This portion of our website covers almost everything related to protection system in power system
including standard lead and device numbers, mode of connections at terminal strips, color codes in multi-core cables, Dos and Don’ts in execution. It also covers principles of various power system protection relays
and schemes including special power system protection
schemes like differential relays, restricted earth fault protection
, directional relays and distance relays etc. The details of transformer protection
, generator protection, transmission line protection & protection of capacitor
banks are also given. It covers almost everything about protection of power system
testing, instrument transformers
like current transformer
or potential transformer
testing and associated protection relay
are explained in detail.
The close and trip, indication and alarm circuits different of circuit breakers are also included and explain.
Objective of Power System Protection
The objective of power system protection
is to isolate a faulty section of electrical power
system from rest of the live system so that the rest portion can function satisfactorily without any severer damage due to fault current.
Actually circuit breaker isolates the faulty system from rest of the healthy system and this circuit breakers automatically open during fault condition due to its trip signal comes from protection relay. The main philosophy about protection is that no protection of power system can prevent the flow of fault current through the system, it only can prevent the continuation of flowing of fault current by quickly disconnect the short circuit path from the system. For satisfying this quick disconnection the protection relays should have following functional requirements.
Protection System in Power System
Let’s have a discussion on basic concept of protection system in power system
and coordination of protection relays
In the picture the basic connection of protection relay has been shown. It is quite simple. The secondary of current transformer
is connected to the current
coil of relay. And secondary of voltage transformer
is connected to the voltage
coil of the relay. Whenever any fault occurs in the feeder circuit, proportionate secondary current
of the CT will flow through the current
coil of the relay due to which mmf of that coil is increased. This increased mmf is sufficient to mechanically close the normally open contact of the relay. This relay contact actually closes and completes the DC trip coil circuit and hence the trip coil is energized. The mmf of the trip coil initiates the mechanical movement of the tripping mechanism of the circuit breaker
and ultimately the circuit breaker
is tripped to isolate the fault.
Functional Requirements of Protection Relay
The most important requisite of protective relay
is reliability. They remain inoperative for a long time before a fault occurs; but if a fault occurs, the relays must respond instantly and correctly.
The relay must be operated in only those conditions for which relays are commissioned in the electrical power
system. There may be some typical condition during fault for which some relays should not be operated or operated after some definite time delay hence protection relay must be sufficiently capable to select appropriate condition for which it would be operated.
The relaying equipment must be sufficiently sensitive so that it can be operated reliably when level of fault condition just crosses the predefined limit.
The protective relays
must operate at the required speed. There must be a correct coordination provided in various power system protection relays in such a way that for fault at one portion of the system should not disturb other healthy portion. Fault current
may flow through a part of healthy portion since they are electrically connected but relays associated with that healthy portion should not be operated faster than the relays of faulty portion otherwise undesired interruption of healthy system may occur. Again if relay associated with faulty portion is not operated in proper time due to any defect in it or other reason, then only the next relay associated with the healthy portion of the system must be operated to isolate the fault. Hence it should neither be too slow which may result in damage to the equipment nor should it be too fast which may result in undesired operation.
Important Elements for Power System Protection
Consists of mainly bulk oil circuit breaker
, minimum oil circuit breaker, SF6 circuit breaker
, air blast circuit breaker
and vacuum circuit breaker
etc. Different operating mechanisms such as solenoid, spring, pneumatic, hydraulic etc. are employed in circuit breaker
. Circuit breaker
is the main part of protection system in power system it automatically isolate the faulty portion of the system by opening its contacts.
Consists of mainly power system protection relays like current
relays, impedance relays, power relays, frequency relays, etc. based on operating parameter, definite time relays, inverse time relays, stepped relays etc. as per operating characteristic, logic wise such as differential relays, over fluxing relays etc. During fault the protection relay gives trip signal to the associated circuit breaker
for opening its contacts.
All the circuit breakers of electrical power
system are DC (Direct Current) operated. Because DC power can be stored in battery and if situation comes when total failure of incoming power occurs, still the circuit breakers can be operated for restoring the situation by the power of storage battery
. Hence, the battery
is another essential item of the power system. Some time it is referred as the heart of the electrical substation
. An electrical substation battery
or simply a station battery
containing a number of cells accumulate energy during the period of availability of AC supply and discharge at the time when relays operate so that relevant circuit breaker