01․ In which of the following given faults, all the sequence currents are equal?

Assumptions in LG faults are
1. Fault current I

_{f}= I_{R}2. I_{Y}= I_{B}= 0 3. V_{f}= I_{R}×Z_{f}= I_{f}×Z_{f}Therefore, Where, I_{R0}, I_{R1}and I_{R2}are sequence currents.02․ If all the sequence voltages at the fault point in a power system are equal, then the fault point is a

In double line to ground fault, all the sequence networks are connected in parallel. Therefore, all the sequence voltages at the fault point are equal.
V

_{R0}= V_{R1}= V_{R2}Where, V_{R0}, V_{R1}and V_{R2}are sequence voltages.03․ The zero sequence current of a generator for line to ground fault is j3 pu. Then the current through the neutral during the fault is

Assumptions in LG faults are
1. Fault current I

_{f}= I_{R}2. I_{Y}= I_{B}= 0 3. V_{f}= I_{R}×Z_{f}= I_{f}×Z_{f}Therefore, Therefore, Current through the neutral during the fault I_{f}= 3×I_{R0}I_{f}= 3× j3 = j9 pu04․ Which of the following statement is/are true?Z

_{n}A fault current of 3 I

_{R0}produces a drop of 3 I_{R0}× Z_{n}and to show in the equivalent zero sequence network the same drop where current of I_{R0}flows, the impedance should be 3 Z_{n}. Therefore, the neutral grounding impedance Z_{n}appears as 3 Z_{n}in zero sequence equivalent circuit.05․ A fault occurring at the terminals of an unloaded synchronous generator operating at its rated voltage has resulted in the following values of currents and voltages.
I

_{R0}= j 2.37 pu I_{R1}= -j 3.05 pu I_{R2}= j 0.68 pu V_{R0}= V_{R1}= V_{R2}= 0.237 pu. Which of the following faults has occurred?In double line to ground fault, all the sequence networks are connected in parallel. Therefore, all the sequence voltages at the fault point are equal.

06․ The line currents of 3-phase supply are:
I

_{R}= 3 + j 5 A I_{Y}=2 + j 2 A I_{B}= -2 - j 1 A The zero sequence current will be07․ An unloaded generator with a pre-fault voltage 1 pu has the following sequence impedance:
Z

_{0}= j 0.15 pu, Z_{1}= Z_{2}= j 0.25 pu The neutral is grounded with a reactance of 0.05 pu. The fault current in pu for single line to ground fault is08․ A power system network has n nodes, Z

_{33}of its bus impedance matrix is j0.5 pu. The voltage at node 3 is 1.3∠ -10°. If capacitor is having reactance of -j3.5 pu is now added to the network between node 3 and reference node, the current drawn by the capacitor in pu is09․ In a 3-phase, 5 kV, 5 MVA system, what is the base impedance?

10․ When is the ferranti effect on long overhead lines experienced?

Under no load conditions or light load conditions of a transmission line, receiving end voltage is greater than sending ending voltage will occur in case of medium and transmission lines. This is called ferranti effect. This is due to capacitance effect is dominating compare to inductance of transmission line under no load only.

<<<3031323334>>>