Fault of Electric Cable
Energy Bands in Crystals
Gallium Arsenide Semiconductor
Atomic Energy Levels
Electric Pressure Cooker
Steam Boiler | Working principle and Types of Boiler
Methods of Firing Steam Boiler
Fire Tube Boiler | Operation and Types of Fire Tube Boiler
Water Tube Boiler | Operation and Types of Water Tube Boiler
Steam Boiler Furnace Grate Firebox Combustion Chamber of Furnace
Feed Water and Steam Circuit of Boiler
Boiler Feed Water Treatment Demineralization Reverse Osmosis Plant Deaerator
Coal Combustion Theory
Fluidized Bed Combustion | Types and Advantages of Fluidized Bed Combustion
Steam Condenser of Turbine
Jet Condenser | Low Level High Level Ejector Jet Condenser
Surface Steam Condenser
Economics of Power Generation
Cooling Tower Useful Terms and Cooling Tower Performance
Cooling Tower Material and Main Components
Power Plant Fire Protection System
Hydrant System for Power Plant Fire Protection
Medium Velocity Water Spray or MVWS System for Fire Protection
Foam Fire Protection System
Fire Detection and Alarm System
Gas Extinguishing System
Electric Power Generation
Power Plants and Types of Power Plant
Thermal Power Generation Plant or Thermal Power Station
Hydro Power Plant | Construction Working and History of Hydro power plant
Nuclear Power Station or Nuclear Power Plant
Diesel Power Station
Why Supply Frequency is 50 Hz or 60 Hz?
Economiser in Thermal Power Plant | Economiser
MHD Generation or Magneto Hydro Dynamic Power Generation
Cogeneration | Combined Heat and Power
Thermoelectric Power Generators or Seebeck Power Generation
Cost of Electrical Energy
Gas Turbine Power Plant
Solar Energy Solar Electricity
Solar Energy System | History of Solar Energy
Types of Solar Power Station
Components of a Solar Electric Generating System
What is photovoltaic effect?
Staebler Wronski Effect
Working Principle of Photovoltaic Cell or Solar Cell
Characteristics of a Solar Cell and Parameters of a Solar Cell
Solar Cell Manufacturing Technology
What is a Solar PV Module?
What is Standalone Solar Electric System?
Steam Dryness Fraction
Superheated Steam and Steam Phase Diagram
Vapour Properties Mollier Chart Heat Capacities
What is Steam Flashing?
How to Calculate Steam Consumption During Plant Start Up
Effective Steam Distribution System
What is Water Hammer?
Engineering Thermodynamics Part 1
Science of Engineering Thermodynamics Part 2
Basic Law of Conservation and First Law of Thermodynamics
Carnot Cycle and Reversed Carnot Cycle
Enthalpy Entropy and Second Law of Thermodynamics
Rankine Cycle and Regenerative Feed Heating
Rankine Cycle for Closed Feed Water Heaters and Rankine Cycle Cogeneration
Ideal Verses Actual Rankine Cycle
Rankine Cycle Efficiency Improvement Techniques
Basic Wind Energy
Wind Turbine | Working Types and History of Wind Turbine
Theory of Wind Turbine
Fire Tube Boiler | Operation and Types of Fire Tube Boiler
Operation of Fire Tube BoilerOperation of fire tube boiler is as simple as its construction. In fire tube boiler, the fuel is burnt inside a furnace. The hot gases produced in the furnace then passes through the fire tubes. The fire tubes are immersed in water inside the main vessel of the boiler. As the hot gases are passed through these tubes, the heat energy of the gasses is transferred to the water surrounds them. As a result steam is generated in the water and naturally comes up and is stored upon the water in the same vessel of fire tube boiler. This steam is then taken out from the steam outlet for utilizing for required purpose. The water is fed into the boiler through the feed water inlet.
As the steam and water is stored is the same vessel, it is quite difficult to produce very high pressure steam from. General maximum capacity of this type of boiler is 17.5 kg/cm2 and with a capacity of 9 Metric Ton of steam per hour. In a fire tube boiler, the main boiler vessel is under pressure, so if this vessel is burst there will be a possibility of major accident due to this explosion.
Types of Fire Tube BoilerAccording to the location of furnace there are two types of fire tube boiler and these are external furnace and internal furnace type. There are mainly three types of external furnace fire tube boiler.
- Horizontal return tubular fire tube boiler.
- Short fire box fire tube boiler.
- Compact fire tube boiler.
- Horizontal tubular.
- Vertical tubular fire tube boiler.
Working Principle of Horizontal Return Fire Tube BoilerHorizontal return fire tube boiler is most suitable for low capacity thermal power plant. The main constructional features of this boiler are one big size steam drum which lies horizontally upon supporting structures. There are numbers of fire tubes come from furnace and also aligned horizontally inside the drum. When the drum is filled with water these tubes are submerged in water. The fuels (normally coal) burnt in the furnace and combustible gasses move into the fire tubes, travel through these tubes from rear to front of the boiler drum and finally the gases come into the smoke box. The hot gasses in the tubes under water transfer heat to the water via the tube walls. Due to this heat energy steam bubbles are created and come upon the water surface. As the amount of steam is increased in that closed drum, steam pressure inside the drum increases which increase significantly the boiling temperature of the water and hence rate of production of steam is reduced. In this way a fire tube boiler controls its own pressure. In other words this is a self pressure controlled boiler.
Advantages of Fire Tube Boiler
- Compact in construction.
- Fluctuation of steam demand can be met easily.
- Cheaper than water tube boiler.
Disadvantages of Fire Tube Boiler
- Due to large water the required steam pressure rising time quite high.
- Output steam pressure cannot be very high since the water and steam are kept in same vessel.
- The steam received from fire tube boiler is not very dry.
- In a fire tube boiler, the steam drum is always under pressure, so there may be a chance of huge explosion which resulting to severe accident.