cross-sectional area. So the value of I

_{x}can be expressed in term of original conductor current I and cross-sectional area πr

^{2}square – unit

Now consider small thickness dx with the 1m length of the conductor, where H_{x} is the magnetizing force due to current I_{x} around the area πx^{2}.
And magnetic flux density B_{x} = μH_{x}, where μ is the permeability of this conductor. Again, µ = µ_{0}µ_{r}. If it is considered that the relative permeability of this conductor µ_{r} = 1, then µ = µ_{0}. Hence, here B_{x} = μ_{0} H_{x}.
dφ for small strip dx is expressed by

Here entire cross-sectional area of the conductor does not enclose the above expressed flux. The ratio of the cross sectional area inside the circle of radius x to the total cross section of the conductor can be thought about as fractional turn that links the flux. Therefore the flux linkage is

Now, the total flux linkage for the conductor of 1m length with radius r is given by Hence, the internal inductance is

## External Inductance due to External Magnetic Flux of a Conductor

Let us assume, due to skin effect conductor current I is concentrated near the surface of the conductor. Consider, the distance y is taken from the center of the conductor making the external radius of the conductor. H_{y}is the magnetizing force and B

_{y}is the magnetic field density at y distance per unit length of the conductor. Let us assume magnetic flux dφ is present within the thickness dy from D

_{1}to D

_{2}for 1 m length of the conductor as per the figure. As the total current I is assumed to flow in the surface of the conductor, so the flux linkage dλ is equal to dφ. But we have to consider the flux linkage from conductor surface to any external distance, i.e. r to D

## Inductance of Two Wire Single Phase Transmission Line

Suppose conductor A of radius r_{A}carries a current of I

_{A}in opposite direction of current I

_{B}through the conductor B of radius r

_{B}. Conductor A is at a distance D from conductor B and both are of length l. They are in close vicinity with each other so that flux linkage takes place in both of the conductors due to their electromagnetic effects.

Let us consider the magnitude of current in both conductors are same and hence I_{A} = - I_{B},
Now, total flux linkage in conductor A = flux linkage by self-current of conductor A + flux linkage on conductor A due to current in the conductor B.
Similarly, flux linkage in conductor B = flux linkage by self-current of conductor B + flux linkage on conductor B due to current through conductor A.
Now if we consider a point P in close vicinity both conductor A and B, the flux linkage at point P would be, flux linkage at point P for current carrying conductor A + flux linkage at point P for current carrying conductor B i.e.

Now, ……… shown in the figure below in figure (a) and (b).

- λ
_{AAP}is the flux linkage at point P for conductor A due to current through conductor A itself. - λ
_{ABP}is the flux linkage at point P for conductor A due to current through conductor B. - λ
_{BAP}is the flux linkage at point P for conductor B due to current through conductor A. - λ
_{BBP}is the flux linkage at point P for conductor B due to current through conductor B itself.

λ_{ABP} and λ_{BAP} are negative in value because the directions current are opposite with respect to each other.

If we consider that both conductor are with same radius, i.e. r_{A} = r_{B} = r and point P is shifted to infinite distance then we can write that
If conductor A becomes bundled conductor, then its geometrical mean radius (GMR) will be calculated for n number of conductors per bundle.
Where, d is the distance between the central axis of conductors within the bundle.

## Inductance in Three Phase Transmission Line

In the**three phase transmission line**, three conductors are parallel to each other. The direction of the current is same through each of the conductors.

Let us consider conductor A produces magnetic flux φ_{A},
Conductor B produces magnetic flux φ_{B},
And conductor C produces magnetic flux φ_{C}.
When they carry the current of the same magnitude "I", they are in flux linkage with each other.
Now, let us consider a point P near three conductors. So, flux linkage at point P due to current through conductor A is,
Flux linkage at point P for conductor A due to current through conductor A =

Flux linkage at point P for conductor A due to current through conductor B = Flux linkage at point P for conductor A due to current through conductor C = Therefore, flux linkage at point P for conductor A, As, and in balanced system, then we can write that

If we arrange them in matrix form, then we get

Where, λ_{A}, λ_{B}, λ_{C} are the total flux linkages of conductor A, B and C.

L_{AA}, L_{BB} and L_{CC} are the self inductances of conductor A, B and C.

L_{AB}, L_{AC}, L_{BC}, L_{BA}, L_{CA}, L_{CB} are the mutual inductances of between conductors A, B and C.

Again balanced system And In balanced system, then we can write that Similarly,

__Related pages__

**Please Rate this Article**