Electrical Circuit Breaker
Arc in Circuit Breaker
Arc Interruption Theory
Oil Circuit Breaker
Air Circuit Breaker
Sulphur Hexafluoride Gas Properties
SF6 Circuit Breaker
Vacuum Circuit Breaker
Earth Leakage Circuit Breaker
Circuit Breaker Operation
Short Circuit Current of Circuit Breaker
GIS or Gas Insulated Switchgear
Metal Enclosed Switchgear
Miniature Circuit Breaker
Low Voltage Switchgear
Medium Voltage Switchgear
High Voltage Switchgear
Trip Circuit Supervision
Circuit Breaker Maintenance
Rating of Circuit Breaker
High Voltage Testing
• IR and PI Test
What is Circuit Breaker?
Definition of circuit breaker : - Electrical circuit breaker is a switching device which can be operated manually as well as automatically for controlling and protection of electrical power system respectively. As the modern power system deals with huge currents, the spacial attention should be given during designing of circuit breaker to safe interruption of arc produced during the operation of circuit breaker. This was the basic definition of circuit breaker.
Introduction to Circuit Breaker
The modern power system deals with huge power network and huge numbers of associated electrical equipment. During short circuit fault or any other types of electrical fault these equipment as well as the power network suffer a high stress of fault electric current in them which may damage the equipment and networks permanently. For saving these equipment and the power networks the fault electric current should be cleared from the system as quickly as possible. Again after the fault is cleared, the system must come to its normal working condition as soon as possible for supplying reliable quality power to the receiving ends. In addition to that for proper controlling of power system, different switching operations are required to be performed. So for timely disconnecting and reconnecting different parts of power system network for protection and control, there must be some special type of switching devices which can be operated safely under huge electric current carrying condition. During interruption of huge current, there would be large arcing in between switching contacts, so care should be taken to quench these arcs in circuit breaker in safe manner. The circuit breaker is the special device which does all the required switching operations during electric current carrying condition. This was the basic introduction to circuit breaker.
Working Principle of Circuit Breaker
The circuit breaker mainly consists of fixed contacts and moving contacts. In normal "on" condition of circuit breaker, these two contacts are physically connected to each other due to applied mechanical pressure on the moving contacts. There is an arrangement stored potential energy in the operating mechanism of circuit breaker which is realized if switching signal given to the breaker. The potential energy can be stored in the circuit breaker by different ways like by deforming metal spring, by compressed air, or by hydrolic pressure. But whatever the source of potential energy, it must be released during operation. Release of potential energy makes sliding of the moving contact at extremely fast manner. All circuit breaker have operating coils (tripping coils and close coil), whenever these coils are energized by switching pulse, the plunger inside them displaced. This operating coil plunger is typically attached to the operating mechanism of circuit breaker, as a result the mechanically stored potential energy in the breaker mechanism is released in forms of kinetic energy, which makes the moving contact to move as these moving contacts mechanically attached through a gear lever arrangement with the operating mechanism. After a cycle of operation of circuit breaker the total stored energy is released and hence the potential energy again stored in the operating mechanism of circuit breaker by means of spring charging motor or air compressor or by any other means. Till now we have discussed about mechanical working principle of circuit breaker. But there are electrical characteristics of a circuit breaker which also should be consider in this discussion of operation of circuit breaker.
Let's have a discussion on electrical principle of circuit breaker.
The circuit breaker has to carry large rated or fault power. Due to this large power there is always dangerously high arcing between moving contacts and fixed contact during operation of circuit breaker. Again as we discussed earlier the arc in circuit breaker can be quenching safely if the dielectric strength between the electric current carrying contacts of circuit breaker increases rapidly during every electric current zero crossing of the alternating current. The dielectric strength of the media in between contacts can be increased in numbers of ways, like by compressing the ionized arcing media since compressing accelerates the deionization process of the media, by cooling the arcing media since cooling increase the resistance of arcing path or by replacing the ionized arcing media by fresh gasses. Hence a numbers of arc quenching processes should be involved in operation of circuit breaker.
Types of Circuit Breaker
According different criteria there are different types of circuit breaker.
According to their arc quenching media the circuit breaker can be divided as-
According to their services the circuit breaker can be divided as-
- Outdoor circuit breaker
- Indoor breaker.
According to the operating mechanism of circuit breaker they can be divided as-
- Spring operated circuit breaker.
- Pneumatic circuit breaker.
- Hydrolic circuit breaker.
According to the voltage level of installation types of circuit breaker are referred as-