Uninterruptible Power Supply | UPS
Fermi Dirac Distribution Function
Fault of Electric Cable
Energy Bands in Crystals
Gallium Arsenide Semiconductor
Atomic Energy Levels
Steam Boiler | Working principle and Types of Boiler
Methods of Firing Steam Boiler
Fire Tube Boiler | Operation and Types of Fire Tube Boiler
Water Tube Boiler | Operation and Types of Water Tube Boiler
Steam Boiler Furnace Grate Firebox Combustion Chamber of Furnace
Feed Water and Steam Circuit of Boiler
Boiler Feed Water Treatment Demineralization Reverse Osmosis Plant Deaerator
Coal Combustion Theory
Fluidized Bed Combustion | Types and Advantages of Fluidized Bed Combustion
Steam Condenser of Turbine
Jet Condenser | Low Level High Level Ejector Jet Condenser
Surface Steam Condenser
Economics of Power Generation
Cooling Tower Useful Terms and Cooling Tower Performance
Cooling Tower Material and Main Components
Power Plant Fire Protection System
Hydrant System for Power Plant Fire Protection
Medium Velocity Water Spray or MVWS System for Fire Protection
Foam Fire Protection System
Fire Detection and Alarm System
Gas Extinguishing System
Electric Power Generation
Power Plants and Types of Power Plant
Thermal Power Generation Plant or Thermal Power Station
Hydro Power Plant | Construction Working and History of Hydro power plant
Nuclear Power Station or Nuclear Power Plant
Diesel Power Station
Why Supply Frequency is 50 Hz or 60 Hz?
Economiser in Thermal Power Plant | Economiser
MHD Generation or Magneto Hydro Dynamic Power Generation
Cogeneration | Combined Heat and Power
Thermoelectric Power Generators or Seebeck Power Generation
Cost of Electrical Energy
Gas Turbine Power Plant
Solar Energy Solar Electricity
Solar Energy System | History of Solar Energy
Types of Solar Power Station
Components of a Solar Electric Generating System
What is photovoltaic effect?
Staebler Wronski Effect
Working Principle of Photovoltaic Cell or Solar Cell
Characteristics of a Solar Cell and Parameters of a Solar Cell
Solar Cell Manufacturing Technology
What is a Solar PV Module?
What is Standalone Solar Electric System?
Steam Dryness Fraction
Superheated Steam and Steam Phase Diagram
Vapour Properties Mollier Chart Heat Capacities
What is Steam Flashing?
How to Calculate Steam Consumption During Plant Start Up
Effective Steam Distribution System
What is Water Hammer?
Engineering Thermodynamics Part 1
Science of Engineering Thermodynamics Part 2
Basic Law of Conservation and First Law of Thermodynamics
Carnot Cycle and Reversed Carnot Cycle
Enthalpy Entropy and Second Law of Thermodynamics
Rankine Cycle and Regenerative Feed Heating
Rankine Cycle for Closed Feed Water Heaters and Rankine Cycle Cogeneration
Ideal Verses Actual Rankine Cycle
Rankine Cycle Efficiency Improvement Techniques
Basic Wind Energy
Wind Turbine | Working Types and History of Wind Turbine
Theory of Wind Turbine
Boiler Feed Water Treatment Demineralization Reverse Osmosis Plant Deaerator
- The deposition of dissolved salts and suspended impurities will form a scale on the inside wall of different heat-exchangers and thus there will create excessive pressure and thermal stress (due to uneven heat exchange across the wall of heat-exchanger) inside the heat-exchangers, which may lead to the explosion and serious hazards for boilers.
- The harmful dissolved salts may react with various parts of boiler through which it flows, thereby corrode the surfaces.
- Corrosion damage may occur to turbine blades.
Arrangements for Boiler Feed Water TreatmentFor continuous supply of feed water to boiler, after removing impurities, there are two types of plant generally incorporated. These are:
- Demineralization plant (D M plant)
- Reverse Osmosis plant (R O plant)
Complete arrangements and inside equipment of these plants are described below.
Demineralization PlantThe function of demineralization plant is to remove dissolved salt by ion exchange method (chemical method) and there by producing pure feed water for boiler. The salts which make the water hard are generally-chloride, carbonates, bi-carbonates, silicates & phosphates of sodium, potassium, iron, calcium and magnesium. In D M plant there are three types of resin used for boiler feed water treatment process -
- Cation exchange resin
- Anion exchange resin
- Mixed Bed resin
- Resins are chemical substances (usually polymers of high molecular weight) used to react with salts & eliminates them by chemical process.
- As the name suggests, the cation exchange resin, exchanges the cation & anion exchange resin, exchanges anions with the salts dissolved in hard-water.
Cation Exchange ResinNaCl + RSO3H = RSO3 - Na + + HCl Thus H2SO4, H2CO3 are also produced. We have removed Na + but the water has become acidic.
Anion Exchange ResinHCl + R4NOH = R4NCl + H2O This way we have eliminated Cl - and thus acidity of the water. Similar reaction for H2SO4 also.
Mixed Bed ResinsThese mixed bed resins are used in Demineralization plant of boiler feed water treatment, to remove the ions (especially Na + and SO3 2- ) which may further present in the water after foregoing process of purification.
DegasserThe function of degasser tower is to remove carbonate ions by forming carbon-di-oxide. In degasser tower stream of water is poured from top & air is blown from bottom to top. In the pressure of air the carbonic acid (H2CO3) present in the water dissociates into H2O and CO2. H2CO3 = H2O + CO2 This CO2 is free to mix with air. Benefits of using degasser are:
- It removes the carbonic acid and other gases mixed with water by simple physical method & thereby reduce the chances of corrosion.
- It saves the resins which are very costly chemicals and thereby improves the economy of boiler feed water treatment process.
Reverse Osmosis Plant (RO Plant)Like demineralization plant there is another stage of water treatment which is known as reverse osmosis plant. RO plant uses the process known as reverse osmosis to produce salt-free water. The theoretical aspect is described below:-
Reverse OsmosisOn the higher density solution (lower density solvent) if a pressure (P), greater than osmotic pressure (π) is applied then the solvent molecules pass through the semi-permeable membrane from higher density solution to lower density solution. This phenomenon is called reverse osmosis. This one important stage for boiler feed water treatment process.
Reverse Osmosis PlantIn RO plant using reverse osmosis phenomenon salt-free water is taken out from raw water after the sand filtration. Purity of the salt-free water depends on effectiveness of the permeable membrane.
- Sodium hypochlorite (NaOCl) is injected to raw water to kill the algae or bacteria present in the raw water. Otherwise they may cause harm to the multi grade-filter (MGF).
- The multi-grade filter is the primitive type of filter where sand, stone-chips, stones are used in stacks to remove the large size suspended particles from the raw water.
- The net filter again removes medium-size suspended particles, where the raw water passes through the net minute vents.
- Then by ultra-filtration very small suspended particles are removed. After long usage of ultra-filtration unit, it requires back-wash, and then it is back-washed with water & three chemicals, viz. HCL, NaOH and NaOCl (Sodium Hypochlorite). HCl Removes iron by dissolving it. It also removes the basic salts those are rejected on UFU. NaOH ← It helps to remove acidic salt. NaOCl ← To kill algae and bacteria inside the UFU.
- After ultra-filtration the water is stored into RO feed tank & then pumped with RO feed pump of Reverse Osmosis Plant. In the channel the water is mixed with HCL (for pH controlling, as the water coming from RO plant or RO permeate water should have pH around 6.0) and SMBS (sodium meta bi-sulphate) [Na2S2O5]. Due to the presence of sodium hypochlorite the water is chlorinated. To remove excess chlorine SMBS is used. If excess chlorine is not removed then the semi-permeable membrane may get damaged. It is also mixed with anti-scaling reagent (AS), which reacts with those chemicals which form scale inside the channel.
- Then the water is passed through micro-cartridge filter (MCF) which removes the other suspended particles & the precipitate formed by the reaction of anti-scaling reagent with the scaling chemicals.
- In the this stage of boiler feed water treatment the water is fed to RO unit by H/P pump, where after successive filtration by 1st and 2nd stage RO it is fed to degasser unit.
- After degasification the water is passed through D/M plant MB (mixed bed) resin & stored into D/M water storage tank.
DeaeratorDeaerator is a contact type open heater in which dissolved oxygen in the feed water is removed as much as possible by mechanical means. Gases move from higher partial pressure to lower partial pressure. Partial pressure of oxygen in air is high (as air contains almost 21% oxygen by volume) than the partial pressure of dissolved oxygen in feed water. Hence, by simple mechanical means it is not possible to eliminate the dissolved oxygen from water.
Hence, in deaerator the feed water is heated by LP or VB steam (pressure: 2.5 – 3.5kg/cm2, temperature: 1400oC). Due to heating the partial pressure of dissolved oxygen in feed water increases and solubility decreases to considerable amount. Then by mechanical means dissolved oxygen is released in air. Hence Deaerator is another very important part of boiler feed water treatment plant. The mechanical means is same as that of in degasser. But instead of air, LP steam is blown from bottom to top and feed water is poured from top to bottom. Deaerator also serves as header, to provide a net positive suction head (NPSH) to the boiler feed pumps (BFP) and here by protects the BFPs from any damage due to vapor lock and cavitations.